101 liter gas boiler for hot water
Small steam 101 liter boiler for hot water Description: Small steam boiler refers to the amount of evaporation per unit time is small and low steam pressure steam boiler, steam boilers generally small volume refers to less than 30 micro-liters exemption steam boiler, the mechatronic device, host auxiliary integrated, easy to use, simple to install, simply connect the power, water and heat can, installation, use and technology supervision department supervision is not. Working principle: Its basic principle is: by an automatic control device, to ensure control liquid during operation or high, medium and low probe feedback control electrode opening of the pump, is closed, the amount of water the length of time the heating furnace; it is set by the pressure switch with the constant maximum output vapor pressure steam, the water level falling furnace, when in the low water level (mechanical), water level (electronic), automatic water pump, to the high level, the pump is stopped replenishment; At the same time, the electric tube furnace heating was continued, a steady stream to produce steam, the upper portion of the top panel or instantly display the steam pressure gauge pointer value, the whole process can be automatically displayed by the indicator. Product: Small steam boiler in accordance with the fuel can be divided into small electric steam boilers, small fuel steam boilers, steam boilers and other small gas; in accordance with the vertical structure can be divided into small steam boilers, horizontal steam boiler small, mostly single small steam boiler , double the return of the vertical structure, large steam boiler three-pass mostly horizontal structure
The impact of fuel hot water 101 liter boiler for hot water energy consumption indicators of the country has been engaged in a pile of incentives impressive work of coal to natural gas, fuel oil boiler with hot water, greatly minus the dust pollution, while discharging harmful gases such as nitric oxide has also been inhibition. Energy consumption indicators is a key measure of marked oil hot water boilers, to discuss incentives under the influence of a pile of hot water boiler fuel consumption indicator of subsequent. Through research departments, oil hot water boiler heat losses arising primarily from the comparison of two parts: non-standard air-fuel ratio combustion with smoke exhaust heat waste. Reduce smoke emissions from waste heat can be converted in hot water boiler fuel waste heat recycling install smoke trailing, or leading with more types of condensate recovery boiler. Combustion air-fuel ratio is inappropriate Standard Decomposition: Usually based fuel ejector type hot water boiler burner, air-fuel ratio can be formed mobilization maneuver. Many hot water boiler fuel based on a mechanical blower burner, resulting in a standard air-fuel ratio causes are several later: air-fuel ratio is mainly divided into different from standard probability comparison: when the airflow in excess, there will not be excess cold air It is heated, causing the oil hot water boiler energy consumption rise, low energy consumption indicators of fuel hot water boiler; when there is insufficient air flow, insufficient to ignite the situation will occur, causing low energy consumption hot water boiler fuel indicators.
In recent years, the increasing popularity of Yichun City, Jiangxi Province comprehensive energy saving coal-fired 101 liter boiler for hot water upgrade project, plans to eliminate 75% of the downtown 10 steam tons / hour and below the coal-fired boilers, a ban on new 20 tons of steam / hour and less fuel coal boilers; the rest of principle, then the new 10 steam tons / hour of coal-fired boilers.
Following this, Jiangxi Province Department of Finance issued a special subsidy fund boilers, Yichun downtown 2015--2016 phase-out 10 steam tons / hour coal-fired boilers companies grant. The subsidy standard is: 2 out of steam tons / hour and coal-fired boilers, subsidies to 10,000 yuan / Taiwan; out of steam 2-10 t / h coal-fired boiler, subsidies for 20,000 yuan / Taiwan.
Commissioning of Boiler gas 101 liter boiler for hot water commissioning must be carried out after the hydrostatic test. Before commissioning, should be a comprehensive inspection of each furnace parts, electronic control devices, wiring, etc. are normal, water supply, oil furnace if opened, electrical contacts are in the set position. 1, depending on the size of the fuel consumption, the initial damper, the hydraulic pressure. 2, the power is turned on, the power switch to open the cabinet, the water pump starts furnace, (if the pump is rotated into the anhydrous, pump purge valve is opened, the air exhaust pump). 3, control checks whether the normal water level electrode. 4, check the burner operation is normal. Starter burner starts combustion when the water level rose to a predetermined level, the start of combustion is normal to observe: Start no vibration noise, stable combustion, no smoke, orange yellow flame, burning bright clear. Otherwise, to make the appropriate adjustment (refer to burner instructions). Note: The oil pressure between 0.8 ~ 1.0Mpa, after a good tune, do not easily change, oil pressure is too high or too low have an effect on burner performance life. 5, check the pressure gauge pointer swing is smooth, with or without loosening stuck. 6, whether the discharge check valve is set at the set pressure steam: Pressure controller first maximum working pressure, a safety valve is adjusted to the set pressure higher than 0.05MPa, when the furnace pressure was raised to whether the exhaust pressure setting, if exhaust , pulling the safety valve a few times, and try again, if not enough to deal with safety valve to adjust. Pressure relief valve setting: boiler rated pressure + 0.03MPa. 7, check the electrical contacts of the operation: When the pressure is raised to the maximum working pressure (not exceed the rated working pressure), should stop burning, open the safety valve blowing off steam, the pressure to a minimum operating pressure (maximum operating pressure is generally lowest set to 0.10MPa), combustion burner should be restarted. Note: When the adjustment screw should slow, especially when the pointer approaches the end, otherwise, damage the screw off the wire.