horizontal multitubular two drum boiler is not working
Prevention of industrial horizontal multitubular two drum boiler is not workings produce condensate hazardous industrial boilers which produce condensed water hazard control measures which 1, bold and hydrophobic visible drainage pipe in the boiler inspection process and found that the condensate is not easy to accumulate in the water-tube boiler, while the horizontal boiler shell boiler drain more, but part of the boiler there is still a large amount of condensate (most of which are newly installed and running). The analysis revealed that, due to the large side of the boiler combustion space, even drainage arrangement, large diameter, tube bundle boiler convective condensation water formed can be discharged. Small smoke tube boiler combustion space levels, due to the structure until the drain can only be arranged at the bottom tube sheet boiler and after the drain of less than 30 mm in diameter, and designed to prevent leakage of boiler flue gas, directly connected to the drain pipe drainage pipes. In operation, the contents of the boiler easy to plug welding slag, rust particles. 2, to adjust the position of the economizer due to the large volume of the boiler, economizer boiler mostly installed in a horizontal tail position, while some horizontal boiler economizer housing is mounted directly or obliquely above the boiler flue outlet, the boiler the lowest point of the flue gas flow. Although the drain pipe installed at the bottom of the economizer, but due to gravity, most of the condenser, condenser and condenser will be returned to the boiler flue. During operation, condensed water after a long period of rinsing, immersed in a heating boiler section. Due to the different materials and material economizer boiler, economizer 09CrCuSb, designed using a material having a strong corrosion resistance, and without considering the design of boiler condensate corrosion conditions, 20g materials, poor corrosion resistance, easily corroded. 3, appropriately increasing the return water temperature in the boiler load or the energy efficiency of the testing process in industrial boilers, most of the boiler has a low load operation. Operated at the design load, the exhaust gas temperature before entering the boiler flue gas economizer is higher than the dew point, in the low load operation, the exhaust gas temperature of the boiler flue gas is lower than the dew point, so in the case of satisfying the condition, as far as possible should be boiler work in the vicinity of the design load, or take action. Measures could be taken to improve the return water temperature of the hot water boiler. For example, in the secondary heating system network, a network should decrease the flow, to increase the temperature of the primary water supply and return pipe network. Thereby raising the temperature of the flue gas leaving the boiler heating surface of the body, to avoid condensation of water vapor in the heating surface of the boiler body. 4, the depth of the condensed water recovered by previously described, the industrial gas boiler condensate is quite large, which is part of the condensed water is not effectively contain some depth using heat, in order to take effective measures to recover heat and water. For example, we may be adjusted by adding an alkaline agent (ammonia, cyclohexane, etc.) pH value of the condensate, which is then pumped into the heating system, which not only saves water, and heat is recovered.
School education is the foundation for development of our country, to provide environmental and healthy living environment for students is our top priority school. Winter is fast approaching, fast horizontal multitubular two drum boiler is not working heating and for us to solve the problem of the coexistence of environmental protection, give us tremendous help provide heating in winter. --customer feedback
Constantly advancing ZG horizontal multitubular two drum boiler is not working
In such an ever-changing era, it is an opportunity and a challenge for enterprises. Many of the former big companies were left ruthlessly by time because they could not keep up with the times. ZG boiler has been in existence for more than 70 years and is moving towards becoming a century-old company that is most trusted by customers in the boiler industry. In the past 70 years, ZG boiler has been advancing more and more, and it has become increasingly powerful under the polishing of time.
Pressure hot water horizontal multitubular two drum boiler is not working What does it mean? Pressure hot water boiler is no mention here of a boiler or pressure micro pressure. Henan fast boiler producing hot water boiler pressure of 1 kg, it is not part of the special equipment, the design of this hot water boiler in our mind is to facilitate more people to use. For large-scale industry, it must be used with pressure boiler operation, then the question is, after you purchase the boiler is not required to be reported to the relevant departments to do, and then have to undergo annual boiler inspection, if it is for small or civilian enterprises used, each year these related procedures up enough of a headache. So we designed the boiler pressure is very small, so you need a high-pressure job production line is not suitable for use. Let Henan fast boiler Xiao Bian introduce our boiler compared to other boilers on the market What are the advantages of it? 1. Let me talk about our high-quality stainless steel boiler body, are used, this material from an aesthetic point of view , nice, the main advantage is corrosion resistant, not rust, since this will naturally extend the life of the boiler. Intermediate packing a thick layer of cotton insulation, so some customers fired boiler when the water temperature have reached 100 degrees, touched her hand furnace or cold, indicating that all of our boilers and thermal insulation properties very good. 2. Next said its core portion of the burner. Type burner hob burners is our joint research and development with the Xi'an Jiaotong University, this burner than the imported burners is mainly to ensure environmental protection and efficiency at the same time, lower input costs, and thus to allow customers to get real affordable. This burner instruction issued by the intelligent controller is installed on the boiler, it will automatically electronic ignition, a state of cold five minutes to let the water heat up the furnace, showing that we have developed burner is good. 3. Say you're a high-tech aspects. That is automatic intelligent system, and now the technology developed, we have got used to the use of smart products, such benefits can not only save labor, work all the time can also detect the device, which the boiler is equipped with this intelligent control system allows the entire boiler fully automated real work in this regard is indeed to you left a lot of unnecessary expenses. 4. With regard to thermal efficiency, this could be a problem many customers are concerned about. Because we furnace design is the water fire burning structure, when the gas into the combustion due to the induced draft fan working the upper end, pulling fuel combustion, allow the boiler to provide heat as soon as possible, our boiler thermal efficiency is more than 93% of.