hot water gas condensing boiler constant
As one of Beijing's air pollution emission standards of the most demanding urban, environmental control is very strict. Beijing primary school campus Emerald City as one of the cradles of socialist culture successor, in terms of the quality of students' learning environment is put emphasis on one hundred percent. October 2017, Beijing primary school campus Emerald City with my company, signed a two Thalia T6 series vacuum hot water hot water condensing boiler constant for winter heating use.
Henan Gas Burner common faults and solutions 1, Henan combustion gas powered hot water condensing boiler constant, press the start, the motor does not turn the gas boiler Henan Faulty motor does not turn: (1) lack of pressure lock (2) solenoid valves lax, joints leak, check the lock (3) thermal relay opens (4) condition circuit has at least one is not satisfied (water level, pressure, temperature, and the programmable controller is powered starter) Henan gas boiler motor does not turn exclusion measures: (1) adjusting the air to a predetermined value (2) cleaning or repair of the solenoid valve the pipe joint (3) is not damaged by the checking device is reset and the motor current (4) check the water level, pressure, temperature gauge 2 if, after the normal purging before the start, but misfire Henan gas boiler fault cause misfiring: (1) is less than the amount of electric anger (2) solenoid valve does not work (the main valve, an ignition valve) (3) solenoid burned (4) unstable gas pressure (5) is too large air volume Henan gas boiler misfire Remedy: (1) inspection and repair line (2) renewal (3) to adjust the pressure to a predetermined value (4) decreases with the wind, to reduce the throttle opening
Steam hot water condensing boiler constant steam separator device works in the overall design of the steam boiler, steam separator device is essential, rapid separation of water saturated steam is to improve the steam quality to ensure that an important part of the normal operation of the boiler. Fuel gas boiler is not only fuel but also refers to the gas boiler. Previously no such dual-fuel boiler, burner because either fuel or gas, no dual fuel burners. With the rapid development of the world energy equipment, some European countries begin production and sales of fuel gas burner, dual fuel burner and boiler combination of organic birth of a new breed of boiler - fuel gas-fired boiler. Biomass boiler is a kind of boiler to biomass energy as a boiler fuel called biomass boilers, steam boilers into biomass, biomass hot water boiler, biomass stove, biomass thermal oil heaters, vertical raw biomass boilers, biomass boilers and other horizontal. Convenient to meet customer needs. Then, the authors will guide you to understand the working principles of steam and water separation device on the steam boiler. First, to avoid increasing the local load between the evaporation surface and the vapor space drum boiler, the steam is uniformly by water extraction. Second, it can effectively weaken the kinetic energy soda mixture into the tank, reducing its impact on the water. Third, in order to take advantage of inertia, and centrifugal separation, the mixture having a flow path soda rapidly changing, keeping in mind the shunt separation of water, to avoid being carried steam again. Finally, there is a large surface area, in order to adhere more water droplets. At the moment, a lot of steam separator type, according to the principle of the separation can be divided into natural and mechanical separation. The principle is to use natural separation of steam and water and the density difference between the force of gravity. Mechanical separation principle relies on inertial force, centrifugal force and adhesion. Water separation apparatus is often installed in a steam boiler and used underwater plate, baffle, plate uniformity, manifold, volute separator, corrugated sheet and steel mesh separators.
Gas hot water condensing boiler constant Burner Failures and gas boiler burners Failures and - best ￼ a gas boiler, gas boiler burner ignition misfire rod reasons: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Measures following five: Clear, renewal, adjust the distance, change and switching transformer. Second, gas boiler, but spark ignition rods misfire reasons: 1, the cyclone disc space ventilation is blocked carbon, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Measures are: Clear; first wash, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel); Check tubing and oil filters, insulation equipment ; remove peripheral screw pump, carefully remove the cover inside out oil network, with immersion oil; renewal of the test oil.