16 tons oil steam boiler in plastic factory
The capacity of the boiler is also called the output of the boiler. It is the basic characteristic parameter of the boiler. The 16 tons steam boiler in plastic factory is expressed by the evaporation amount, and the common unit is ton/hour (t/h). Hot water boilers are expressed in terms of heat, in megawatts (MW). The hot water boiler produces 0.7 MW of heat, which is roughly equivalent to that of a steam boiler producing 1 t/h of steam. ZG boiler produces oil and gas boilers with different capacities, which indicate the rated output of the boiler, that is, the evaporation or heat supply under normal working conditions when the boiler is in continuous operation for a long time.
Anyang City Minshan Nonferrous Metal Co., Ltd. is a collection of urban mining, renewable resources, energy as one of the economic wisdom of cleaning companies, mainly non-ferrous metal extraction and processing work. Company to conserve energy, cleaner production for the purpose of this concept coincides with the fast boiler. Thus, when the company in the purchase of the product boiler, and fast boiler almost hit it off, by the party to provide a fast 6 tons of steam integrally condensing gas 16 tons steam boiler in plastic factory (WNS6-1.25.Y.Q).
The heating oil and gas boilers produced by ZG boiler range in the range of 0.7-58 MW and can be used for heating in different fields. The heating boiler generally uses a hot water boiler, and the hot water generated by the boiler releases heat through the pipeline to warm the environment and achieve heating purposes. Some companies also choose 16 tons steam boiler in plastic factorys for heating. But at the same time steam boilers are also used for other purposes, not just for heating.
Henan gas treatment condensing boiler operation in the secondary combustion Accident Henan condensing gas boiler, deposited in the rear of the boiler flue gas condensing Henan combustibles (soot, carbon black) re-ignition combustion phenomenon called secondary combustion, also known as Henan condensing gas boiler flue tail and then burned. It will backpass severe, air preheater, induced draft fan and other equipment economizer even destroyed. 1. Henan condensing gas boiler secondary combustion phenomenon (1) a sharp rise in exhaust gas temperature, chimney to take smoke, fire or even smoke. (2) changes drastically furnace pressure, positive pressure occurs. (3) severe flue enclosure dark red. (4) when there is an air preheater, a sharp rise in the temperature of the hot air, pressure instability. (5) blast doors sometimes the tail action. Cause 2.Henan condensing gas boiler secondary combustion (1) poor atomization burner, oil, gas and incomplete combustion into the rear of the boiler. (2) combustion improperly adjusted, with insufficient wind or with the wind unreasonable. (3) Henan condensing gas boiler startup, shutdown during low furnace temperature, the unburned fuel in the furnace. (4) When shutdown or boiler fire, air gun valve is not closed. (5) the combustion chamber negative pressure is too large, too late to make the gas burn it into the rear of the boiler. (6) Long-term non-stop cleaning backpass furnace, accumulating a certain amount of soot or carbon black. (7) through the air preheater flue or leakage. 3. The gas processing condensed Henan secondary combustion boiler (1) should immediately stop the gas, stop the wind, shutdown. (2) closing the flue, and a baffle duct around the door opening, is prohibited to start sending, induced draft fan. (3) immediately extinguishing device into steam, carbon dioxide or other fire extinguishing means, (4) Strengthening Henan condensing gas boiler feed water and turn on the water, open the valve or economizer recirculation tube to protect the economizer is not burning. (5) When the exhaust gas temperature close to the temperature of the injected steam, or less than 150 deg.] C over 1h and stable openable inspection hole inspection, after checking element determines an ignition source, before the fan starts ventilation and cooling. (6) when the temperature drops below the flue 50 ℃, check before entering the flue tail heating surface, and should completely remove the flue soot. If not burning, can be re-started ignition; if burning, should be replaced, repaired burning member.