automatic gas or oil fired steam boiler
(Iii) use of a waste heat boiler for heat recovery. Using the waste heat boiler using waste heat discharged from the heat of the flue gas in a boiler to heat water or generate steam. Such waste heat boiler is provided thermal oil furnace itself does not change the fuel consumption, the waste heat boiler to produce steam or hot water may be used for the production and the occurrence of heating, thereby indirectly ADSF fuel savings. A waste heat boiler provided the following effects: First, since the heat recovery water, it is easy to improve the thermal efficiency of the furnace. Second, because the number of boiler flue gas can be centralized heat recovery, thereby reducing the cost of construction of the heat recovery unit.
In order to ensure boiler safety, to run smoothly, you must ensure that the use of high-quality natural gas. 1, equipped with one gas separator to increase the capacity, it can effectively store oil and water. Secondly, a level gauge designed to directly observe whether there is liquid in the separator. While the design of the automatic drain pressure relief device is installed. A single control pressure of the air is improved dual control, i.e. the pressure regulating valve is mounted on the main line to control the water separator, the pressure to stabilize, improve security purposes. 2, safety monitoring natural gas as a boiler room burning materials, natural gas leak monitoring must be done. The portable display technology poor performance, poor sensitivity. Host combustible gas alarm system with digital control scaling circuit having an alarm function and a secondary alarm, ensure the safe operation of the boiler. 3, check before firing the safe operation of: (1) whether the boiler inspection gates normally open or closed, check the gas pressure is normal, not too high or too low, open the supply valve leading to the boiler. (2) in the flue baffle must be fully open, otherwise it will affect the purge, causing accidents. Each knob and keep control cabinet to check the normal position. If the stove has a residue should be cleaned. (5) Check the boiler ignition and fire protection program control means should be flexible and reliable. Blast doors should be flexible and rigorous on the boiler. Before the completion of ignition, the ignition is not possible to start the ignition operation: After successful ignition, the load can be adjusted in the normal operation of the boiler when the combustion gas boiler adjusted. We should always observe the combustion furnace, and adjust the amount of steam, wind and steam pressure to ensure the safe operation of the boiler. Note: Program: first five minutes were furnace cleaning, automatic ignition after 5 minutes, observe the ignition is successful, the success of one minute after a small fire can be operated automatically converted to fire properly. For the boiler load and the air pressure adjusted by adjusting the pressure regulator to achieve. When adjusting the load, adjust the air pressure at the same time, it must be synchronized to adjust the air flow to ensure a reasonable match air volume and air volume, in order to achieve economic operation of the boiler. In normal operation, the amount of gas should not be adjusted or reduced drastically in order to avoid dramatic changes in combustion, the pressure receiving member sudden expansion, shrinkage and damage. When the boiler is running, the pressure gauge must be monitored regularly in order to maintain stable water pressure. BCP pressure changes observed, reflecting the relationship between water temperature and steam consumption. In the boiler operation, when the steam pressure is automatically adjusted, the main purpose of the staff is to monitor automatically adjusts the boiler system is sensitive and timely solutions to problems and ensure the sensitivity and reliability of the automatic control system. 4, first close the main valve shutdown operation, the air supply is stopped, the circulating pump and the water pump is still running, when the boiler water temperature falls below 70, and supplies or stops the circulation pump in operation of the pump after about 4 hours. Note: In addition to the accident and emergency parking stop, parking general approach should not cut off the power. After the shutdown, it is timely for the boiler and ancillary equipment to conduct a comprehensive inspection. If you find a defect in the device, and repair should be recorded at the time of shutdown. Safety Precautions 1. burner startup, if the burner is repeatedly locking and alarm, you should find out the cause of the malfunction, press the reset button after troubleshooting, press the reset button and then continue to boot. Note: Press the Reset button for less than 10 seconds. A lower burner inlet must be clean and clean, and does not allow offal. 2. burner once the ignition is unsuccessful, Boiler Fan should be restarted. Ventilation After 5 minutes, start the second startup burner igniter. three. During normal operation, the thermal device near the burner portion (e.g. flange connections) will be very hot, in order to avoid burns. Do not put flammable materials in the vicinity so as not to cause a fire. 4. The operation of the boiler circulating pump must be closely monitored and the hot water boiler pressure, gas distributor, pipeline valves, pressure gauges, flow meters, water level gauge and the like. 5. When the firefighters open the door or fire door observation, you should wear gloves and a side view. 6. A burner working environment should be kept clean and dry, in particular, a flame detector (i.e. electric eye) should be kept clean, part of the control circuit should humidity and temperature; class should cleaning and maintenance of a combustor. 7. During use, the filter should be cleaned regularly check or replace the filter cartridge in accordance with impurities of the fuel. 8. Check the electrical installations include: wire is damaged, the sheath is damaged, the screw is loose, the contact is good, whether the motor is running abnormal noise. Describes the advantages and disadvantages of natural gas boiler, editor of Sin sets introduced, the use of technology and safety precautions. Industrial boilers to energy efficient, environmentally friendly development direction. Natural gas boiler to meet the needs of these three points. They are the future of the boiler market trend, more and more restricted energy policy, energy saving and environmental protection requirements.
25 tph SZS gas-fired automatic or oil fired steam boiler for cigarette factoryFrom 2014, Baoji City began to implement natural gas projects and vigorously implemented coal-to-gas conversion projects. Baoji Cigarette Factory is one of the major backbone enterprises of the China National Tobacco Corporation and is the largest cigarette manufacturer in the northwest region. In line with the environmental protection policy, Baoji Cigarette Factory implemented the "coal to gas" project. Through bidding activities, it cooperated with ZOZEN boiler to dismantle 35 tph coal-fired boilers and install 25 tph SZS gas-fired steam boilers to improve boiler operation levels and reduce air pollutant emissions.
The "national industrial energy-saving technologies and equipment Recommended List (2018)" key recommendation "premix wing-type vacuum condensing hot water boiler" There is a beautiful name - Thalia T6, through the rational use of the U-shaped smoke tubular, cross-wing type tube design structure, and heat transfer at the same time meet the thermal requirements, reduced to 33% of the entire area of the boiler can be placed in a small area in the boiler room. At the same time the use of advanced industry premix combustion technology, will reduce nitrogen oxide emissions to 18 mg / cubic meter, well below the most stringent air pollutant emissions of Beijing, Tianjin, Zhengzhou and other cities 30 mg / cubic meter standard.