energy efficient gas oil heating boilers
Select the first steam energy efficient oil heating boilers to know what parameters? Steam boilers have the following main parameters: 1, Rated evaporation Rated evaporation is power steam boiler, steam boiler is the most important parameter, usually expressed in tons evaporation, that is, we usually say how many tons of boiler. 2, rated steam pressure rated steam pressure means that the steam pressure generated in the steam boiler, generally expressed in MPa or kg. 1MPa is 10 kg, like laundry, all hospitals, factories and the like conventional steam occasions the general use of low-pressure steam 1.0MPa or less. Only when using steam as a power to require the use of high-pressure steam. 3, where the steam temperature of said steam temperature, refers to the temperature of saturated steam. Saturated steam pressure and steam temperature are corresponding. Temperature of saturated steam at a pressure of 1MPa 184 ℃. 4, gas / oil / coal consumption fuel consumption is an important indicator of concern when choosing a steam boiler, which is directly related to the use of the running cost of the boiler. In the operation of the boiler, the fuel cost is very impressive, if just considering the purchase cost of buying a cheap but high energy boiler, which led to the late high operating costs, certain that it will be wasted. 5, the thermal efficiency of fuel consumption with the boiler thermal efficiency of boilers is inversely proportional. The higher thermal efficiency, lower fuel consumption of the boiler. Boiler thermal efficiency expressed as a percentage, the value is a more intuitive. 6, the boiler operating weight, size or location in the election of the steam boiler, it should find the place whether the load per unit area can withstand the weight of the steam boiler, and if there is enough space to place the steam boiler maintenance and reserve space.
Analysis and pressure steam energy efficient oil heating boilers burning issues of excessive treatment: this kind of boiler steam boiler, because it is an important site for the product, so in their knowledge and understanding of the, at least, should achieve a comprehensive and specific to this extent, so in order to further the product site, rather than just stay on the surface, and then, in the use of the product, there is a good use of effects. Therefore, in order to achieve the above objectives, the following will continue this topic, which reads as follows. 1. steam boiler, which is in use, whether the boiler must first obtain use permits, and then to use this kind of boiler? In addition, if classified according to their fuel, then, in particular, which has several? Steam boilers, because it belongs to special equipment, therefore, can not be directly used, relevant departments should first obtain use permits issued by the boiler, and then to use steam boilers. In addition, this kind of boiler, if classified according to the type of fuel, then, can be divided into three electric steam boiler, gas steam boiler and steam boiler fuel.
How to set the height of the energy efficient oil heating boilers chimney
The coal fired boiler can be divided into two kinds：vertical boiler and horizontal boiler. And the horizontal boiler is very economic because of its long flue gas flow, slow smoke discharge, high heating efficiency. So it is widely sued in the market. After buying a boiler, it is necessary for them to build a boiler room,in the installation the height of the chimney also need to pay attention. According to the ZG engineer, the chimney height should be accordance with the lowest height of GB13271-2001 stipulation. Only one chimney is allowed in a boiler room. The specific requirements was listed below:
1.When the boiler’s output capacity is more than 1t/h or 0.7MW, a permanent thief hatch and relevant facilities should be setted in compliance with the stipulations of measuring method for smoke and dust of boiler emission, and The determination of particulates and sampling methods of gaseous pollutants emitted from exhaust gas of stationary source.
2. The exit diameter of the chimney should be not lower than the largest load. The smoke flow should not be too fast. when the load of the coal fired boiler is at its lowest level, the velocity of the chimney exit should not lower than 2.5~3m/s.
3. If the chimney heat does not reach the height of the above stipulations, the maximum discharge concentration of the dust,sulfur dioxide, nitric dioxide should be carried out at 50% of the corresponding area and time emissions standard .
Recently, China's 21th National Assembly HVAC academic year in "Swan City" - Sanmenxia City, Henan Province began. This annual meeting embodies the HVAC industry leading experts, technical design schools scientists, representatives of major HVAC manufacturers and industry media, nearly 20,000 HVAC colleagues attended the meeting.