heavy oil fired steam boiler coal fired thermal oil
Fangkuai Group adopts the concept of “moulding character and creating high-quality products”, and continues to research and continuously improve the technological content of products to get closer to users. With the mission of “creating convenient and fast boiler high-quality products for users”, it uses remote monitoring, APP, and active return visits. And other channels to provide users with convenient and efficient services; with the core values of "professionalism, lean work" as the core value, established an effective enterprise management system, adopted ISO9001 quality management system, OHSA18001 occupational health and safety management system and ISO14001 environmental management System certification; and cultivated a large number of high-quality employees with norms of behavior, professionalism, and continuous commitment to provide customers with more convenient and efficient services.
Check Item item hot water boiler hot water boiler comprising a boiler inspection and checking internal use preparations, checking in the furnace and the flue, the boiler attachment check, check automatic control system, the secondary device, check the combustion device, the auxiliary heat check the surface of the hot water boiler must be done before running some tests, these tests are quite a lot of us, it is possible because of our neglect and causing very serious consequences. Therefore, we must forestall, be sure to carefully check the following before the hot water boiler operation. 1, including the use of internal inspection and boiler ready. 2, inspection, and furnace fouling and debris inside the flue in the furnace and flue should be cleaned. Flue duct and damper, the shutter must be complete and compact, flexible switch, opening and closing accurately indicated. 3, check the boiler accessories, check the safety accessory is intact; cock is rotating flexible, easy to use; all kinds of instruments and controls should be complete, good, clean. After passing the examination, should the gauge cocks in working condition. 4, check the automatic control system. 5. Check the accessory device. 6, inspection of the combustion apparatus, the combustion apparatus is intact inspection; mechanical transmission system, coal handling system, the ballast system test switch normally; spring-loaded safety level of a gearbox should be appropriate, well lubricated; coal shutter indicate the correct scale. iron eagle neat, well, turn the ballast plates full, flexible movement. 7, the auxiliary heating surface of the inspection, check the auxiliary device (fan, blower, pump, etc.) are firmly connected coupling; proper belt tension triangle; oil should be good enough; cooling water flow. After passing the examination, installed security guard, respectively, commissioning, and note the current when idling. It is fed out of the hot water boiler heat equivalent to a mass per hour (usually expressed in tons) in water was heated from 20 ℃ and heat output of all vaporized into a fired steam boiler coal fired thermal oil water absorbed three expressions, in tons) water from 20 ℃ heated and vaporized into all heat absorbed by the steam boiler it is fed out of the hot water heat equivalent to a mass per hour (i.e. typically kcal / hr (kcal / h), tonnes / hour (t / h ), megawatt (MW). (1) kcal / h is in metric units of expression, which represents the heat of hot water boiler fed out per hour. (2) t t borrowed steamed steam boiler popular argument, ( 3) megawatts (MW) is the international system of units unit of power, the basic unit is W (1MW = 106W). this expression formal documents should be used.
Boiler boiler should be classified according to which of several energy conversion device is a way, the energy input to the boiler chemical energy, electrical energy, a boiler with a steam output of the fuel in the constant heat, high temperature water or organic heat carrier. Many types of boilers, we like how to categorize them? Here Jinhe company you explain one by one! Many classification of the boiler, the boiler can be divided according to use, can be divided according to the structure, the type of fuel boilers, but also you can press the water cycle in the form of pressure classification. It can be used as boiler thermal power boilers and heating boilers. Power boiler comprising a power station boilers, marine boilers and boiler locomotive, corresponding to power generation, marine, and locomotive power dynamic. Heating boiler comprising a fired steam boiler coal fired thermal oils, hot water boilers, hot tube boiler, stove and the heating medium heating furnace, to give a corresponding steam, hot water. Hot air and the heating medium and the like. Boiler by the structure, divided into fire tube boiler and water tube boilers. Fire-tube boiler, including vertical and horizontal boiler boiler, water tube boilers and water tube boilers including horizontal, vertical, water tube boilers. By species classified as boiler fuel gas-fired boiler, oil-fired boiler and upgrade technical gas boiler and gas boiler, furnace oil and gas alternative --- pulverized coal boilers, gas boilers and other dual-use. Combustion gas boiler can be divided into layers by firing boiler, in fluidized bed boilers and combustion chambers. The latest fuel alcohol-based fuel boiler, he will greatly reduce the pollution of the atmosphere of a gas boiler. Evaporation of less than 20t / h is called a small boiler, evaporation to 75t / h is referred to as large boilers, evaporation of medium-boiler referred interposed therebetween.
What part of the body including the boiler? What role have? It comprises a crucible and the furnace: a body: refers to a soda boiler system, which is superheated by the reheater water preheating system and a vaporization system composed of dry steam. The role of the high-pressure boiler feedwater heater through the further heating evaporation, for the purpose of blowing rpm turbine to do work. System configuration: economizer, the drum, the downcomer, water wall, superheater, reheater, economizer high pressure heater outlet feedwater is introduced into the economizer, economizer tube within an outer absorber tube gas and fly ash heat, water temperature increases to about 300 ℃ drum water out from the economizer line into the bubble along the top of the boiler disposed outside. Drum lower half of the water, the upper half steam. Unsaturated high pressure drop along the water reaches the bottom of the bubble tube at the bottom of the lower header outside the boiler, a number of pipes mounted in parallel on the bottom of the boiler around the lower header, the furnace by the upward flow of the absorbent in the central flame of the inner tube wall pipe convective heat radiation heat transfer and high temperature flue gas. Since the heat absorption is much less than the water vapor, the water wall within a predetermined vaporization rate can not be greater than 40%, because the working fluid will easily melt late Wall water absorbing tube rupture occurred. Downcomer role is water vapor to the bag waterwall lower header, to establish a water circulation. Wall water in the tank through the second line and then returned to the boiler water wall, the water in the drum is completed, the downcomer, the circulation between the superheater waterwall separated in the steam drum is withdrawn from the top of the drum, laying into the first top ceiling superheater, then through the cladding wall superheater, low temperature superheater, platen superheater, to a high temperature superheater, after reaching the rated temperature of the heating steam turbine into work. After the reheater boiler is also provided with a large reheat means that steam from the high pressure cylinder acting, temperature and pressure of the exhaust gas is reduced, the exhaust gas is heated to a reheater, and then returned to the steam turbine, a low pressure cylinder continues to work. Furnace body: it refers to a boiler furnace combustion system and its role is to heat the fuel combustion in the furnace as much as possible and transfer heat to the working fluid, and the completion of the water wall and economizer water water heated in the tubes, heated in the dry steam superheater and reheater tubes, the air in the air preheater tube heated. The system consists of: a combustor, furnace, air preheater. Production process: raw coal from the coal by the belt conveyor to the higher field position of the coal bin, the bottom of the coal from the coal bin out through the stoker evenly into the ground to a coal mill. Nature of the atmosphere via the air inlet of the blower is arranged in the vertical flue to the boiler air preheater, subjected to heat of the flue gas, flue gas waste heat recovery. About 250 degrees out of hot air into two air preheater from: one directly introduced into the burners of the boiler as secondary combustion air into the furnace; the other can be introduced into the mill inlet for drying, transporting coal, which said primary air portion of hot air. Excellent flow of drying gas and pulverized coal mixture powder consisting of primary air, conveyed via line separator to be coarse coarse separator, the separated coarse powder inlet sending back regrind mill, and eligible powder and primary air mixture into pulverized powder separator, gas separation, the separated coal fines into storage to save it from the powder according to the magnitude of the thermal load of the boiler, the control of coal flow discharged coal warehouse bottom while separated from the fines separator as the primary air pulverized coal power delivery, after the pressing of mill powder mixture with the gas mixture into a fine powder fed again by a burner into the combustion furnace.