dzh series water and fire tube biomass boiler
Bagasse biomass fired dzh series water and fire tube biomass boiler for sale in ZG Boiler is mainly used in industrial production, and it can be applied in paper mill, textile mill, oil refinery, chemical industry, sugar mill, brewery factory, food plant and it can also be used to central heating, district heating and many other places where need steam or hot water. Among these applications, bagasse fired boiler for sugar mill is the most popular one.
Shandong Mining Group in the six months after the dzh series water and fire tube biomass boiler use, users submit a report to our company, our company started in 2017 using WDR0.5-0.8-Ⅱ electric fast Boiler Co., Ltd. of heating steam boiler. Large output, stable and reliable, high degree of automation, simple operation, do especially in terms of security is in place. After-sales service is very timely response to our technical consulting reply quickly and accurately. Whether it is party party products or fast fast service. My company is very satisfied. --customer feedback
How to deal with the failure of the gas burner dzh series water and fire tube biomass boiler? How to deal with the failure of the gas burner boiler? Gas boiler with a combustion burner manner generally ejection liquid and gas, so that stable fuel injection, ignition a necessary condition. Biomass boiler categories: biomass boilers Horizontal, vertical biomass boilers. Biomass gas thermal oil heaters, biomass steam boiler, biomass hot water boiler, biomass oil furnace. Boiler summarizes the four points of failure. Cause of these problems is different, not as ignition rods ignition, spark ignition rods single ignition, fuel injection increased strength unstable flicker noise large burners. The reason for these problems is different, the boiler needs to pay a lot of effort to collect them. First, the reasons many ignition misfire rod, such as clogging of the seam, moisture, leakage, ignition rods of different gap distances, skin damage, short circuit, all these reasons and due to improper operation caused by unscheduled maintenance. Troubleshooting not very difficult, can solve the cleaning, changeover, the ignition rod spacing problems.
Steam dzh series water and fire tube biomass boiler preventive measures introduced Common Failures and precautions steam boiler and steam reciprocating pump 1. Biomass boiler is a kind of boiler to biomass energy as a boiler fuel called biomass boilers, steam boilers into biomass, biomass hot water boiler, biomass stove, biomass thermal oil heaters, vertical raw biomass boilers, biomass boilers and other horizontal. Fuel gas boiler is not only fuel but also refers to the gas boiler. Previously no such dual-fuel boiler, burner because either fuel or gas, no dual fuel burners. With the rapid development of the world energy equipment, some European countries begin production and sales of fuel gas burner, dual fuel burner and boiler combination of organic birth of a new breed of boiler - fuel gas-fired boiler. Near the steam boiler room should be equipped with adequate and effective fire fighting equipment. 2. Steam boiler room must have staff on duty 24 hours, the guards take turns, and always check the water level in the boiler, in order to ensure that it is above the safety line to prevent an explosion caused by burning dry. If the fire operation in explosive areas must obtain a work permit fire and take adequate fire safety measures in order to carry out fire work. When the fire should send someone on duty at all times observe the fire situation. 3. A storage vessel containing the non-flammable gas in the boiler room. 4. The staff of steam boiler room must be certified before the arrival of the boiler and proficient technique, it has a certain capacity to detect and recognize security risks. 5. If the boiler safety on a regular basis in accordance with the boiler maintenance procedures, should be carefully examine each of insecurity in the inspection process. 6. Distribution Line steam boiler room disposed defective safety device using a metal tube or pipe nonflammable hard plastic protection switch box should be installed outside the boiler room, respectively, to achieve power, should be prohibited. 1. What is the reason there is no discharge of steam reciprocating pump is? How, how? A: (1) Failure: 1 suction or discharge pipe blockage. (2) out of the stuck valve. There is an air cylinder. (4) a suction tube connected lax. (5) column (live) seriously damaged piston ring. (2) Method excluded: (1) exclusion of pipe blockage. (2) Remove the inlet, the outlet valve on the plug. (3) filled with water, the air is discharged. (4) fastening the pipe. (5) Replace Column (live) piston ring.