factory direct sell natural gas steam boiler
Water wall boiler tube leak or burst phenomenon how to do 1, the normal water flow is not greater than the steam flow. 2, the furnace pressure transient and unstable prejudiced. 3, tube leak detection alarm device. 4, the furnace may not tight at the outward discharge gas and water vapor, and a significant leakage sound. 5, the main steam pressure drop. 6, boiler combustion dark flame instability caused by severe boiler fire. 7, when the induced draft fan is automatically cast, abnormal static vane opening is increased, the current increases. 1 reason, the presence of water wall tube material defects or post-production, the installation of the damaged pipe, poor welding quality. 2, the inner tube fouling overtemperature. 3, the inner tube corrosion. 4, water wall wear. 5, the long-term high load operation, furnace coking, coal sulfur corrosion caused by high temperature water wall. 6, improper combustion, flame deflection. 7, in the possession of bad foreign body, the water cycle. 8, the wall of the long-term over-temperature operation. 9, the temperature difference between waterwall tubes, mechanical stress crack. 10, the normal exit or drain sootblower steam punctured tube. 11, smashed chunks of coke furnace water wall tube or serious explosion occurred, resulting in water wall tube suffered external damage. 12, boiler overpressure long run. 13, the boiler starts to heat up, step-up too fast. 1 process, the leakage should try waterwall tubes outage. The leakage is not serious, while still capable of maintaining operation, note that each of the automatic operation when the device, if not normal, it is cut immediately to the manual, if necessary, may be down, down-load operation. Closely monitor the development trend of damaged parts, good accident anticipation, application shutdown as soon as possible. 2, if the leak is serious, the bursting point temperature after a sharp rise in quality work, leading to serious over-temperature wall, unable to maintain the normal operation of the boiler or threaten the safety equipment, emergency shutdown provision should be processed, when the steam temperature to protect the action value, the protection does not move, should immediately hand MFT. 3, note that the operation of the electrostatic precipitator, to strengthen the inspection checks, to prevent fouling, and the electrodes ESP hopper, pipes and the like plugging air preheater ash. 4, after the shutdown, should retain ID fan, the furnace pressure is maintained constant, there is no discharge to be stopped after soda ID fan.
Inner Mongolia Autonomous Region Development and Reform Commission issued a notice publicity Inner Mongolia clean heating in winter embodiment (hereinafter referred to as "Notice"), "notice" mentioned that in 2019 the region to achieve clean heating rate of 50% in 2021 to reach 705; urban built New forbidden zone 35 tons of steam / hour and below the coal-fired boilers, which Hohhot, Baotou, Wuhai city urban area will phase out 35 tons of steam / hour and below the coal-fired boilers, all new buildings to achieve clean heating.
The region's total heating area of about one billion square meters of urban heating an area of about 750 million square meters, of which: decentralized heating an area of about 090 million square meters; central heating an area of about 660 million square meters, heating rural area of about 250 million square meters, of which central heating an area of about 027 million square meters, the rest are dispersed heating.
Urban areas mainly in the CHP and district heating central heating boiler room mainly to gas, industrial waste heat, wind power, solar and other energy sources to supplement heating. Rural areas with decentralized heating the main heating source mainly scattered coal-fired boilers, conventional coal-fired furnace or straw.
Urban district heating cogeneration accounted for 51.5%, the proportion of area of 43.6% heating boiler, gas heating accounted for 4.5%, the proportion of the heat pump in other ways, electric heating and the like about 0.4%.
To clean as the goal, in ensuring the safety of people's livelihood heating premise, overall thermodynamic equilibrium between supply and demand, either alone or using a combination of various cleaning heating mode, alternative urban area and would like to keep burning coal for heating casual, less warm air pollutants areas emission. Adhere to safety bottom line, build a reasonable size, safety and reliability of heat supply systems.
2, according to local conditions, the residents can afford. Based on natural resources, economic strength, infrastructure around such as regulation and install air pollution control requirements, scientific assessment, depending on the region to its own characteristics, full old people's consumption capacity, adhere to both energy security and clean development, should power the electricity, should be coal is coal, the gas should be air, clean heating strategy adopted XI, to promote its low cost and low pollutant emission cleaning combination heating under the same conditions.
Considering the urgency of the air pollution control, affordability, work to promote the difficulty and other factors, co-ordinate the work of promoting cleaner heating city, county and urban-rural.
1. oil and gas factory direct sell steam boiler system
A complete gas boiler system mainly includes the boiler body, burner, control system and other auxiliary structures
Gas & oil fired factory direct sell steam boiler
Steam boiler in tannery production processing