24mv high pressure boiler in hospital
But continuously compare them, we will find that no matter which brand, condensing 24mv high pressure boiler in hospitals are better than the price of ordinary boilers lot more expensive, which is what causes it? In the end what is the difference between the two? Today we have the following three aspects to compare the two and see what exactly the difference was, where condensing boiler is better? 1, energy (high furnace thermal efficiency condensing) water produced in the ordinary boiler fuel combustion state in the steam superheater in the flue gas, from the chimney with the flue gas loss, resulting in low thermal efficiency of the boiler. Condensing boiler fully recovered latent heat of condensation in flue gas sensible heat and water vapor, high thermal efficiency, can be described as very energy efficient. 2, the service life (life expectancy is substantially higher than ordinary boilers) ordinary boiler due to the design of key parts of the combustion chamber, heat exchangers, etc., combined with domestic water, gas quality and other factors, led to the ordinary life of the boiler can not meet the design requirements, parts of Europe net imports of boiler service life generally five years, the outstanding domestic brands can surpass imported brands. Condensing boiler service life is generally welcomed by customers about their 4-5 times, because of its revolutionary product works, leading an ordinary life will drastically boiler. 3, scale process (condensing furnace without any scale) the conventional type boiler: the piping system is heated thereby often very easy to form scale, relatively easy to damage the apparatus. In order to solve the scale problem, most customers had to monogamous water softeners. As a result of the new condensing boiler burning hot mix, using a large water pipe system, compared to ordinary boiler, condensing boiler is do not worry about the scale of the problem.
Residential area points run low nitrogen 24mv high pressure boiler in hospital What? For now use low nitrogen boiler is very wide, many industrial applications and even district people's lives is also used to this type of boiler, because it has been so special transformation is relatively energy-efficient and less likely to pollute the environment So widespread has been recognized and loved people. However, in order to further ensure safety, when the boiler is running low nitrogen residential area should be to comply with the following points. A, water temperature and to control the speed at the time of low nitrogen Sheung residential district boiler start of operation of the boiler and the temperature of each component is uniform and ambient temperature, as the temperature inside the combustion boiler starts rising, since the boiler relatively thick wall so that the outside temperature rises more slowly, resulting in a temperature difference generated inside and outside wall. Nitrogen and low boiler manufacturers find the temperature difference between the inside and outside will be greater as the thickness, so if the water temperature rises too much, it is possible to make the internal boiler is deformed to form cracks. Nitrogen is low boiler manufacturers emphasize To avoid this situation, one should control the Sheung speed and the water temperature, so as to be uniform so that the temperature rise in the inner and outer walls of the boiler, in order to protect the boiler is not destroyed. Second, to control the rate of temperature increase of the combustion process in which a low nitrogen boiler startup, with the temperature inside the pressure will rise together, so that both are simultaneously carried out, so control the rest of the wanted speed it is necessary to control the rate of temperature rise. And during the gradual lifting of the drum it will not only be a thick outer wall of a temperature difference occurs but also other parts of this will change so that thermal stress is generated, which for low nitrogen adverse boiler maintenance, is low nitrogen alert boiler manufacturers must control the thermal stress and reduce as much as possible to avoid excessive heating adversely affect important parts of the pressure line, flow orifice and the like. Third, the boosting speed should be adjusted during the low nitrogen pressure inside the boiler rises, the need to go through several different stages, and the pressure is increased by a certain entity, the increase rate is not the same saturation temperature of the working fluid, and the lower the pressure, the corresponding saturation temperature rise rate greater height and unit pressure as the pressure increased, increase in the saturation temperature of the water will become increasingly smaller. Thus professional boiler manufacturers of low-nitrogen of a boost very slow in the beginning, but at relatively high pressure until the situation can be improved appropriately boosted by adjusting the speed of impotence, because the pressure rise and temperature rise have mutual influence, it is not possible to separate transfers, must be considered to operate.
Mr. Lu Haigang mechanism for promoting the company's innovative company with a brief overview of the results related to the design and operation of the 24mv high pressure boiler in hospital were carried out on-site laboratory report. Mr. Jiang Zuojun hardware and software technology R & D infrastructure of the group now has a fully affirmed and expressed the company play a greater role in the adjustment of domestic environmental protection in low-emission structure expressed expectations.
Second, the difference in thermal efficiency
Also mentioned briefly in front of the thermal efficiency condensing boiler is higher than ordinary boilers, we will talk about further thermal efficiency. Why focus on how the thermal efficiency, thermal efficiency have so important? Of course, important! The level of thermal efficiency of a boiler directly determine the level of consumption of these boilers, in other words the thermal efficiency is related to everyone pocket money!