automatic gas oil hot water boiler price
How to deal with Henan, gas-fired burner fault? Henan burner gas boilers are generally spray liquid, gas combustion, so smooth fuel injection and ignition becomes a necessary condition, a German boiler summed up the four points of failure, namely, ignition misfire stick, stick ignition spark but not on fire, extinguished or flashing when the fuel injection instability intensified, large burner noise causes of these problems are not the same, a German Industry and Trade Co., Ltd. Weinan spent vigorously before collected over. The first reason, Henan gas-fired burner ignition misfire produced rod has several aspects, plugging cracks, moisture, leakage, ignition gap distances different rods, skin damage, short circuit, improper operation of these reasons are not generated timing of maintenance As a result, the fault is not present it is difficult to process, as long as the gas-fired burner cleaning Henan, renewal, lane changing from the ignition rod can be solved. Henan also gas-fired burner ignition spark rod is mainly due to clogging of misfire, poor ventilation, the throttle angle is set too small, the distance from the leading edge tip of the firing rod inappropriate oil nozzle, the first solenoid valve is heteroaryl oil gun clogging, strainer clogging the pump itself, water and other large oil, this solution needs to be more trouble Henan, gas-fired burner cleaning, renewal, debugging, testing and other means.
Boiler and burner What is the difference? Simply put by the boiler and boiler furnace consisting Pot is the place to absorb heat, increasing the temperature is generally endothermic water, or water absorbs heat of vaporization of components, mainly heating water wall, etc. surface composition, and the fuel is coal furnace, where the heat released by burning oil, material, and other components mainly furnace while the burner is to provide a combustion apparatus of the release of energy, the material is spray combustion, combustion air.
Zhengzhou Sunrise Optoelectronics Technology Co., Ltd. by the Dongxu Group, Henan Province, the state-owned asset management companies and Zhengzhou Investment Holdings Limited jointly made, mainly engaged in flat panel display and solar industry design materials, manufacturing and sales operations. Sunrise Optoelectronics project has been put into a production line, the second phase will continue the expansion, three new production lines to meet the production needs of Project Phase II, Sunrise Optoelectronics urgent need to increase new boiler equipment. After investigation and screening of a number of boiler brands, determined to cooperate with the fast boiler, steam signed a 10-ton integrated condensing gas steam boiler (WNS10-1.25-Y.Q).
Matters needing attention in loading and installation of Gas-fired Steam Boiler
Gas-fired steam boilers are a very wide range of special equipment, usually built in boiler rooms. However, in the process of loading and installation, some problems must be paid attention to, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.