china gas heating hot water boiler machine
How to prevent gas china heating hot water boiler machine explosion gas hot water boiler belongs to the category of special equipment, thermal equipment and is a frequently in high pressure high temperature state, it is inevitable some small problems that may occur during operation, this is normal; but if not in place or because of negligence, they are likely to make the boiler exploded. So, for safety equipment and personal safety, we have to understand some common sense prevention hot water boiler explosion. 1, hot water boiler furnace explosion prevention occurs first on the boiler design, should be strictly thermodynamic calculation and strength calculation in accordance with the requirements of GB50041-1992 "boiler room design specifications", the structural arrangement should be reasonable, material quality should meet the requirements. Boiler manufacturing, construction plans should ensure compliance with national quality boiler scale delineation. Boiler safety accessories should be complete, agile and reliable, and maintenance schedule, often check on the failure of the attachment timely replacement. Schedule for maintenance of the boiler, the outer part of the boiler maintenance, subject to the existence of timely repairs and reconstruction to ensure test quality standards. 2, prevention of fuel, gas hot water boiler furnace explosion at the point of blast furnace to double-check each gas line, oil line is tight (leak), pressure is normal, Installation and reconstruction of new oil and gas pipelines necessary to purge and clean. Check the ignition lead before the drum whether the fan has to take the air 5 ~ 10min, after ignition failure to analyze the reasons, and then restart the ignition process to take the air ignition. Boiler use permit and inspection certificate did not apply for the boiler, furnace stokers right to refuse point. Enterprises should choose a fireman permit manipulation of experienced fireman point-furnace work, fireman staff should strengthen the inspection tour, identify problems in time to prevent the flame; flame once found, should immediately cut off fuel. Boiler installation should be controlled protection device, comprising an automatic ignition, flame protection, automatic adjustment of combustion and the necessary alarm chain protection.
How natural gas steam boiler steam boiler model selection natural gas main type WNS and SZS type Both models can burn natural gas, liquefied petroleum gas, coal gas, coke oven gas, biogas, including steam boilers and china heating hot water boiler machines, gas concrete how the selection of steam boilers, we take a look. Due to the different sectors of production processes, demand for steam boilers are also different, and therefore, when the gas steam boiler selection, need to have enough knowledge of the production process, in order to make the right selection and design of the boiler. 1, selection of technical parameters: gas comprising steam boiler rated evaporation, rated steam pressure, steam temperature rated, e.g., general pressure chemical production requirements are not too high, the pressure required to produce 10 kg as an example, then the boiler design pressure of 1.25 MPa is necessary to use; 2, ancillary equipment options: supporting auxiliary gas steam boiler main control cabinet, water supply pump, circulation pumps, burners, sub-cylinder, water treatment equipment, energy, a condenser, users can choose according to their own needs and price configuration; with the Earth's atmosphere deteriorating, I believe that we Chinese citizen environmental awareness is still very strong, in order to reduce pollution of the planet, we must first consider how environmentally friendly energy-saving performance, then consider fuel, gas boiler combustible gases, polluting emissions, environmentally friendly energy-saving ideas. Boiler pressures, consider the problems caused by an explosion caused by overpressure, and even carbon dioxide poisoning incidents. In the control of gas-fired boiler operation, select the better it is simple and easy to operate.
Gas boiler installation and preparation requirements of (a) the preparatory work before the installation of a boiler installation must be installed by the unit has installed a license .. The installer must be familiar with "Boiler Safety Technology Supervision", and carefully read the installation instructions and other random technical documents. 2, a mounting position: 1) as close as possible to install a boiler steam, hot site, to facilitate shortening the hot water and steam pipes, reducing capital costs, reducing the pipeline heat loss. The installation site should be water supply, sewage convenience. Burning light diesel oil, heavy oil residue and the boiler must be closer to the oil reservoir; burning natural gas, town gas boiler must be easy to close the gas source. 2) boiler room layout should follow the "Boiler Safety Technology Supervision" relevant provisions "boiler room", to be well-lit, well-ventilated, no ground water, ease of operation and maintenance, boiler room must be equipped with at least two fire extinguishers 1211. 3) Check the boiler foundation, prepare the boiler in place. 3, equipment acceptance: acceptance by conduct an inventory purchase contract or supply list. 4, lifting large boiler: not less than 1.1 times the lifting equipment of large weight of the boiler, two lugs for the lifting jack top or at the bottom edge away slowly, not to any other parts of the lifting or addendum to avoid damage to the boiler. (Ii) installation requirements: 1, the main steam line installation requires the main steam lead pipe height is generally greater than 0.5 m, the bending radius should be greater than or equal to 5 times the diameter of the pipe, the pipe should be installed at the lowest trap, preventing water pipe, It should be a main steam pipe insulation. 2, a main return pipe installation requirements should the main return pipe elbow minimize installation, to facilitate the mounting operation of the valve, piping should be insulated. 3, the hydrostatic testing relief valve, the safety valve should be installed in the exhaust pipe, the exhaust pipe connected to the straight pipe outdoor safety. 4, should be connected to a sewage outfall tank or other security, the pipe should be secured to prevent shifting or counter scald accidents blowdown. 5, railings, stairs (with large oven) after the positioning by drawing the boiler installation. 6, water table must be installed to the lighting device, easy to install or inspection.
As a leader in the fast side condensing gas boiler, in recent years, provide a clean boiler to Beijing multiple office units, was well received. I units through the preliminary investigation and contrast, select fast boiler, it turns out, party fast product does have quite a good cleaning environmental performance, in line with the Beijing municipal government requirements for air pollution emissions, the use of very at ease. --customer feedback