180kg one hour electric steam boiler
Automatic water level control? Electric steam boiler can be set manually or pot Free subject: 108KW the water volume is less than 30.4, flexible and convenient: used in line JB / 2379-93 and "metal tubular electric heating element technical conditions" desired low heat load surface heating element; quality thick stainless steel tube outer heating wire, Ni-Ge alloy built expensive electric components, high thermal efficiency, and longer life. Garland using each heating element is connected to the control system employs multiple heating pipes packet control group can be set to manual or automatic mode; opening pressure can according to the flexible electrical power and steam consumption! 5, safety: in strict accordance with the whole "Steam Boiler Safety Technology Supervision" manufacture, possess a number of complete protection, leakage protection, water protection, ground fault protection, overpressure protection, steam, boiler automatic protection? 1, ease of operation: automatic intelligent control, without staff on duty. Can be set to manual or automatic mode; pressure, automatic level control, boiler fittings touch of a button, either into the automatic operation, the automatic control of the pressure controller, the control system can give food factory in three full pump load change two 10T gas boiler, electric heating automatic start-stop control! 2, clean environment: heating using electric energy, without any environmental pollution clean, easy to install small footprint! , Automatic level control? Electric steam boiler 6, the original electric stepper control, speed control can be divided according to the actual amount of steam, the boiler to reduce the impact on the power grid, so that the boiler operation is more stable.
About Code of Practice Code of Practice for the safe operation of the hot water boiler hot water boiler hot water boiler safe operation because of its specificity required safety practices. Understandable that the normal life and production are inseparable from the use of the hot water boiler. How hot water boiler safety issues need to be protected? 1, carefully check the work before the hot water boiler, drainage, gas pipe fittings, safety valve, pressure gauge, water level, is sensitive so that, after confirming it is safe to operate. 2, with both hands to manipulate when Sheung hand to open the door of water, whereupon the other hand the water injector and valve open, the water naturally into the furnace. When stopped, the steam valve should be closed first, then turn off the water door, switch and valve, the front face must escape to avoid soft drinks out of the accident. 3, hot water boiler in operation, inspection departments to pay attention to observe the pressure and water level. Fireman are not allowed to leave their posts without permission, when night work, avoid dozing off, more sleep deprivation, in order to avoid accidents. Hot water boiler blowdown, must be performed once per shift, adjust the water level in the sewage before, slightly higher 2/3, followed by sewage. 4, the water level table class must be flushed once. When flushing, according to established procedures, the first closure valve and open the drain valve, flush valve steam, steam at this time pay attention to the origin is blocked. Steam valve is then closed, when attention is blocked antecedents water. Flushing valve, until the water becomes steam, some a little longer, in order to guarantee no false water level. Hot water boiler coal must be checked, to prevent coal detonator explosives and other explosives thrown into the furnace, to prevent the risk of explosion. 5, to always check the temperature of the motor housing and the machinery, such as mechanical failure or an electric motor with a fever more than 60 degrees, stop testing immediately. Hot water boiler normal operation, the vapor pressure shall not exceed the operating pressure, the safety valve inspection once a week.
Battle to win the blue sky, is the major decisions and plans to make a big party in the nineteenth, and is for building a moderately prosperous society, to improve the quality of life of citizens and establish a beautiful China's development goals. To fully implement the nineteen spirit, promote the governance of air pollution intensity and improve the living quality of the environment, this year March 8, Zhengzhou Municipal Party Committee General Office, Zhengzhou Municipal People's Government Office issued the 2018 air pollution control program and the corresponding subsidy policy, the implementation of low-nitrogen gas boiler retrofit demonstration project, as follows:
Before the end of September 2018, the city's more than 20 tons of steam (with), and the urban areas more than 4 tons of steam (with) the completion of gas-fired low-nitrogen transformation project demonstration projects, nitrogen oxides emission concentration is not higher than 30 mg / cubic meter, City level financial awards complement carried out in accordance with the 40% investment in equipment;
Before the end of September 2018, the city's more than 4 tons of steam (with), and the urban areas more than 2 tons of steam (including) low nitrogen gas boiler reconstruction project completed demonstration projects, nitrogen oxides emission concentration is not higher than 30 mg / cubic meter, City level financial awards complement carried out according to 30% of equipment investment;
Before the end of April 2019, the city completed all gas-fired low-nitrogen transformation, nitrogen oxides emission concentration is not higher than 30 mg / cubic meter, the municipal finances awards complement of 15% investment in equipment.
What problems should be paid attention to in maintenance Electric normal pressure Boiler
Nowadays, advanced electric atmospheric pressure boilers need to be used in industrial production as well as in daily life. However, the electric atmospheric pressure boiler is a highly operational mechatronics equipment, such as customer inspection, maintenance is not timely will result in equipment line aging, equipment oil circuit and oil pump wear and so on. Therefore, users need to pay attention to the maintenance of equipment when running boilers, then, what problems should users pay attention to in the maintenance of electric pressure boilers with good performance?
1, pay attention to stop furnace detection electric atmospheric pressure boiler in the maintenance, users should let the equipment according to the normal shutdown procedure operation to achieve slow cooling, at the same time, Users should use pot water circulation and furnace ventilation to gradually reduce the temperature in the pot and furnace. It is worth noting that when opening the door hole of the equipment, users need to pay attention to preventing the burning of steam, hot water and flue gas in the boiler.
2, note that when users maintain the insulation, the combustor and flue of the detected atmospheric pressure boiler should be separated from the total flue or the other running boiler flue. The test results are as follows: (1) the combustor and flue of the tested atmospheric pressure boiler should be separated from the main flue or other running boiler. And the flue gate should be closed tightly, and in the partition after ventilation. In addition, the blind plate used in equipment partition should have sufficient strength and hardness to avoid being bulged by high pressure medium in the operation of electric normal pressure boiler, and the partition position should be clearly indicated to avoid confusion.
3, note that the user must completely cut off the connection pipe between the vessel and the gas equipment, especially to the combustible and toxic medium equipment before the inspection of the atmospheric pressure vessel is carried out by the user of the equipment container. In addition, the equipment container not only needs to close the equipment valve, but also needs to use the blind plate of the equipment to close the valve so as to prevent the gas leakage into the container and cause the fire explosion or poisoning accident of the valve so as to cause the combustible or toxic gas to leak into the container.