17000kg h thompson cochran fire tube boiler
Burns Hospital Affiliated Hospital of Shanxi Linfen Linfen Steel is attending a hospital burns burns and other diseases. Hot water 17000kg h thompson cochran fire tube boiler is essential hospital equipment heat, hot water output can provide disinfection of medical instruments and ward heating demand. With constantly improving our environmental policy, boiler correspondingly introduced more sophisticated Use. Linfen hospital burns to respond positively to the national environmental policy, decided to introduce an environmentally friendly low nitrogen gas hot water boiler. Taking into account the special circumstances of the hospital, the boiler should also have the use of safe, clean overall characteristics. Based on the above considerations, finalize the Linfen hospital with burns boiler party cooperation fast, fast is provided by one side of a gas condensing pressure hot water boiler (CWNS2.1-95 / 70-Y.Q).
Why does not need cooling water and 17000kg h thompson cochran fire tube boiler ignition solve the problem after: boilers, which have some common problems, as well as some difficult problems, such as: why water boiler does not need to start from within the ignition period of time? The use of cast iron economizer, then how to solve the problem of cooling the ignition process? In addition, there are questions about what the boiler, and to promptly answer? Since these issues are brought up, and that below, you may wish to give the correct answer, so that we have a complete understanding and correct understanding. 1. Why do not need to water after the boiler ignition start a period of time? This, then, according to technical personnel, is the citation boiler ignition, since the boiler water temperature rises, its volume expands, and further, so that the water level increased. With further increase in the temperature of boiler water, so that the steam generated in the water wall, so that the boiler water level is further increased, so that this period of time from the start of ignition, the water is not required.
Clearly, high calorific value gas in a low calorific value greater than the value, the difference is part of latent heat of vaporization of water vapor. The actual industrial and civil engineering applications commonly used in gas low calorific value gas is calculated. If the calculated low calorific value, condensing gas 17000kg h thompson cochran fire tube boiler is capable of absorbing latent heat of vaporization, i.e., the thermal efficiency may reach a high of 108%.
Using electric 17000kg h thompson cochran fire tube boilers should be noted that the problem first, before operating an electric boiler be sure to carefully read the product manual, in strict accordance with the instructions, so as to correctly understand and use electric boilers, will not affect the use of operational errors. Second, the need to carefully check before starting electric boiler water source, and the power supply voltage, to ensure that there is no abnormality, and then the valve is opened, the water fills the conduit, the electric boiler into operation time. Third, when the electric boiler appears when failure requires maintenance, as far as possible off the power again after the inspection, but also for added security. Fourth, keep it clean and tidy electric boiler, to do the work waterproof moisture pump motor, electric control boxes and other parts. If conditions permit, can be prepared in a small boiler room. Also to be regularly fittings and spare pipeline pumps, pipe inspection, and take all security work.