heavy oil steam boiler industrial boiler
Our jewelry processing company in the automotive production, many processes require energy, to be honest we really a headache on the choice of the boiler, thanks met specializes in the research and production of fast square boiler boiler! The purchase of two Taipower hot water boiler, tangible help us save a lot of costs. --customer feedback
What problems should be paid attention to in maintenance Electric normal pressure Boiler
Nowadays, advanced electric atmospheric pressure boilers need to be used in industrial production as well as in daily life. However, the electric atmospheric pressure boiler is a highly operational mechatronics equipment, such as customer inspection, maintenance is not timely will result in equipment line aging, equipment oil circuit and oil pump wear and so on. Therefore, users need to pay attention to the maintenance of equipment when running boilers, then, what problems should users pay attention to in the maintenance of electric pressure boilers with good performance?
1, pay attention to stop furnace detection electric atmospheric pressure boiler in the maintenance, users should let the equipment according to the normal shutdown procedure operation to achieve slow cooling, at the same time, Users should use pot water circulation and furnace ventilation to gradually reduce the temperature in the pot and furnace. It is worth noting that when opening the door hole of the equipment, users need to pay attention to preventing the burning of steam, hot water and flue gas in the boiler.
2, note that when users maintain the insulation, the combustor and flue of the detected atmospheric pressure boiler should be separated from the total flue or the other running boiler flue. The test results are as follows: (1) the combustor and flue of the tested atmospheric pressure boiler should be separated from the main flue or other running boiler. And the flue gate should be closed tightly, and in the partition after ventilation. In addition, the blind plate used in equipment partition should have sufficient strength and hardness to avoid being bulged by high pressure medium in the operation of electric normal pressure boiler, and the partition position should be clearly indicated to avoid confusion.
3, note that the user must completely cut off the connection pipe between the vessel and the gas equipment, especially to the combustible and toxic medium equipment before the inspection of the atmospheric pressure vessel is carried out by the user of the equipment container. In addition, the equipment container not only needs to close the equipment valve, but also needs to use the blind plate of the equipment to close the valve so as to prevent the gas leakage into the container and cause the fire explosion or poisoning accident of the valve so as to cause the combustible or toxic gas to leak into the container.
Steam boiler steam separator device works in the overall design of the steam boiler industrial boiler, steam separator device is essential, rapid separation of water saturated steam is to improve the steam quality to ensure that an important part of the normal operation of the boiler. Fuel gas boiler is not only fuel but also refers to the gas boiler. Previously no such dual-fuel boiler, burner because either fuel or gas, no dual fuel burners. With the rapid development of the world energy equipment, some European countries begin production and sales of fuel gas burner, dual fuel burner and boiler combination of organic birth of a new breed of boiler - fuel gas-fired boiler. Biomass boiler is a kind of boiler to biomass energy as a boiler fuel called biomass boilers, steam boilers into biomass, biomass hot water boiler, biomass stove, biomass thermal oil heaters, vertical raw biomass boilers, biomass boilers and other horizontal. Convenient to meet customer needs. Then, the authors will guide you to understand the working principles of steam and water separation device on the steam boiler. First, to avoid increasing the local load between the evaporation surface and the vapor space drum boiler, the steam is uniformly by water extraction. Second, it can effectively weaken the kinetic energy soda mixture into the tank, reducing its impact on the water. Third, in order to take advantage of inertia, and centrifugal separation, the mixture having a flow path soda rapidly changing, keeping in mind the shunt separation of water, to avoid being carried steam again. Finally, there is a large surface area, in order to adhere more water droplets. At the moment, a lot of steam separator type, according to the principle of the separation can be divided into natural and mechanical separation. The principle is to use natural separation of steam and water and the density difference between the force of gravity. Mechanical separation principle relies on inertial force, centrifugal force and adhesion. Water separation apparatus is often installed in a steam boiler and used underwater plate, baffle, plate uniformity, manifold, volute separator, corrugated sheet and steel mesh separators.
Note Di steam boiler industrial boiler steam boiler operational considerations should use great caution when using, because the slightest error will bring harm, so the operation should be more cautious, for a description of the use of steam boilers, process clear operation should pay attention It matters. Biomass boiler is a kind of boiler to biomass energy as a boiler fuel called biomass boilers, steam boilers into biomass, biomass hot water boiler, biomass stove, biomass thermal oil heaters, vertical raw biomass boilers, biomass boilers and other horizontal. Steam boiler is an energy conversion device, the energy input to the boiler fuel chemical energy, electrical energy, thermal energy and other forms of high temperature flue gas, and after converting the boiler, the steam output having a certain outside thermal energy, high-temperature hot water or an organic carrier. According to many years of experience in the use of steam boilers, summarizes the operating steam boiler matters should be noted: First, before the boiler to be familiar with the use of manual, to protect the normal use of safety equipment and operating personnel fundamentally. Before starting, check the power supply voltage is operating properly and water, close the drain valve to open the water supply valve, the pump checks whether the jam, remove the blade cover, and the motor shaft to the flexible state to start the scroll machine. Check the boiler or the power off when changing accessories to avoid the risk caused by the charging operation. Secondly, the electronic control box, pumps, motors and other components should be avoided in order to prevent moisture absorption burning boiler should pay attention to maintaining clean, according to the relevant boiler water quality requirements, be sure to install a water softener use, because they do not use a water softener can cause boiler fouling, serious it can cause burst pipes, shortening the life of the boiler. Finally, if the above conditions are not covered by the warranty, if not used in accordance with the provisions of water treatment equipment, sewage note that when used. Emissions once a day, with pressure 0.1MPa-0.15MPa emissions to prevent clogging pipes, sewage pipes should be connected properly to prevent burns, the safety valve should be flexible maintenance plans, pull the lever at least once a month safety valve to check its take-off and elastic seat. Local Technical Supervision safety valve should be checked once a year.