11 mw oil fired hot water boiler in pakistan
The 1 ton wns series oil and gas boiler adopts a horizontal three-return structure, and the boiler produces fast steam and high thermal efficiency. The boiler adopts a large-area combustion chamber. The combustion chamber is surrounded by a jacketed water jacket. A dense fire tube is arranged on the upper part of the combustion chamber, and an advanced combustion device is arranged. The fuel is fully burned in the combustion chamber, and the high-temperature flue gas enters the dense fire tube to continue to radiate heat. Then gathered in the smoke chamber for further heat release.
Our preliminary investigation when the other side is very interested in fast boiler, a number of fast-party research and development as well as outstanding patent cases in all industry sectors, we have confidence in each other quickly this brand. After the cooperation, but also the strength and each staff fully aware of the fast boiler of a good attitude, and cooperation in the box, very at ease. --customer feedback
Pressure fire operations and precautions Henan fast boiler's steam boiler Xiao Bian told you about the operation of steam boilers and pressure fire precautions and stainless steel high temperature magnetic pump structural characteristics 1. pressure steam boiler fire steps of (1) to reduce boiler load, according to the length of time of shutdown, the seam thicker, the thickness is generally not more than 200 mm, suitable to accelerate the speed of the grate. (2) to the slag is thickened seam about 1 mm from the stop grate rotation, the drum is stopped, the operation of the induced draft fan, blowing off a small segment of the regulating plate stopper and dampers qs, relying on natural ventilation to maintain coal the lean-burn, the sewage, boiler water level will rise to the maximum allowable level. If the fire burn coal gate, grate can be switched on again, the coal-fired back, a distance. (3) the recovery boiler needs to run, as long as the opening lead, a blower, to adjust the smoke, and the wind baffle plenum segment adjusting the opening degree of the shutter, the adjustment of combustion steam boiler seam thickness to be normal, start grate, can be restored run. 2. Note the use of a steam boiler (1) before starting Check power supply voltage, there are unusual circumstances water, close the drain valve opens the water supply valve, check whether the pump stuck, stuck if the pump, remove the fan cover, rotation of the motor shaft to the flexible state to boot. (2) When the steam boiler maintenance or replacement of parts, turn off the power to avoid live work dangerous. (3) electronic control box, pump motors and other parts should avoid damp water to prevent burning boiler should pay attention to keep clean. (4) steam boilers in accordance with quality requirements, when using the apparatus sure to install a water softener, the water softener is not used because the boiler may cause fouling, may cause serious squib, shortening the life of the boiler. (5) Please note that when using sewage. And at least once a day with a discharge pressure of between 0.1MPa to 0.15MPa discharge may be prevented clogging of pipes, sewage should be properly connected, to guard against burns. Stainless steel high temperature magnetic pump structural features: a sliding bearing magnetic pump sliding bearing materials impregnated graphite, PTFE and engineering ceramics. Because of engineering ceramics has good heat resistance, corrosion resistance, abrasion performance, so the sliding bearing magnetic pump more use of engineering ceramics production. Because of engineering ceramics are brittle and expansion coefficient, so the bearing clearance is not too small, so as not to hold the shaft accident. Since the magnetic pump in order to lubricate sliding bearing medium conveyed, it should be used depending on the medium and conditions, making use of different materials bearing. 2. Cooling lubricating fluid flow control pump operation must be flush cooling internal friction annulus region between the sliding bearing and the magnetic rotor and the containment shell with a small amount of liquid. Coolant flow rate is typically 2-3% of the design flow of the pump, the annulus area between the inner magnetic rotor of the eddy current generated spacer bush high heat. When enough cooling lubricant or flushing holes poor, clogging, the medium will result in a temperature above the operating temperature of the permanent magnet, the inner magnetic rotor gradually loses its magnetism, the magnetic force actuator failure. When the medium is water or water-based liquid, the temperature rise can be maintained in the annulus region of 3-5 deg.] C; or when the medium is a hydrocarbon oil, allows the annulus region of the temperature was maintained at 5-8 ℃. Henan is committed to fast boiler steam boiler manufacturing, product quality, reasonable prices and widespread industry praise, if you have any needs, please contact us!
Boiler and burner What is the difference? Simply put by the boiler and boiler furnace consisting Pot is the place to absorb heat, increasing the temperature is generally endothermic water, or water absorbs heat of vaporization of components, mainly heating water wall, etc. surface composition, and the fuel is coal furnace, where the heat released by burning oil, material, and other components mainly furnace while the burner is to provide a combustion apparatus of the release of energy, the material is spray combustion, combustion air.