horizontal oil fired hot water boiler best prices
A heated boiler is called a boiler. Heat transfer oil, also known as organic heat carrier or heat medium oil, has been used as intermediate heat transfer medium in industrial heat transfer for more than 50 years. Based on the idea of forced cycle design, a once-through boiler is developed. Generally, coal, oil and steam are used as fuel, heat conduction oil is used as the medium, hot oil circulation pump is used to force the medium into liquid phase circulation, heat energy is transmitted to the heating equipment and then returned to the heating furnace for re-heating. High operating temperature at low pressure, and high precision control for medium operation. The heat utilization rate of the system is high, and the transportation and maintenance are convenient. The closed circulation heat supply is connected with the atmosphere, can extend the service life of the boiler, liquid phase or gas phase transportation heating. The boiler adopts three-way coil design, the system sets the expansion water tank, and realizes low-pressure and high-temperature heating. The coil structure is adopted, the heating surface is sufficient, and the expansion is fully absorbed. Imported low-NOX combustion machine, combustion charge, belongs to environmental protection products. Boiler can choose advanced touch screen computer controller and digital computer controller automatic control system. With automatic temperature regulation, automatic ignition, and differential pressure, overtemperature, quenching protection. Boiler manufacturing standards, strictly in accordance with the relevant national standards. Pot The use of furnace water quality requirements: some users believe that as long as the boiler to maintain water can be, the water quality is not a choice. In fact, the quality of water on the boiler or have an impact, the editor recommends that you choose clean tap water. Because if there are impurities in the water, the use of this impurity water will have some impact on the equipment. The impurities form a thick layer of scale on the inner wall of the boiler. Scale will gradually thicken with time, and the accumulation of thickness will affect its heat transfer efficiency, resulting in a waste of energy consumption. If the scale appears, it should be cleaned up in time, so that the heat can be concentrated in the scale, which is not easy to emit. .
Gas introduced gas steam boiler steam boiler stop sign Profile: natural gas steam boiler is a steam boiler gas, natural gas steam boiler with natural gas as fuel, the combustion in the furnace heat put out by heating the pot water, and allowed to vaporized into steam energy conversion device. Water pan (drum) is continuously released from the combustion of a gaseous fuel energy to heat the furnace temperature is increased and produce steam under pressure. Since the boiling point of water increases with increased pressure, the pot is sealed, the expansion of water vapor generated inside the pressure limited thermodynamic formed, strictly speaking, the steam boiler is heated in water at constant pressure saturated steam drum regasification water formed, is widely used as an energy source. Protection device: (1) protect the boiler water a boiler water level gauge plate supporting one to two, should always be compared with each other, inconsistent findings indicate that shall be corrected immediately. Class water level should be flushed, to determine their true level. While the water level comes electrode rod can accurately capture level signal to an alarm or a pump control. (2) steam pressure protection pressure controller: selection of high sensitivity of the pressure controller, the pressure is high, or low levels of signal to the electrical switches, other control lines or automatic control chain protection. Using pressure controllers and electrical contacts, the vapor pressure can overpressure alarm; single adjustable pressure controller or dual fire burning fire the actual operating pressure. Safety valve: safety valve is the last line of defense to protect the boiler, the boiler pressure exceeds the limit, according to the set pressure relief valve design with the school, the exhaust steam pressure relief, to ensure the normal operation of the boiler. (3) having a burner flame protection flame protection inlet means, combustion function is to detect, when the ignition failure or extinguish combustion middle, immediately off the burner into the oil (gas) solenoid valve, the blower continues to operate at this time, the furnace was purged combustible residual gas, after 20 to 30 seconds purge, and various auxiliary blowers automatically cut off power, the boiler operation stops. (4) self-locking power failure protection case, the boiler shutdown immediately burst self-locking power interruption, if the current power is restored, the boiler will not start at any time, you must reset release self-locking, to re-start the ignition. Editing boiler ignition procedures: 1. Check operation and (or) shift recording. 2, inspection, examination boiler, external. 3, check the main safety accessories. Safety valve, water gauge, pressure gauge, to be tight, reliable and sensitive. 4, check the water treatment equipment. 5, inspection equipment and soda water supply system pipe. Adjust the valves as required to start. 6. Check the oil supply equipment. After the above inspection qualified, you can start the boiler. Note: The boiler is a high-temperature, high-pressure thermal equipment, is one of special equipment, widely used in government agencies, public companies and all walks of life, it is dangerous and special equipment. Event of an accident involving public safety, it will cause huge losses to the state and people's lives and property. For public safety, people's lives and property safety, according to the State Council, "Regulations on Safety Supervision of Special Equipment", the boiler should use full attention the following matters: 1, should be accompanied by safety technical specifications of the factory boiler design documents, product quality certification, safety and the use and maintenance instructions, supervision and inspection certificate (safety supervision, inspection and performance certificate). 2, boiler installation, maintenance, alteration. Engaged in the installation of the boiler, maintenance, renovation of the unit shall obtain special equipment installation and maintenance certificates issued by the Provincial Quality and Technical Supervision, before engaging in the boiler installation, maintenance, alteration. Construction unit before construction will be prepared for installation, maintenance, alteration in writing inform the special equipment safety supervision and management department of the municipality or district, and will start informing sent to the local county level Quality and Technical Supervision for the record, told immediately after construction. 3, inspection of boiler installation, maintenance, transformation. After construction, the construction unit To State Quality and Technical Supervision of Special Equipment Inspection and hydrostatic testing of the boiler installation supervisory inspection declaration. After passing by the State Quality and Technical Supervision, State Special Equipment Inspection, County of Quality and Technical Supervision involved in overall acceptance. 4, registration boiler. After the boiler inspection, the use of units must be in accordance with the "special equipment registration and use of management rules", fill "boiler (census) Registration Form", the State Quality and Technical Supervision to register and obtain a "registration certificate to use special equipment safety . " 5, operation of the boiler. Boiler operation must be performed by trained and qualified to obtain "special equipment operator certificate" certified personnel to operate, must strictly abide by the rules and eight systems, six record. 6, check the boiler. Periodic inspection of boiler once a year, not be used without safety periodic inspection of boilers. Safety accessories safety valve of the boiler regular inspection once a year, pressure gauge biannually verified, may not be used without the periodic inspection of the safety accessories. 7, non-pressure boilers will be installed for the boiler pressure. Do not use water level gauge, safety valve, pressure gauge three safety accessories insufficiency boiler.
Henan gas boiler before which components should be checked before checking Henan gas furnace tube boiler, furnace, pipe tobacco, and other head and bracing member whether the normal pressure, with or without severe corrosion or deformation, cracks, gas boiler Henan left without inner scale, impurities, with or without tools objects, etc., and confirmed no one in the boiler, before they close all manholes, hand holes, into the holes, hand holes, the cover should be put gland n, should rubber ring or asbestos mat asbestos mat prepared cords asbestos rope between the manhole cover. To avoid the use of the mat, is bonded to the edge of the hole or holes of the cover, the two contact surfaces to be coated mat black oil and a mixture of lead powder, white lead oil to stop. Henan gas boilers, boiler external inspection for damage, the furnace heating surface should be checked, whether the heat insulation layer intact. Or whether there is residual fuel in the furnace soot within the examination. Chimney device can be reasonable. Check whether the position extinguishing apparatus reasonable, easy maintenance can extinguisher, heating pipes can open, close, barometer indicating whether correctly, the fan, the motor can properly steering damper can switch sensitivity. Conditioning installation can load the correct position, ignition electrodes, ignition position, the position of a small fire, the fire can preset position is good. The circulating pump leak-free, noise-free and temperature anomalies, adhere to the bearing housing oil level is normal, water outlet pipe flow. Henan gas boiler water treatment equipment, deaerator commissioning, check the boiler feed water feed water can reach the kingdom of the request.
At 15:31 on January afternoon 55 points, Zhangjiakou Municipal Publicity Department announced through the official micro-Bo: Zhangjiakou Shiqiao Eastern red floor Combibloc bath center for illegal use of obsolete coal-fired boilers, boiler and furnace door ring gall bladder junction cracking, resulting in rapid ejection soda.
At present, the accident has killed two people were killed and two injured, the injured have been rushed to hospital.
Since the accident the suspect, the suspect has been controlled.
It was a painful stricken by the accident, the suspect illegal use of coal-fired boilers have been eliminated, resulting in four families forever pain.
As can be seen from the government over the country began to strictly limit the use of coal-fired boilers, coal-fired boilers in order to face a fate or modification or elimination of the unlawful use of coal-fired boilers have been eliminated but can cause great harm, the accident is a obvious example.
Therefore, actively cooperate with the investigation of the relevant units of boilers, boiler out of strict compliance with the Code and running, grasp the safe operation of the boiler to a large extent, reduce the occurrence of such tragic accidents.