fire tube d type boiler for drinks
China's energy structure dominated by coal, this structure does not change in the next twenty to thirty years. That is to say, within the next longer period of time, coal will continue to be the backbone of our energy, industrial fire tube d type boiler for drinkss will continue to mainly coal-fired boilers. The question arises: on the one hand is the proportion of coal-fired boilers quietly decline, on the other hand is still coal-based energy structure, how to reconcile these two contradictory how industrial boilers will be out of embarrassment??
Beijing New Energy Automobile Co., Ltd. is China's first to operate independently and gain new energy automobile production qualification of new energy auto companies, mainly engaged in new energy vehicles and key parts and components research and development, production, sales and service business segments, and the layout intelligent manufacturing, energy management, smart travel, Internet +, and other strategic emerging industries. In the new energy automobile manufacturing process, and a series of paint drying processes can not do without the help of hot water fire tube d type boiler for drinks. Due to the company before the device has reached less than the growing production needs, the introduction of the 2017 mid-tail electric company producing heating pressure hot water boiler (CEDR0.7--95 / 70-Ⅱ).
As to brick factories, they usually need steam and hot air in brick curing, drying process. An manager working in a brick factory, contacted with our consumer service online, he wanted to get the price of 10 ton coal fired chain grate fire tube d type boiler for drinks. As he said, the old one in brick factory served for 8 years, and lower efficiency and higher running costs now. Their factory decided to replace it and buy a new one finally. Coal fuel price is cheaper in local, easy to coal resource; thus they still want to use coal fuel as its energy. Our sales contacted with this factory and quote his the price of SZL series coal fired chain grate boiler, capacity 10 ton, pressure 1.25 MPa.
Measures to improve the thermal efficiency of the fire tube d type boiler for drinks plant food which measures to improve the thermal efficiency of the boiler plant foods What? Many food factory in boiler production process, due to the thermal efficiency of the boiler has not improved, or thermal efficiency of the boiler has been in a low stage of words. For productivity improvement and waste of resources but also have a very large loss. So be sure to conduct a detailed understanding of how the method for improving the thermal efficiency of the boiler plant is for food. 1) The flue gas heat recovery techniques to reduce exhaust smoke heat loss of the main factors affecting the exhaust gas temperature is lost. The higher the exhaust gas temperature, exhaust heat loss will be. Now, when most of the new boiler factory is equipped with flue gas heat recovery equipment, such as economizers, half or full condensation condensing flue gas heat recovery device, these measures can effectively reduce the exhaust gas temperature and improve the thermal efficiency of the boiler. 2) reasonable control air-fuel ratio, to optimize combustion and reduce the loss of incomplete combustion when the heat losses and the excess air coefficient is too high, corresponding to the remaining inhaled cold air into the furnace, the remaining part of the cool air which does not participate in the combustion, but vain drained after being heated, the heat loss of exhaust gas is increased; cold air into the furnace as to continue to increase beyond a certain limit, the furnace temperature will drop, will not constitute a complete loss of combustion increases. When the excess air coefficient is too low, because the fuel can not get enough oxygen to completely burn incomplete combustion loss increases configuration. The prolonged severe incomplete combustion, boiler heating surface will result in carbon, influence the efficiency of heat transfer, exhaust loss continues to increase. Thus, the reasonable control of air-fuel ratio, exhaust heat loss q2 try to drop and incomplete combustion loss q3, is to improve the thermal efficiency of the boiler of the other key points.