industrial boiler efficiency industrial oil gas fired
2018, the Group's trade unions lead the effort and hard work. In June - July, the group took part in the front-line staff union workers vocational skills competition in Henan welders trials, employee segment slowly rise to become the dark horse on the field, won the "female bonding child" in the world, made in Anyang City fifty-one Heroine Heroine number of honorary titles. 2018, the group led everyone happy union work. "Division with only" mechanism in the company to bear fruit, youth workers get training and skills gradually improved. Rich in the traditional sense of "apprentice ceremony" making our "division with only" job skills training to become a shining Anyang City workers "business card." On the municipal key tournament organized by the company, young welder you compete to catch the top ten among them are four outstanding students under the "division with only" mechanism generated.
First, the reasons gas industrial boiler efficiency industrial oil fired burner ignition misfire bar: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the gas boiler ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs.
The cultivation of greenhouses is to artificially create an environment in which various fruits and vegetables can be grown in winter. To ensure the normal growth of plants, temperature stability is essential. In order to maintain a certain temperature in the greenhouse, various heating equipment is required. The application of heating industrial boiler efficiency industrial oil fireds in greenhouses can be very common. The different types of oil and gas boilers produced by ZG boiler are a kind of heating boiler that is very suitable for greenhouse heating.
（9）Combustion Adjustment method of Oil-fired Gas-fired Boiler
The combustion adjustment of oil-fired gas-fired boiler is successful and the load adjustment can be carried out after turning into normal operation. At this time, the combustion situation in the furnace should be observed frequently. If the atomization of oil and gas is not good, the flame jumps, the flame hits the furnace tank, and the exhaust temperature is too high or too low, the oil pressure, oil temperature, steam volume, air pressure and steam pressure should be adjusted in time to ensure the safe and economical operation of the boiler. The oil pressure and the pressure are related to the boiler load. The adjustment of the oil pressure is realized by adjusting the pressure of the burner or the amount of oil returned. The adjustment of air pressure is achieved through the opening of the valve. When adjusting a load, enter At the same time, the air volume adjustment must be carried out synchronously to ensure the reasonable match between the oil quantity and the air volume, so as to achieve the purpose of economical operation of the boiler.