china manufacturer steam boiler horizontal gas
In recent years, the state environmental protection is all the more attention we as a company with the times, in order to respond positively to the implementation of the national environmental protection requirements from coal to gas project. But the choice of boiler suppliers in this area quite a headache, after repeated comparison and investigation, we chose to partner with fast boiler. Fang did not disappoint quickly proved that the recommended boiler operation after use to fully meet our needs, both energy saving and environmental protection, high thermal efficiency, to a certain extent, cost savings for our fuel. --customer feedback
More details gas boilers should be promptly after use as a china manufacturer steam boiler horizontal plant drainage, heating, bath with gas boiler is a kind of fuel for the gas equipment (fuel gas-fired boilers), because it is compared with oil-fired boiler, electric boiler up more economical, which is widely used. After carrying out the gas boiler must turn on the water to be disabled. Why is that? We will come and detailed discussion about this issue today. To turn on the water when the gas boiler is disabled: gas boiler in the boiler water if the winter will put the cracking, there will be odor and summer long embroidered, so that the life of the boiler will be reduced. At the bottom of the boiler there is a turn on the water with the section of the door, then opened, gas boiler pipes in the water will flow back to the boiler, the boiler is done and the water on it. Water level controller SZB-IV (electrode type water level alarm) 1. When the normal level of + 30mm, pump control switch contacts are open, the pump stops working. 2. When the normal water level -30mm, pump control switch contacts in contact, the pump starts to work. 3. When the normal water level of + 50mm, a first group of electromagnets high gas boiler water level contacts the combined output high level alarm signal. 4. When the normal water level of the gas boiler -50mm, a second group of electromagnets in conjunction with the low water contact output low water level alarm signal.
The reason the gas boiler burner increased noise analysis when making use of the gas boiler and found this small fire normal, but this time turn the fire, extinguished or flashing instability. First speaking, that is because of this fire damper of the air volume setting is too large; i.e. after an oil fire because the micro-switch valve (damper outermost that group) inappropriate setting (set lower than the fire damper of the air flow larger) burner gas noise increases, mostly because the oil shut-off valve which is closed or lack of oil into the oil filter clogging; or, this is because of low temperature into the oil, the viscosity is too high or the pump into the oil temperature is too high; oil pump failure; fan motor bearing damage; there is because the fan impeller dirty equipment resulting in large noise. The above-described failure when using gas boiler, but also because the viscosity is too high oleaginous easy to be atomized (heavy oil); cyclones and because improper disc and the nozzle pitch; Note that because the fire is worn or dirty nipple; also because this preparatory tank the heating temperature is too high, causing the oil pump oil feed steam does not conform; or because the fuel inside the boiler resulting aqueous oil. When the above-described fault gas boiler used to perform this process, the test should be done gradually decreases; after heating temperature should be; adjusting the distance (between 0 ~ 10mm); clean or replace; is set to about 50 deg.] C to about; or drain oil change.
11.Steam exiting the high pressure steam turbine is called cold reheat.
It is reheated in the re-heater and sent back to the second steam turbine. By the time the flue gas exits the boiler most of the energy in the coal will be transferred to the water in the boiler. The hot gases are cleaned up before they are sent to a stack. Feed water is generally supplied by condensed steam from the low pressure steam turbine. Large amounts of cooling water are used to condense this steam into liquid water in the condenser.