500kw coal boiler stoker grate boilers manufacturer
Wuhan Port District Social Welfare Institute (apartments for the elderly) is invested by the government pension services, with a total construction area of 38,000 square meters, 532 beds, mainly adopt destitute persons, social support on behalf of the elderly. Hope to provide welfare to the elderly year-round 24-hour hot water, the original 500kw coal boiler stoker grate boilers manufacturer equipment can not meet this demand, therefore, require additional purchase orphanage hot water boiler. After much investigation, in cooperation with the welfare determined fast boiler, provides three integrally condensing gas hot water boiler (WNS1.4-1.0 / 95/70-Y.Q) by a fast boiler.
Necessity textile mill converted to a coal-fired 500kw coal boiler stoker grate boilers manufacturer gas boiler is a boiler equipment industry needs is more important, because a lot of links to the papermaking process requires a lot of steam drying, stereotypes and so on. However, along with the national policy of environmental protection departments to ban coal-fired boilers, and now more and more manufacturers have to use coal-fired boilers to coal-fired boilers upgrading or purchasing a new low - NOx emissions. Mills from coal to gas boilers is an important direction of the current transformation of coal-fired boilers, is one of more types of enterprise transformation, especially in the area more natural gas, coal into gas boiler is the main way. 1, in order to transform mechanization layered fired boiler gas boiler, you should first remove the front arch and a rear arch, while increasing the bottom heating surface, instead grate, grate to prevent overheating, combustion; 2, through the furnace heat transfer calculation methods determining the size of the boiler, furnace flame center position, and then pouring furnace work. In order to avoid the center position after arch boiler tubes, based on the original slope of the original arch made pipe. 3, the furnace in order to prevent an explosion, when the coal-fired boiler furnace gas is substituted, or when fuel not atomized combustion gases in the furnace incomplete combustion or heating surface of the end of the furnace, a fire or explosion occurs, should be mounting the appropriate parts of the boiler explosion vent, and to increase the ignition and flame failure protection program control to automatic control means, to ensure safe operation of the boiler. 4, is closely related to the selection and arrangement of the burner and furnace, the filling degree of the flame in the furnace should preferably not to form a dead air. Gas burner arrangement considered reasonable and piping layout, convenient operation, inspection and maintenance;
Our state-of-the-art “Advanced Bio CFB” can co-fire high alkaline – quick growing agro biomass in utility CFBs. We are currently using this technology at the 280 ton coal CFB 500kw coal boiler stoker grate boilers manufacturer that we supplied at the Power Station in Mongolia.
Several factors underlie the vertical steam 500kw coal boiler stoker grate boilers manufacturer efficiency China has been working to catch on coal to natural gas, vertical steam boiler with greatly reduced contamination of dust, smoke and other effects of a nitric oxide gas has also been healthy curb. Efficiency is an important indicator of a measure of vertical steam boiler, a good number of factors under the topic to discuss the direct impact of vertical steam boiler efficiency began. After analysis of stakeholders, heat loss from vertical steam boiler contains two pieces: the proportion of full combustion air with flue gas emissions unreasonable heat loss. Heat loss can be reduced smoke emission can be installed at the end of the vertical steam boiler stack waste heat reuse install, or more leading system with condensing boiler. Combustion air ratio sufficient unreasonable faults into: general vertical ejector-type steam boiler burner selection, resulting in a motor fuel ratio can not be adjusted. Most of the selected vertical steam boiler is mechanically strong emission combustion engine, air-fuel ratio resulting irrational factors are the following: air-fuel ratio can be divided into two reasonable chance comprising: when the air in excess, the excess will have full cold It is heated, resulting in increased operating costs vertical steam boiler, steam boiler efficiency vertical drop; when the air is not enough, will produce insufficient burning phenomenon, caused by vertical steam boiler efficiency.