360kw electric steam boiler 360kw electric steam
The United States is our national enterprise, one of the world's top 500, with very bright glory on the world stage. US air-conditioning as a subsidiary branch, with a very large market competitiveness. 2016, Hubei US air-conditioning due to market demand to expand production lines, need to purchase steam boiler to provide energy support for the new production line. After the boiler industry for a number of enterprises contrast, is determined to cooperate with the fast boiler, buy a whole 10 tons of steam condensing gas steam boiler (WNS10-1.25-Y.Q).
Electric steam boiler is electrically heated by electrical power installed for the manner of thermal energy, so that the completion of the reaction the boiler, the steam output device outwardly, is a new innovation of "coal to electricity" policy.
First, before regularly shutting down boilers and inspecting electric furnaces, the following three aspects of preparation should be done: The main contents are as follows: (1) consult the technical file of boiler retrofit electric furnace registration and understand the use of boiler retrofit electric furnace. In order to make the boiler reform electric furnace inside and outside inspection, the general need to know: boiler transformation electric furnace design, manufacturing, installation situation; boiler transformation electric furnace transformation situation; boiler transformation electric furnace operation history and use situation; Boiler retrofit electric furnace water treatment, boiler rules and regulations implementation, and so on.
2) the preparation for stopping the furnace before inspection. First, according to the maintenance schedule, the furnace shutdown date is arranged, and then the boiler revamping electric furnace is shut down according to the normal shut-down procedure, so that the furnace is slowly frustrated. The cooling method can be adopted by injecting gas to dissipate the sinking water, replacing the furnace water for cooling, and cooling by ventilation in the in-line furnace. When the temperature of the furnace water drops to 70 ℃ 80 ℃, the water can be discharged. Open all the doors. When opening the door hole, prevent warm water, steam suddenly spurts out to burn people. The steam, feed water and sewage pipes in the furnace are separated from the corresponding pipes in the boiler revamping furnace in operation. The baffle used for partition should be strong enough to avoid being bulged out by high pressure media. Break position Clear instructions should be given. The flue which is connected with other boiler revamping electric furnaces should also be reliably separated. In addition, it is necessary to remove the soot and scale on the heating surface of the boiler retrofit electric furnace.
3) preparation of inspection tools and lighting. In order to ensure smooth inspection work, inspectors should prepare the necessary instruments, tools, gauges and safe and reliable lighting.
Hot water boilers are classified according to what conditions according to different hot water boiler fuel can be divided into electric water boilers, hot water boiler fuel, gas hot water boiler, coal-fired hot water boiler; can be divided according to whether atmospheric pressure and two kinds of hot water boiler pressure hot water boilers, hot water boilers we usually call refers to the atmospheric pressure hot water boiler, due to its safe operation, people bathing or heating largely adopted this pressure hot water boiler. 1, the tubular assembly Computerized water boiler controller, all the functions are stored on a smart chip, intelligent, digital boiler, automatic, user-friendly, intelligent control of boiler water, water reaches the automatic stop heating; large-screen font temperature, boiler water temperature at a glance. 2, boiler water temperature can be freely set from 10 deg.] C to 100 deg.] C, the boiler can supply both hot water bath can provide water for drinking, may be a dual oven. 3, the top of the furnace through the air opening is provided, the boiler is in an unpressurised state, there is no danger of explosion, while the machine is equipped with thermal protection (ultra-high-temperature furnace during the heating tube buzzer alarm and automatically stop working, secondary overheat protection (boiler housing temperature exceeds 105 deg.] C, the secondary circuit is automatically cut off), anti-dry water protection (when the furnace is less than the water level is very low, the boiler is stopped and an alarm beep), etc. .2 number of security, pot such hot water boiler drum cartridge type hot water boiler, early mostly modified from a steam boiler made, which in the case of boiler water within a boiler of natural circulation. in order to ensure safe and reliable boiler water cycle, the boiler requires to have a certain height, so such larger boiler, steel consumption, and the cost is relatively increased. However, since this type of boiler capacity and can maintain the natural water cycle, when the system pump is suddenly stopped, the pot can be effectively prevented vaporization of water. it is also for this reason natural circulation hot water boiler in our rapid development.