high-efficiency hot water biomass boiler
How to deal with water shortage in electric steam high-efficiency hot water biomass boiler machine in use for some time this or that problem will be serious delays in the progress of work, causing great inconvenience to the people, such as water shortage, this problem arises in the use of electric steam boilers after a period of water shortage in how people deal with how to solve it. Electric steam boiler how to deal with water shortages: water level proofread each water level indicated by the right to judge whether the electric steam boiler water. In the electric boiler can not be determined when full of water or water vapor, can turn on the water faucet open water level, water flows out of the pot if not, indicating that water scarcity is an accident, otherwise it is full of water accidents. For the embodiment allows a small electric steam boiler waters operation, water may be called first, determines the electric steam boiler is mild or severe water shortage. This only applies to the water level gauge water hole communicating tube heating surface is higher than the highest water capacity and fire community large electric steam boiler. Otherwise it can not be called electric steam boiler water, because it will delay the time of the incident electric steam boiler water treatment, the worsening of the situation. When a slight electric steam boiler water, should reduce the fuel and air, the combustion decreased, and electric steam boiler feed water slowly to the normal level. Typically by adjusting a valve opening degree and the size, to control water flow rate and water, being careful not excess water. To quickly identify the cause of water shortage in the water and remove the process, and then check the electric steam boilers there is no unusual circumstances, after confirmation by the normal operation can resume electric steam boilers. When electric steam boilers severe water shortages, the need for emergency fire fighting shutdown. The fire shutdown procedures according to the method of implementation of the emergency shutdown, is strictly prohibited water to the pot and when serious water shortages. Some fireman personnel after the discovery of electric steam boiler water shortages, interrupted several times with water, each time a small amount of water replenishment way to cover up the accident electric steam boilers. This practice is very dangerous. If electric steam boilers are also less severe water shortage will cause biomass boiler leaks. If electric steam boiler water can cause serious electric steam boiler explosion. Only natural ventilation and cooling in electric steam boiler pot temperature dropped to below 70 ℃, water only slowly. Electric steam boiler for the water to normal level after thorough examination, no abnormal situation in order to re-start ignition, electric steam boilers to resume operation. Traditional old-fashioned coal-fired boiler using coal, gas, fuel oil and other fuel, these fuels are non-reusable primary energy, the future price will be higher. And the shortcomings of the traditional old-fashioned coal-fired heating methods are also caused by incomplete combustion, incomplete combustion can cause a lot of heat from the flue gas discharge out together, so it will cause energy losses. Boiler not only save electricity, but also saves time and effort, not the traditional coal-fired boiler heating boiler released by carbon dioxide, toxic gases, dust and other harmful substances, so users do not need to clean up, so it can save a large sum of maintenance cost.
In the low profit era of Chinese paper packaging industry, entrepreneurs have been turning their attention to internal management, increase business efficiency by saving energy. At present, the paper packaging industry equipment many of them appear old and comes with a variety of issues, in particular energy use seriously inadequate problem is solved and bear the brunt of reform issues. So we must make an effort in the use of energy, use energy-saving equipment for the industry, in order to solve the problem fundamentally.
How to deal with the failure of the gas burner high-efficiency hot water biomass boiler? How to deal with the failure of the gas burner boiler? Gas boiler with a combustion burner manner generally ejection liquid and gas, so that stable fuel injection, ignition a necessary condition. Biomass boiler categories: biomass boilers Horizontal, vertical biomass boilers. Biomass gas thermal oil heaters, biomass steam boiler, biomass hot water boiler, biomass oil furnace. Boiler summarizes the four points of failure. Cause of these problems is different, not as ignition rods ignition, spark ignition rods single ignition, fuel injection increased strength unstable flicker noise large burners. The reason for these problems is different, the boiler needs to pay a lot of effort to collect them. First, the reasons many ignition misfire rod, such as clogging of the seam, moisture, leakage, ignition rods of different gap distances, skin damage, short circuit, all these reasons and due to improper operation caused by unscheduled maintenance. Troubleshooting not very difficult, can solve the cleaning, changeover, the ignition rod spacing problems.
CFB high-efficiency hot water biomass boiler can be divided into coal fired boiler and biomass fired boiler according the cumbustion fuel.ZG can design and supply CFB steam boiler,CFB hot water boiler and CFB power plant boiler.The capacity of CFB steam boiler is 10-280ton,CFB hot water boiler is 20-160ton,CFB power plant boiler is 10-50MW.All these three types boiler play a vital role in industry.