gas technology tubeless vertical boilers can be solution
Fangkuai Group has more than 60 independent intellectual property rights, advanced clean fuel technology tubeless vertical boilers can be solution manufacturing technology, and jointly established a clean fuel boiler production, research and research cooperation base with Tsinghua University and Xi'an Jiaotong University. An enterprise with a R & D and test center for clean fuel boilers. The thermal efficiency of “Fangkuai” boilers can reach 107%, which has been included in the national special equipment energy-saving catalog. The company developed ultra-low nitrogen full premixed combustion condensing boilers and ultra low nitrogen emission fuel gas boilers, which are developed by the company using Ultran condensation technology.
Some of the causes direct impact on the thermal efficiency of horizontal steam technology tubeless vertical boilers can be solution of the country are carrying out a blaze of glory roaring coal to natural gas operations, the choice of horizontal steam boiler, greatly reducing the fine dust contaminated with dust, along with toxic gases such as nitrogen oxides emissions It has also been suppressed. Thermal efficiency is a key measure of horizontal steam boiler, a good start and that is that let you look at some of the causes direct impact on the thermal efficiency of horizontal steam boiler. Through research departments, the heat loss of horizontal steam boiler is very important from two aspects: the combustion air-fuel ratio is not satisfactory and Smoke and heat loss. Smoke and heat loss reduction should be modified in the tail horizontal steam boiler soot waste heat recycling install, or choose would be more leading series condensing boilers. Combustion air-fuel ratio over the substandard Analysis: common horizontal ejector-type steam boiler burner choice, without the formation of air-fuel ratio can be flexibly adjusted. Most of the horizontal steam boiler selected non-automatic strong emission burner, leading to the root causes of unsatisfactory air-fuel ratio has the following areas: air-fuel ratio is not ideal is more important is divided into two kinds of probability: When an excess of oxygen, there will be endless excessive cold air is heat conduction, resulting in increased energy consumption horizontal steam boilers, hot horizontal steam boiler efficiency decreased; when oxygen is not standard, incomplete combustion occurs, generating heat horizontal steam boiler efficiency decreased.
How to maintain the technology tubeless vertical boilers can be solution shutdown? After boiler shutdown cooling, heating surface must be thoroughly cleaned of fouling and ash grate the upper, the lower portion of the furnace. Then to maintain a certain degree of natural ventilation flue. In general, in order desiccant moisture should be placed in the furnace, flue. The quicklime as a drying agent, within the furnace or flue gas per cubic meter should be placed generally about 3kg. After placing all the ventilation should be tightly closed doors. After the change of lime powder to be replaced. Low-lying position as boiler room, ground during shutdown severe flood tide, often approach should be used and placed a small fire to dry desiccant combination. How to care? If the boiler shutdown a long time, the boiler shutdown after complete removal of soot coated with an anti-corrosion red lead paint in oil or other metal surface furnace. As internal corrosion Maintenance shutdown of the boiler body, under normal circumstances, can be used wet shutdown maintenance is not more than one month, one month electrically operated steam boiler should be taken to dry more maintenance. To note the following problems when a dry maintenance: desiccant boiler not in direct contact with the metal surface, may be mounted in a container such as the iron plate after the desiccant is placed, and a hole for shutting the other hand hole cover.
A number of factors cause the pressure of the heat efficiency of the technology tubeless vertical boilers can be solution module are carrying substantially all parts of the coal gas impressive work, use a large extent, avoided the module boiler fouling contamination, while discharging hazardous gas like nitrogen oxides obtained a clamp. Thermal efficiency is an important measure of the rule module boiler, let us study the cause of a number of factors under the pressure of the thermal efficiency of the boiler module. After inquire about the personnel, boiler heat loss module is mainly produced in the bear on these two: the proportion of full combustion air with smoke emission unreasonable heat loss. Reduce smoke emission install heat loss can be recovered in the flue gas waste heat boiler module terminal fitting, or use more advanced features of FGR boiler. The combustion air fully proportional unreasonable non-compliant analysis: General ejector module boiler burner, causing the air-fuel ratio is no way to maneuver to mobilize. Part of the boiler module using a mechanical blower burner, resulting in unreasonable cause fuel ratio factors are the following: the main air-fuel ratio unreasonable encompass divided into two cases: when oxygen is excessive, the excess will be numerous cold is heated, resulting in increased cost of energy boiler module, the thermal efficiency of the boiler module lowered; when oxygen is non-compliance, will produce incomplete combustion occurs module boiler heat efficiency is lowered.