high pressure water tube steam boiler
Structural Advantage of WNS Hot Water Boiler
1.Reasonable design: horizontal internal combustion three return all wet back design,100% corrugated furnace, with good heat flexibility. The water covers fire overall design, sufficient heating area, make sure the boilers high efficiently operated.
2.Fully automatic operation: Users simply start the button, boilers can run on the setted program. The load of water saving, water supply, etc. are fully automatic operation, no need for guard in position.
Stanley Agricultural Group Co., Ltd. is specialized in the production and sale of fertilizer and other agricultural technology promotion of integrated services provider, has total assets of 6.3 billion yuan, more than 8,000 employees, annual production capacity of 5.2 million tons. Earlier this year, fast Boiler stand out in many boiler brand competition, and Stanley reached a cooperation, to provide a whole 10 tons of steam condensing high pressure water tube steam boiler (WNS10-1.25-Y.Q), provide support for the heat Stanley fertilizer plant.
Will be different effect of dust, equipment for health is unstable or volatile dust removal systems, pressure boiler design in the use of flue gas treatment needs to pay attention to the amount of change on different types of Baotou pressure boiler precipitator making use affect the collection efficiency during normal operation, the level of efficiency of the bag is a bag filter, ESP and venturi scrubbers and other equipment. In selecting effective precipitator according to the nature of the selected gas, must be considered when using the gas flow rate, temperature, composition and humidity and other factors, the electrostatic precipitator is adapted to the amount of wind, temperature
How full boiler water treatment? 1, the boiler is full of water refers to: (1) the water level is not visible or not, a high level alarm; (2) steam temperature decreases, main steam isolation valves and the turbine inlet valves visible white steam; (3) turbine or steam pipe occurs water hammer; (4) water flow is not larger than the normal steam flow. 2, causes: (1) water supply is automatically jump manually, resulting in abnormal increase of water supply; (2) safety valve on the drum or steam header, resulting in up water or with water; 3) evaporation boiler more overload occurred priming. 3, processing method: a boiler steam pressure and when a normal pressure, the drum water level rises, exceeds + 50mm, the following measures should be taken: (1) the flushing drum were compared with two level table to check instructions are correct. (2) from the automatic to manual adjustment of water supply, water supply and close the door manually turned down and to reduce the total water supply amount adjusting gate. If after treatment b above, within the drum water level is still rising, exceeds + 75mm, should be carried out the following measures: (1) to open the door for emergency drain drum should be put to the normal water level water level shut down immediately. (2) The steam temperature, the heated reducing or closing off the small door, door open and main steam superheater tubes hydrophobic hydrophobic gate. When the treated drum water level continues to rise, and exceeded the upper drum water level meter water level visible, on emergency shutdown, as soon as possible with the main pipe splitting, immediately stop the water, recycled to open doors, turn on the water to strengthen the boiler and steam drum note an upper level of the water table appears to be put to the normal water level off. Standby furnace often the case, the value of the long obtaining consent, according to Stoke furnace operation. C If the drum can not see when the water level within the water table, not in time, should take the following measures: (1) were compared with two wash drum water level table, check the instructions are correct. Full drum water level tables turn on the water door, turn on the water and then slowly close its doors, as there is water in the water table appears, and water levels continue to rise full of tables full of water and has not been proven boiler water level gauge steam over the side of the tube, press the emergency shutdown process. (2) open the door turn on the water table level, and slow to close its doors after the turn on the water, the water level in the water table invisible. To prove a serious full of water, soda and then close the door, turn on the water to open the door, the water level of the water table memory after the release to do, turn on the water shut the door immediately. Ajar quickly and valve inner water table level occurs, and filled with water, before this time has exceeded the determination level of the steam drum level side through the tube sheet, emergency shutdown should be treated as soon as possible and the manifold splitting. (3) When the water level in the boiler accident occurs, it is difficult to judge if the water level should be shutdown immediately. After the shutdown called by the water method called water, check the water level in the drum.