2 ton natural gas fired hot water boiler
Shunde main business of special sea oil production and processing, etc., in the course of special oil refining, a large amount of steam required for oil and gas extraction, distillation and extraction technology and other aspects, therefore, the boiler is supplied special sea oil processing technology company Shunde indispensable less equipment. As environmental policy progresses, the chemical industry as more polluting industries are highly valued the various departments of quality supervision, sea Shunde companies to follow the development of the State Environmental Protection pace, choose clean the boiler industry-leading fast Boiler cooperation with the parties by quickly assess the specific needs on-site estimates and sea Shunde, to provide a SZS series of 25 tons of steam water tube steam boiler (SZS25-2.0-YQ).
Why gas steam boiler energy saving may be why gas steam boiler energy saving gas steam boiler design pressure should be slightly higher than the high work pressure, and not less than safety valve opening pressure. Design pressure gas furnace using 1.2 to 1.5 times the working pressure; liquid pressure furnace design should take pressure of 1.05 to 1.2 times; Liquid furnace gas and steam outlet pressure differential should be greater than 0.15MPa (1.5kgf / cm2). Temperature gas steam boiler import and export, from the design of both economic and security point of view, to design gas-steam to run a suitable temperature difference in the system, this temperature difference should be less than 30 ℃. Gas steam boiler is a closed loop, the return oil temperature and oil temperature only a 20-30, 20-30 words, only heating the temperature difference can reach temperature gas steam boiler. The steam boiler is added to cold water, the cold water is heated into steam to heat heating device, steam becomes condensed water discharged 60-70 degrees. Therefore, the role of energy saving functions!
The main characteristics of the indicators boiler What? To demonstrate configuration, capacity, parameter and economical operation of the boiler, etc., generally represented by the following indicators to the basic characteristics of the boiler. A) evaporation industrial boilers evaporation is generally 0.1 ~ 65t / h. For the 2 ton fired hot water boiler with a nominal thermal power of its capacity to indicate the size, in units of MW. (Ii) pressure and temperature for saturated steam production boiler, just indicate steam pressure. For the production of superheated steam boiler, the steam temperature of the steam must be marked at the outlet of the superheater, i.e., superheated steam temperature, the unit is deg.] C. For hot water boiler, the hot water temperature has rated outlet and rated the import of sub backwater temperature. With rated thermal power, rated water temperature and the return temperature corresponding to the rated nominal referred circulating water flow of water through the hot water boiler, the unit is t / h. Heating boiler (iii) an evaporator heating surface and the heating surface of the heat generation rate surface evaporation rate or heating rate is an indicator of the intensity of the boiler work, the greater the numerical value, the better the heat transfer, the smaller the amount of metal consumed boiler. Heating surface evaporation rate general industrial boiler is less than 40kg / (m · h); heating surface of the heating rate of hot water boiler is less than 83700kJ / (m · h) iv) the thermal efficiency of the boiler which is an index indicating economical boiler heat, general industrial combustion thermal coal boiler efficiency of around 60% to 82%. Sometimes, in order to measure the heat economy schematically steam boiler, are also commonly used coal or coal water vapor than the ratio expressed as the ratio of the amount of coal in the boiler per unit time over the period of time and the amount of steam production. Coal-water ratio of about the size and type of boiler, coal quality and operation management quality and other factors. Industrial boilers coal-water ratio is generally l: 6 ~ 1: 7.5. Description (a) Evaporation: desired amount of steam produced per hour steam boiler called evaporation, the unit is t / h steam boiler showed that the size of the rated capacity of evaporation, i.e. in boiler design parameters and ensure a certain efficiency. maximum continuous evaporation, also known as the rated output of the boiler (ii) pressure and temperature: the rated pressure steam boiler of the steam at the outlet of the steam or the hot water boiler rated working pressure rated pressure at the outlet of the hot water boiler is called, and He said maximum working pressure, in units of MPa (iii) an evaporator heating surface and the heating surface of the heat generation rate: refers to the heating surface of the pot soft drinks and other heat transfer medium and the flue gas heat exchange area of the pressure receiving member, usually with smoke metal surface area of the gas-side heating area is calculated, in units of square meters. the amount of steam per hour per square meter of the resulting heating surface, called boiler heating surface evaporation rate, in units of kg / (m · h) per hour hot water boiler m² heating surface of heat generated by the heat generation rate is referred to as heating surface, the unit is kJ / (m · h). (Iv) thermal efficiency: thermal efficiency of the boiler is a boiler effective utilization percentage of the heat input and heat boiler per unit time, also called boiler efficiency, [eta] is represented by the symbol.
Steam boilers common faults and submersible pumps fast boiler's Henan Xiao Bian introduce a common steam boiler failure problems common faults and submersible pumps steam boiler water level is with you, the causes and solutions to a steam boiler water level is a common problem its reasons: 1, the water level is too low installation; 2, water, a water pipe connected too small; 3 have a water level or a low level display instrument automatically when the water level on only one boiler; 4, drainage water gauge no grounding drain cock; 5, the drum water level is an effective, other water damage; 6, the tap water is screw fixed; 7, the tap water gauge leak, leaking; 8, water gauge false water level on a display; 9, the drum water level in the two water gauge level of inconsistency; water glass is often broken; 11, water glass is no guard; 12, the water level is low level indicating no glass panel represents red; 13, level glass plate is dirty, the water level observation is unclear. The main reason is because of 1-4 above design, installation or alteration of dislocation caused. When the steam boiler with a low water level status is when the drum water level is only one case, because the internal balancer lowland water's leakage short circuit (can not be detected at that time), causing lowland water level is high water level appears ( the so-called full of water), while the water level on the drum have shown that low water levels (and may even see the water level), then the fireman because they can not determine the true level of the boiler will go immediately and check the water level on the drum, it will be very serious water shortage delays container boiler accident occurred. Some even show the water level too low trust level's status, and take a lot of sewage, mistakenly steam boiler water when filled with water incident handling, acceleration accidents, there is precedent for such incidents to be investigated. Then, the above-mentioned reasons for the failure of 5-9 main problem is the boiler running for long periods of time rinse water, a daily maintenance is not carried out, resulting in water cock rust, gas, water and even the block, or insufficient packing or aging deterioration . False water level phenomenon, in addition to gas, water or even the cock pipe is blocked, but also could be vapor, the water pipe connected to the water level due to misalignment connected; steam, water tap handle installed the wrong position resulting cock closed, since there poor water quality, the water level in the boiler and false priming. Water gauge glass is broken mainly steam, water faucet centerline not aligned, the presence of glass bending stress; long glass without expansion gap; water gauge is being cold draft at window glass, and glass pipe quality was poor. Submersible pump is a mechanical and electrical integration of high-tech products. In recent years, due to the submersible pump in a sealed, insulation, cooling and monitoring technologies have made great progress, but also successfully achieved the automatic coupling pumps and water pipes, so that the large diameter submersible pump application significantly faster. Since diving save electric pumping station project investment, quick installation and maintenance, operating conditions greatly improved equipment reliability and service life improved significantly. At present, China is not only the production and installation of large-diameter 900 mm below the axial and mixed-flow pump, can produce diameter 1.4 m and 1.6 m large submersible pumps, has laid a good foundation for the promotion of technical diving electric pump station. Gao dive afraid of flooding, but also has good maneuverability advantages of quick removal and installation, able to cope with the water level soared, chestnut room flooding and other emergencies pieces, large-scale changes asked of submersible pumps. Henan is committed to fast boiler steam boiler manufacturing, product quality, reasonable prices and widespread industry praise, if you have any needs, please contact us!