fully automatic heavy oil steam boiler for industry
If the configuration boiler fuel gas or dual fuel burners, then the boiler is oil or gas boiler. Fuel gas-fired boiler is a more general concept, fuel gas-fired boiler is divided into water boilers, hot water boilers, fully automatic steam boiler for industrys and thermal oil boiler, according to their own use to select a different fuel gas-fired boiler time of purchase.
Industrial boilers will be changing due to the boiler Maximum Achievable Control Technology (MACT) standards that were finalized in December. What will this mean for manufacturers that use steam and utility plants, and what are the ramifications for the boiler industry at large.Oil, Process Gas and Solid fuel burning boilers will be subject to more Environmental Protection Agency (EPA) restrictions that will require retrofitting existing steam plants to make them compliant with the current boiler MACT standards.
Around the city to promote the coal to gas project, the major institutions of the heating system put forward higher requirements. Central Conservatory of Music is available to students and teachers clean, safe, comfortable, energy-efficient heating environment, protect the health of teachers and students, to transform the traditional boiler treatment. Praise fast boiler Willie sharp series obtained in the transformation of low nitrogen boiler major institutions in Beijing, the Central Conservatory of Music in late 2017 with the signing of fast boiler boiler purchase contract, ordered six Willy sharp series V6-99, to for the entire school's heating facilities.
Combustion gas treatment unit and a fault, gas boiler burner ignition misfire rod reasons: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Measures following five: Clear, renewal, adjust the distance, change and switching transformer. Second, gas boiler, but spark ignition rods misfire reasons: 1, the cyclone disc space ventilation is blocked carbon, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Measures are: Clear; first wash, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel); Check tubing and oil filters, insulation equipment ; remove peripheral screw pump, carefully remove the cover inside out oil network, with immersion oil; renewal of the test oil. Third, when the gas boiler and turn the fire a small fire normal, off, or flashing instability reasons: 1, the air volume damper setting fire too. 2, oil fires micro switch valve (damper outermost that group) inappropriate setting (set throttle air flow rate is greater than the fire). 3, oleaginous easy to spray viscosity is too high (heavy). 4, and the nozzle plate spacing cyclone inappropriate. 5, fire nozzle worn or dirty. 6, the preliminary fuel tank temperature is too high, so that the steam not smooth oil pump oil feed. 7, fuel oil boiler water. Action: Test gradually reduced; heating temperature; adjusting the distance (between 0 ~ 10mm); clean or replace; approximately set to about 50 deg.] C; or drain oil change. Fourth, the noise increases gas boiler burner reasons: 1, cut-off valve is closed or the passage into the fuel shortage, an oil filter blockage. 2, the oil inlet temperature is low, the oil viscosity is too high or the temperature is too high the pump inlet. 3, oil pump failure. 4, fan motor bearing damage. 5, dirty fan impeller. Processing methods: ① the oil line check valve is open, if the oil filter is working properly, the filter cleaning pump itself. ② heating oil or reduce the oil temperature. ③ Replace the oil pump. ④ replace motor or bearings. ⑤ cleaning fan wheel.