1 4mw 2t h gas fired steam boiler for soap factory
10 tph WNS series gas-fired 1 4mw 2t h fired steam boiler for soap factory renovation project for Urumqi Railway
ZOZEN has played an active role in promoting the process of "coal to gas". In particular, the WNS series of gas-fired steam boilers have gained a good reputation in the industry due to their safe and efficient performance. This gas-fired boiler features compact design and is equipped with boiler control, alarm and interlocking devices of water level and steam pressure to ensure safe and reliable boiler operation. And the large-diameter corrugated furnace and high-efficiency heat-conducting threaded tubes increase the heating surface. With the energy-saving device at the tail of the flue, the exhaust gas temperature is reduced below 60℃, and the thermal efficiency is as high as 98%, helping clients achieve their goal of energy saving and emission reduction.
The reason you need to know the boiler energy consumption (reheat steam temperature) reheat steam temperature problems 1. Circumstances reheat temperature rises 1.1 Move boiler furnace flame center, furnace outlet temperature increases (see main economic indicators No. 5 boiler exhaust gas temperature). 1.2 coal increased too fast. 1.3 Excess air amount is increased. 1.4 pulverizing system start-stop. 1.5 Automatic control of the reheater desuperheating water improper adjustment. 1.6 reheater sootblowing time poor choice. 1.7 feed water temperature is low. 1.8 the high pressure turbine exhaust temperature is high. Next to the 1.9 high leakage, high reheater inlet temperature. Hot and cold extraction section greater then 1.10. 1.11 boiler heating surface design is unreasonable, over-temperature reheater tube wall, forced cooling operation. 2. Reheat the following partial flame temperature is lowered center 2.1: burner tilt deviation, hem; burner is switched from the upper to the lower layer, the lower layer or to an excessive amount of the powder; volatile coal fraction is increased, the pulverized coal thinning, water reduction. 2.2 reheater heating surface fouling, slagging, fouling the interior. 2.3 Save reheat the heated drain valve. 2.4 automatic adjustment inappropriate, excessive reheater desuperheating water. 2.5 feedwater temperature. 2.6 economizer and water wall sootblowing time poor choice. 2.7 reduce the amount of coal too fast. 2.8 # 1, # 2 high pressure heater is disabled, increasing the reheated steam flow.
Zhengzhou Fangkuai Boiler Sales Co., Ltd. is a subsidiary of Fangkuai Boiler Company and is mainly responsible for the domestic and foreign trade of Fangkuai Boiler. The Fangkuai headquarters base has a single R & D center, a full-service laboratory and two manufacturing plants, with a production area of 120,000 square meters. It is the leading domestic enterprise with automatic boiler processing capabilities, and its products are exported to many countries and regions. At present, Fangkuai Boiler has established industry-university-research cooperation bases with Tsinghua University, Xi'an Jiaotong University and Zhengzhou University, and has established the only academician cooperation station in the boiler industry. It has more than 100 patented technologies and masters the core technology of advanced clean fuel boilers. , R & D, production capacity are at the forefront of the industry. Relying on its own technical advantages in industrial boilers and digital control, the Fangkuai Boiler Remote Monitoring Cloud Service Platform has been organized to truly realize the intelligent operating system of industrial boilers, making it easier and faster to operate boilers.
Steam boiler automatically displays the instrument will encounter in the use of water which asked 1 4mw 2t h fired steam boiler for soap factorys by fuel can be divided into electric steam boiler, steam boiler fuel, gas steam boilers. According to the structure can be divided into vertical steam boilers, horizontal steam boiler, steam boiler small single, double back to the vertical structure, large steam boiler mostly as three-pass horizontal structure. When the water level is low or groundwater automatically display meter, installed in the steam boiler only a low level means, even water too thin; when the groundwater level automatic means or instruments show lower, the steam boiler is mounted in a water only means; e no other ground water drainage means drainage cock; drum means on a level effective means further water damage; plug door apparatus can not twist the water level; a level plug door apparatus leakage leakage; means water false water level display; water level on the two drum devices are inconsistent; water glass breakage frequently means; glass protection device is not level; water means water level glass plate red indicator is not displayed; glass plate It does not show red; red glass panel is not displayed. If the apparatus dirty water, the water level can not be clearly observed. Steam boiler water level gauge inconsistencies mainly glass and clear observation of steam boiler water level gauge is not cleaned for a long time during operation, routine maintenance is not performed, resulting in water means cocks rust, soda connecting tube blockage. Or filler inadequate or aging. In addition to steam, water or tap is blocked, the phenomenon of false water level may also be due to misalignment between the steam pipes and caused the water level instrument; steam, dislocation faucet handle position will result cocks closed, but may also be due to boiler poor water quality, and water vapor and water and the water level caused by false. Broken glass is mainly water vapor, the centerline of the tap out of alignment, the bending stress in the glass tube memory, no glass expansion gap length is too large, the water level window directly blown cold, poor quality glass. During the boiler operation, we found that the water level is unclear, when the ultra-high water level should be stopped immediately, should discover the problem.