hr steam boiler condensing oil fired boiler best quality
Fast boiler particularly strong technical team, they listened carefully to our needs and give us tailored technology solutions, from boiler production, transport to the site installation and commissioning took only 35 days time, all aspects of the deal in place, the boiler quickly it is put into use. --customer feedback
In theory, the boiler fuel consumption under ideal operating conditions = boiler output / fuel calorific value / boiler thermal efficiency.
1. Boiler output refers to boiler power. Steam boilers generally refer to evaporation (t/h), and hot water boilers are thermal power (MW). So far, ZG boiler has been able to produce nine systems and more than 200 products. The wns series horizontal oil and gas boilers produced by ZG boiler have a capacity range of 1-20tph.
2. Boiler thermal efficiency refers to the percentage of effective heat and heat input to the boiler at the same time. Like the wns series of fire tube oil and gas boilers produced by ZG boiler, the thermal efficiency is high, up to 98%.
Henan gas treatment condensing boiler operation in the secondary combustion Accident Henan condensing gas boiler, deposited in the rear of the boiler flue gas condensing Henan combustibles (soot, carbon black) re-ignition combustion phenomenon called secondary combustion, also known as Henan condensing gas boiler flue tail and then burned. It will backpass severe, air preheater, induced draft fan and other equipment economizer even destroyed. 1. Henan condensing gas boiler secondary combustion phenomenon (1) a sharp rise in exhaust gas temperature, chimney to take smoke, fire or even smoke. (2) changes drastically furnace pressure, positive pressure occurs. (3) severe flue enclosure dark red. (4) when there is an air preheater, a sharp rise in the temperature of the hot air, pressure instability. (5) blast doors sometimes the tail action. Cause 2.Henan condensing gas boiler secondary combustion (1) poor atomization burner, oil, gas and incomplete combustion into the rear of the boiler. (2) combustion improperly adjusted, with insufficient wind or with the wind unreasonable. (3) Henan condensing gas boiler startup, shutdown during low furnace temperature, the unburned fuel in the furnace. (4) When shutdown or boiler fire, air gun valve is not closed. (5) the combustion chamber negative pressure is too large, too late to make the gas burn it into the rear of the boiler. (6) Long-term non-stop cleaning backpass furnace, accumulating a certain amount of soot or carbon black. (7) through the air preheater flue or leakage. 3. The gas processing condensed Henan secondary combustion boiler (1) should immediately stop the gas, stop the wind, shutdown. (2) closing the flue, and a baffle duct around the door opening, is prohibited to start sending, induced draft fan. (3) immediately extinguishing device into steam, carbon dioxide or other fire extinguishing means, (4) Strengthening Henan condensing gas boiler feed water and turn on the water, open the valve or economizer recirculation tube to protect the economizer is not burning. (5) When the exhaust gas temperature close to the temperature of the injected steam, or less than 150 deg.] C over 1h and stable openable inspection hole inspection, after checking element determines an ignition source, before the fan starts ventilation and cooling. (6) when the temperature drops below the flue 50 ℃, check before entering the flue tail heating surface, and should completely remove the flue soot. If not burning, can be re-started ignition; if burning, should be replaced, repaired burning member.
Use should pay attention to the problem of hr steam boiler condensing fired boiler best quality pressure gauge. Rated steam pressure of less than 2.45MPa steam boiler, a manometer accuracy no less than 2.5; equal to the rated boiler steam pressure 2.45MPa, the pressure is not less than 1.5. Dial gauge diameter of not less than 100 mm, to ensure that the operator can clearly see the surface pressure indication. 2. Steam boiler gauge plate should draw a red line that indicates the maximum allowable working pressure. 3. The steam boiler pressure gauge should be installed in place to facilitate the observation and purged, and should prevent high temperature, vibration and icing. 4. The steam boiler pressure gauge should be checked at least once every six months, after calibration seal should be sealed. 5. The steam boiler gauge connection tube not leak water and steam, otherwise it will reduce the pressure instruction value. Biomass boiler is a kind of boiler to biomass energy as a boiler fuel called biomass boilers, steam boilers into biomass, biomass hot water boiler, biomass stove, biomass thermal oil heaters, vertical raw biomass boilers, biomass boilers and other horizontal. Steam boiler is an energy conversion device, the energy input to the boiler fuel chemical energy, electrical energy, thermal energy and other forms of high temperature flue gas, and after converting the boiler, the steam output having a certain outside thermal energy, high-temperature hot water or an organic carrier. 6. A steam boiler pressure gauge measuring range should be compatible with the operating pressure of the device under test, the working pressure is generally 1.53 times, preferably 2 times the working pressure. Steam boiler no pressure gauge, pressure gauge or pressure gauge damage does not meet the requirements. When the steam boiler pressure gauge of the following circumstances, should stop using: 1, the surface of the glass broken or blurred dial; 2, lead-free seal, lead seal is broken or exceeds the calibration cycle; 3. When no pressure gauge pointer position is limited to the limit staple nail can not be restored, and the unlimited gauge pointer from zero rank bit data is out of range pressure layer. Difference; 4, leak or pointer jump table; 5, other defects affect the gauge accuracy.