electricity natural gas steam boiler supplier
Corner tube steam electricity natural gas steam boiler supplier is one type of chain grate steam boiler. ZG manufactured corner tube biomass fired steam boiler’s power is among 6 to 15 MW. This biomass fired steam boiler adopts corner tube pattern, self-supporting structure. The furnace and the descending fuel gas duct adopts total welding membrane water cool tubes wall structure, which has benefits of good sealing, lower heat reducing. Both air pre-heater and economizer adopt case pattern structure which is convenient to transport and install. As a top steam boiler manufacturer in China, our single drum corner tube biomass fired steam boiler made in China is both eco-friendly and high efficiency.
SUMMARY gas steam electricity natural gas steam boiler supplier maintenance gas boiler twice monthly maintenance inspection item A. Fuel supply line: a filter cleaning gas oil; ignition gas conduit 2 airtightness inspection; 3 checks whether the flow line... B. inspection of the instrument: a flushing water table; 2 Syphons flushing; valve experiment. C. Check burner:.... The flame detector (photocell) cleaning the light receiving surface; second inspection oil pump pressure is normal; 3 checks the combustion flame is normal; 4 check burner, the burner sound is abnormal; 5 Cleaning revolutions cup; 6 o'clock washing water rod. . Check D. Intake system: a washing water filter; 2 reaches rated pump head and flow; 3 a check valve is working properly... E. daily drainage tank and the cleaning debris. Water quality testing, water testing furnace. F. Check the combustion consumption is normal. Every three months in addition to the maintenance items plus the inspection item inspection items: Electric Part A: 1 line is loose aging, failure; 2 check the reliability of electrical components, overload; Protection relay 3 is normal; B.... open soft low deactivation tank valve exclude sludge; C to test the boiler and then point interlocking means: 1. low water position; overpressure 2; 3 flameout 4. The exhaust gas temperature ultrahigh; D. et quality tobacco. detection: analysis of tobacco smoke constituents comprising temperature detecting tail, combustion is working properly checked. E. burner and boiler cleaning outer cleaning. Paul A. large projects each year hosts a body part of a comprehensive clean-up tobacco pipes, water pipes, front and rear smoke box, part of the furnace and the burnout chamber and smoke tubes ash collection. 1. inspection openings comprehensive inspection hole hand hole, manhole sealing soundness, and timely replacement of defective seals. 2. The overall comprehensive testing instruments, valves, comprising detecting pressure gauge and safety valve, the pressure controller and the electrode level controller tuning. Part B. burner: Burner cleaning turn round cup, ignition means, filter, pump, motor and impeller systems, throttle link means to add a lubricant. Re-awarded for combustion testing. C. access control section detecting electrical components, control lines, the control box clean ash collection, each control point is detected. D. water supply system maintenance water treatment plant to check whether water quality standards, a comprehensive clean soft water tank, to check the functioning of the pump and lift, clean check valve spool and so on.
How to use gas-fired electricity natural gas steam boiler supplier gas boiler includes a gas water boiler, gas hot water boiler, gas steam boilers, gas hot water boiler which is also known as gas heating boilers and gas boilers bath, as the name suggests refers to the gas boiler fuel gas boiler, gas boiler and oil-fired boiler, electric boiler comparison economy, so most people have opted for a steam boiler equipment gas-fired boiler, heating, bath with. 1, boiler water, softening the first, but also to clean the water quality can not be an impurity. 2, gas boiler before the fire, you want to view the valve pipes, steam pipes, water gauge, pressure gauge and drain valve and so on, whether it is intact, whether the normal use. 3 and can not be conditioned to avoid rendering problems. If the gauge to reach the promised 80% working pressure, to avoid excessive pressure. 4, the water table in a glass tube, which should consolidate outer shield, but also to clean and tidy. How should the functioning of the water table at any time of the investigation, if any anomalies should be handled immediately. 5, when the gas boiler shutdown urgency, you want to cancel burning, then closed throttle, then open the door and release valve, the order can not be inverted. 6, when the pressure rises quickly, when and beyond promised to work pressure or boiler annex presents the phenomenon of failure, or a furnace, ducts appear deformed, when leaking air leakage, urgency should be shutdown immediately.
It is reported that in March 15, Chifeng City, a special inspection of the pressure to carry out an internal inspection of industrial gas and steam electricity natural gas steam boiler supplier upgrade skills than the ability to test cum activity. Chifeng City, the special prosecutor, deputy director Jiao Wenxiang, deputy chief engineer Wang Shusen, deputy chief engineer Zhang Yulin and a pressure test of all personnel to participate. The ratio of the activity is divided into document review, site inspection, inquiry exchange three links, the city of Chifeng hotel comparison site inspection in WNS4-1.25-Q type of boiler.
In the field, compared to persons in accordance with the "boiler periodic inspection rules," "Boiler Safety Technology Supervision" and other relevant standards, test preparation equipment industrial gas steam boiler inspection, the document review, site inspection programs, projects, methods, inspection found defect assessment and treatment, inspection records and test the views of notice to fill in field operations and other aspects of comparison. Then the referee group of inspectors to participate in the comprehensive assessment ratio, the final nine inspectors compared the results were satisfactory. The ratio of inspectors to participate have said, by building a mutual learning platform for the exchange ratio of activities to enhance their own inspection techniques, in order to better carry out the annual inspection lay a solid foundation.
After comparison, the assessment team for each ratio of staff present in the actual operation problems raised rectification, so that each person than to recognize their lack of inspection in the presence of, as well as their ability to enhance the tailored inspection Program. In the future, I will continue to strengthen and enhance the inspection capabilities, adhere to the bottom line of thinking and problem-oriented, to provide a solid technical support for the safety of special equipment to hold the bottom line.