gas oil fired liquid steam boiler energy efficient
Inter-regional Pingdingshan Coal Industry Group Co., Ltd. by the Pingdingshan Shenma Group and two Chinese top 500 enterprises founded by restructuring, cross-industry, cross-ownership and transnational business of large state-owned energy and chemical group, under the People's Government of Henan Province , is the most complete variety of coking coal, thermal coal production base, has Asia's largest chemical production base in nylon. Carefully selected and comparison, fast boiler Pingmei cooperation with party has chosen to provide a 2 tons of steam electric oil fired liquid steam boiler energy efficient (WDR2.0-1.25-II) by a fast side.
Method for safe operation of oil fired liquid steam boiler energy efficients steam boiler before use, must be checked for damage of the insulating layer, to check the burner is operating correctly, and to check the position of the opening degree of the valve to ensure it is correct. Must be checked for automatic control instruments and equipment safety equipment accessories, equipment, in order to comply with the requirements. Check item prior to ignition of the steam boiler: open valve before oil circulation pump, oil heating valve is opened, adjusted reasonably high level of the tank, the gas pressure is determined before the natural gas burner ignition must be within the range, the power good . Refers to the operation of the steam boiler is refluxed pressure activated device circulating pump, the circulating pump outlet, inlet, outlet, and the system, it is in the normal range. Circulation pump run for 30 minutes. After the stability of the system, the next step. Open the gas tube steam boiler manual valve, button start-up burner, natural gas burner into the furnace, and then the ignition, the flame remains stable, i.e. is in a safe operating condition. In the firing process steam boiler, if you accidentally quenching phenomenon occurs, the device will automatically interlock burner saver appear. It must be promptly cut off the natural gas pipeline to start the furnace purification. Replacement of the residual gas in the furnace and closed. The system load requirements, temperature requirements and thermal oil outlet, the burner can automatically adjust the size of the fire source.
How to choose a oil fired liquid steam boiler energy efficient heat exchanger? Steam boiler heat exchangers are generally divided into two categories, one is a direct contact heat exchanger, and the other is an indirect heat exchanger. Fuel gas boiler is not only fuel but also refers to the gas boiler. Previously no such dual-fuel boiler, burner because either fuel or gas, no dual fuel burners. With the rapid development of the world energy equipment, some European countries begin production and sales of fuel gas burner, dual fuel burner and boiler combination of organic birth of a new breed of boiler - fuel gas-fired boiler. Biomass boiler is a kind of boiler to biomass energy as a boiler fuel called biomass boilers, steam boilers into biomass, biomass hot water boiler, biomass stove, biomass thermal oil heaters, vertical raw biomass boilers, biomass boilers and other horizontal. They are used to recover flue gas heat, to achieve energy saving effect of the separation device. In general, conventional steam boiler can be increased by a simple transformation of energy-saving effects, such as increased waste heat recovery installation, which is energy-efficient steam boilers advantage. To promote energy saving is largely the cause of the country, to create more profits for the company, cost savings. Choose a good heat exchanger is one way to achieve energy efficiency goals. Direct contact heat exchanger is a steam boiler with heat recovery and a high ability to remove pollutants in flue gas, but acidic water quality, not easy to use in hot water heating boiler. The so-called indirect heat exchanger, thermal energy means that we recovered from the condensed-called flue gas. Today, more and more people choose to use the steam boiler, the proportion of the market is also increasing. Such steam boiler flue gas discharged contains a large amount of steam, by condensation and release large amounts of latent heat of vaporization. Coal-fired boiler efficiency is much higher than coal-fired boilers. This boiler has a good effect on the selection of the indirect heat exchanger.
After the gas hot water boiler hot water boiler vaporization emergency 1. Vaporization handler circulating pump stops abnormally pump failure caused by: ① blower stops running immediately. ② immediately open the door, take measures to pressure the fire, lift the chute gate, cutting off the supply of coal grate. ③ In the case of boiler pressure not greater than 0.6MPa (600KPa), the exhaust valve to follow, only a sharp rise in pressure in the boiler deflated, used only relief exceeds 0.9MPa, and the exhaust process to be carried out slowly, prevention boiler due to loss of pressure and more violently again vaporized. ④ close the boiler water, water main gas valve. ⑤ open stop valve recirculation line, to ensure that the water supply pipe velocity convection heating surface (economizer) to prevent re-vaporization of the economizer. ⑥ The operation of the above operation, at the same time to pay the boiler to reduce the boiler water temperature and the furnace pressure. ⑦ After the boiler pressure is normal, i.e., opening the standby circulating pump, into the normal combustion. 2. Treatment failure or sudden loss of power boiler vaporization of power: ① immediately open the door, lift the coal chute slide gate to take pressure fire measures to reduce the oven temperature. ② Grate with the fastest speed in order in the shortest time to fire onto the slag tap. ③ the degree of treatment in the first case. Once a short time can not supply heating network system, antifreeze should take emergency measures. 3. Due to excessive heat boiler boiler vaporization process: ① the immediate closure of the drum, induced draft fan. ② immediately open the door, take measures to pressure the fire, lift the supply of coal chute slide gate, off of coal, while the grate into fast gear. ③ In the case confirmed the presence of water, the boiler can supply water to the boiler body, boiler out of the water while closing the main valve. ④ Open line stop valve recirculation pump to ensure water velocity convection heating surface of the pipe, to prevent the economizer again vaporized. ⑤ Open circulating pump with jog mode, jog each time less than 30 seconds, again less than one minute jog interval. Jog purpose is to reduce the boiler water temperature, while preventing a large amount of steam into the pipeline system. ⑥ back into place after the safety valve, circulating pump running, and then the normal burning stove. 4. Water boiler system run vaporization process due to water loss, loss of pressure caused by: ① immediately closed drum, induced draft fan. ② out of the water while closing the main valve and the boiler circulating pump. ③ take the same measures to cool the furnace tube described above. ④ Open stop valve recirculation line. ⑤ rely exhaust valve until the safety valve back into place. ⑥ until the boiler water temperature drops below 50 ℃, when the temperature of the furnace temperature less number 200 ℃, again within the boiler feed water, water course to be carried out slowly, to prevent harm to the boiler when the temperature is too large. ⑦ After processing leakage fault, the system time to the replenishment, and out of the water boiler always open the valve, and the circulating pump, and then normal combustion.