61 tph gas fired hot water boiler in hospital
WNS type gas steam boiler system control principle: ①, after WNS type gas steam boiler on the power switch, click on the pump control switch open position, after boiler feed water rises to the normal position, click-burner power switch, clicking the start button, the control system power is on, the burner into the working state, according to the operation program for the controller, to be re-ignition burner fires into the combustion state, the boiler enters normal operation this stage. ②, high output level when the water level rose to a high level alarm signal indicator light, when the water level rises to the pump stops running + 25mm, the water pump when the water level falls -25mmm automatic restart, when the water level falls -50mm, outputs a low level alarm indicator light, with bell sound, and cut off the power to the controller to achieve protection shutdown, -75 mm when the water level falls, the output signal of low water level indicator light. ③, when the pressure is raised 0.73MPa, the output signal of the first indicator light overpressure, combustion conditions and off the controller circuit, the controller stops the shutdown. Output when the pressure rises above a second overpressure 0.75MPa signal issued bell sound, alarm and cut off the power supply control system implemented emergency stop. Regulating the pressure when the pressure exceeds the upper limit, the controller output signal of a small fire fire closed valve, a valve to open the small kerosene ignition burner. When the lower limit pressure drops below the regulated pressure, the controller outputs the fire signal to open fuel valve fire, the fire to burn. ④, after the failure of the burner failure occurs, the burner control valve is automatically shut down to stop the oil combustion. Vertical coal-fired steam boiler structural features
How to avoid the food processing enterprises boiler water pollution? How to avoid the food processing enterprises boiler water pollution? How to avoid the food processing enterprises boiler water pollution? It is well known in the food production process, many sectors need to use boilers, such as cooking, faced with the problem of sewage treatment, also with a certain level sterilization, dry, wine and so on. In the country's growing emphasis on environmental protection, continue to increase supervision of enterprises under the enterprise adoption of what approach to avoiding disadvantages, complete sustainable development? Primary, flue gas collection equipment processing equipment. Since SMEs by financial constraints, skills, and other places, a time can not be cut all the transformation, it is possible, after passing through the coal-fired boiler exhaust gas purifying exhaust purification device tail device, such as a fume hood, an exhaust gas collection processing device, effectively to prevent the direct discharge of black smoke, a serious impact on the surrounding environment. Second, clean power conversion, such as coal gas, coal to electricity. I learned that a beer factory invested more than 10 million will replace all coal-fired boilers, gas-fired. Now, 180 tons of steam boiler plant now farewell all coal, burning a low nitrogen gas cleaning switch, effectively reduce pollution. And compared with previous coal-fired boilers, coal saving more than 80,000 tons per year business.
Henan run several areas, including Henan gas boiler gas boiler operation includes several aspects: daily monitoring and adjustment operations; accident treatment; start and stop; optimal operation mode and technology improvements. When the normal operation of the boiler, the daily operation of the monitoring and adjustment of the operating accounts for the major part. "Stable" is the key, pressure, temperature, water level, negative pressure, milling parameters, etc., remain stable conditions is an important guarantee for safe and economic operation. Briefly, the steady working primarily by "balancing" the means to obtain, for example, outside the furnace combustion conditions and load balance, the pressure is stable; to balance the amount of water and evaporation, is stable water level; primer with the supply air volume the amount of negative pressure equilibrium is stable, according to Henan gas boiler operation adjustment purposes, and in accordance with the purpose of regulating the boiler operation, to take the necessary means of regulation. Daily adjustment of the key - "steam pressure." Among the major parameters of Henan gas boiler, main steam pressure to maintain stability is the key which only the steam pressure is stable, the remaining parameters to stabilize. Unstable steam pressure, steam temperature, the water level will also change, so first of all start from the pressure adjustment. Vapor pressure is divided into an outer and an inner interference disturbance, our plant, i.e. outside the external disturbance load generally little change, so change in vapor pressure are changed within the furnace i.e. interference caused by operating conditions, so holding furnace combustion conditions the stability is the stability of the vapor pressure. If the combustion conditions change, such as wind than powder, coal calorific value and other factors change, a pressure change occurs, requires us to be adjusted, thereby changing into a stable state of the combustion furnace transient state conditions.
The only example of an ultra-low nitrogen oxide emissions through boilers Enterprise Test - fast boiler, the production of gas 61 tph fired hot water boiler in hospital, gas steam boiler, condensing boiler integrated, NOx emissions is far below the required standards, environmental protection departments successfully passed the test and get the user's praise.