heavy oil fired hot water boiler prices in ireland
An oil boiler or oil fired boiler is an appliance that uses oil to heat up water. Boilers are essentially closed containers that heat water that is distributed throughout a building or complex for various purposes. When you are considering the purchase of a boiler, one of the most important choices to make is with regards to the fuel. Oil boilers and electric boilers are sought after for several different reasons, and some of their major differences, pros and cons of each are outlined below.
April 15 --16 days, ASME joint review by the American Society of Mechanical Engineers group assignment, our company ASME quality control system and demonstrate products on-site audit. After a strict and rigorous audit, the joint review team leader (AIS) announced: "fast Boiler Co., Ltd.-site audit by ASME recommendation issued: power boilers (S) and pressure vessel (U) Certification and Seal"
With this knowledge points, easily handle common fault boiler pump gas boiler pump is an important equipment, mainly for replenishment aspects boiler. Once the water pump fails, will first trigger replenishment system abnormalities, then water level gauge, pressure gauge, valve instrument will throughout the spate of error, and thus lead to serious boiler accidents. We have compiled the boiler pump five common faults; mastered them, to help you easily cope with pump failure. A lack of flow causes: Effect of multiple pump flow is insufficient suction pipe leakage, valve leakage bottom; inlet plug; insufficient depth of the bottom valve into the water; the water pump speed is too low; sealing ring or excessive wear of the impeller; and other highly absorbent excessive . Solution: Check the suction pipe with the bottom valve, blocking the leakage source; clean mud inlet at the outlet or plug; end of the valve must be greater than the depth of the water inlet pipe 1.5 times the diameter, to increase the depth of the bottom valve into water; check the power supply voltage, increase pump speed, replace the seal ring or impeller; reduce the installation position of the pump, or the replacement of the high lift pump. Second, causes excessive power consumption: pump speed is too high; the pump shaft bending or misalignment of the spindle motor or pump shaft and not parallel; inappropriate selection of the pump head; pump suction sediment or obstructions; motor ball bearing damage. Processing Method: check circuit voltage, reducing the pump speed; correct or adjust the relative position of the pump shaft and the pump motor; with a suitable pump head; or clean sediment blockage; three ball bearings replace the motor, pump noise or rattling Cause: pump installation is not strong or high pump installation; motor ball bearing damage; pump shaft and the motor shaft bending or misalignment, and the like are not parallel. Approach: install stable pumps or pump with reduced height; replace motor ball; correction bent pump shaft or adjust the relative position of the pump and motor. Fourth, the motor shaft, or bearing overheating causes: lack of lubrication or bearing rupture. Approach: filling oil or replacement. V. No water causes: pump and suction tube not filled with water; level below the pump filter tube; suction tube rupture. Processing Method: negative end of valve failure, filled with water; reduce the installation position of the pump, so that water drainage pipe under the action, or the like movable liter water filter and then pumping water; the suction pipe repair or replacement
Matters needing attention in loading and installation of Gas-fired Steam Boiler
Gas-fired steam boilers are a very wide range of special equipment, usually built in boiler rooms. However, in the process of loading and installation, some problems must be paid attention to, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.