automatic steam generator coal water slurry boiler
Electric steam boiler is heated in the drum is an electric boiler into steam energy conversion device, the energy input to the boiler fuel chemical energy, electrical energy, thermal energy and other forms of high temperature flue gas, the boiler after the conversion, externally output having some heat steam, hot water or organic heat carrier. Refers to the original meaning pot heated on fire water container, electrical means boiler furnace manufacturers place combustion of fuel and a boiler furnace boiler consists of two parts. high degree of automation. Such equipment is mainly convert electrical energy into thermal energy. Heating on the fire water containers. Generating hot water or steam boiler may directly provide the necessary heat for industrial production and life, but also by steam power plant into mechanical energy, or through the generator converts the mechanical energy to electrical energy. Provide hot water boiler known as hot water boilers, industrial production is also a small amount applied. Boiler steam is known as steam boilers, often referred to as boiler, used for power plant, ships, locomotives, and industrial and mining enterprises. But to the technical system energy use; second only to emphasize the cleanliness of clean energy while also emphasizing the economy; cleanliness third clean energy refers to meet certain emissions standards. Refers to an electric steam boiler water heated to a certain temperature parameters, and the production of industrial steam boilers, boiler manufacturers electric pot original meaning refers to the heated water into the steam drum, the fire in the furnace emits heat, a steam boiler of the principles.
How to choose energy saving gas heating boiler? Most of the field of construction, industrial, life needs to be heating boiler, then what the election or steam boiler hot water boiler heating? How much tonnage, how many? And how to make energy-efficient and environmentally friendly choice of boiler it? These issues will no doubt cause great distress to the customer, the following solve these problems, we can do a simple discussion, consider providing some feasible ideas. A. How to determine the tonnage and the number of boilers must first be calculated from the area of heating and domestic hot water heat demand of the total amount for this issue. Meanwhile, in the calculation of the process, also taking into account factors external architectural features heating areas, temperature characteristics, the peak water heating, etc., due to local conditions at the time. Then, after completing a comprehensive evaluation, will be able to consider the issue of tonnage and number of units furnace, then how should the election, which requires analysis to analyze the results of previous projects using features of the boiler, but also to figure out the actual boiler operating efficiency, as well as tonnage and heat supply matches demand real problem customer site. II. When selected gas heating boilers, steam boilers or hot water is selected by boiler application analysis of many companies, both on a simple comparison, you will find hot water boiler will be energy efficient than steam boiler, so if there are energy-saving project demand, suggested the use of hot water boiler. Of course, both need something like hot water and steam needs, you need to hotels, hospitals and other places to determine the actual situation. If the hot water heating system using a large amount of steam required is very small, it is recommended to configure another small steam boiler or automatic steam generator coal water slurry boiler outside of the hot water boiler to meet the needs of a small amount of steam. For example, hospital star hotel or on the amount of steam demand does not exceed 30% of total heat demand, and based on actual experience, in addition to a steam boiler efficiency problem in itself a significant attenuation in the low load operation outside the state, the system energy loss larger, final energy efficiency is generally only about 60%, serious waste of energy. III. How to select energy saving gas heating boiler from the heat required systems, combustion systems, control systems and other consideration, and that is in heat transfer systems, taking into account the use of materials heat exchanger, steel, copper or iron, which according to their comparative property, currently used is copper; combustion system is the key to deciding whether the boiler equipment, energy saving and environmental protection. Current common combustion are: full-premixed, atmospheric premixed and diffusion. But just in terms of energy savings, premix technology would be more advantageous, it pre-mixed air and gas, multi-mode radiator heat, the intensity of the heat transfer improved. The advantage of using this method is that the combustion flame combustion clearer, and higher thermal efficiency. In short, the selection of gas heating boiler is a more complex issue, it requires theoretical and practical circumstances combined into consideration before they can get a reasonable result.
After the project identification, party fast technical staff soon made contact with our company, to our installation, commissioning, to ensure the look normal, stable use during boiler operation. Thanks fast boiler professional technical support and good service, I provide a lot of help for the textile dyeing and finishing production company. --customer feedback
Heating boilers partial failure of boiler pressure controller controls the generator, because there is no water showed no the control circuit board, which is mainly controlled by heating the liquid level control float. When an appropriate amount of water, floating on control splendidly floating-point voltage, so that the boiler applied AC contactor work, start heating. This simple structure generator, the current market use more circulation. Such a generator common fault is not heated, mostly appear on the float level controller. First check the external wiring float level controller, whether the control point of the vertical line connected pair, and then split the float level controller, to see if it floats flexible. Then you can use the manual, the heat upper and lower part of the fault can be turned on by the control point whether the amount of the multimeter. After checking everything is normal, then check whether the water tank float. In other words it can float, i.e. the fault is rectified.