latest horizontal 2 ton oil gas fired steam boiler
Since our company uses WNS6-1.25-YQ split two condensing boiler, the boiler runs very stable, high degree of automation, greatly reducing the labor intensity of fireman our staff, because running very clean without any emissions, but also greatly improved our paper mill house and the surrounding environment, high operating efficiency boilers. Service is also very timely response to our technical consulting reply quickly and accurately. Especially for regular visits to thank! --customer feedback
Determine the location of the latest horizontal 2 ton oil fired steam boiler room siting what issues need attention 1, boiler room refers to the building design boiler and ancillary equipment, water treatment facilities, pumps and sub-steam (water) tank and the like. Boiler should be separate and independent from other buildings. Boiler room should not be set directly in crowded places (such as public bathrooms, classrooms, restaurants, auditoriums, shopping malls, waiting rooms, etc.), or at the top, bottom, or the immediate neighborhood of the main evacuation port on both sides. 2, the new boiler room should not be connected to the house. 3, provided in the boiler room such as a semi basement layers or high buildings or the first layer must meet the following conditions: (1) each steam boiler rated evaporation does not exceed 10t / h, steam pressure does not exceed the rated 1.6MPa; rated each water boiler (including direct fired absorption chiller-room unit) does not exceed the output 7MW, the rated water temperature ≤95 ℃. (2) Each steam boiler must have a reliable overpressure protection interlocking means interlock protection device and the low water level. (3) accessories and safety interlock protection device for each boiler to regular maintenance and testing to ensure that sensitive and reliable. (4) the building structure between the boiler should have the appropriate proof Measures. (5) operate independently of the fireman who must hold the appropriate level of operating permits fireman, boiler and continuous operation of the same class more than five years, has not been an accident. (6) There must be safe evacuation routes. 4, should not be located in the boiler room or a high-rise multi-story building basement, an intermediate floor or roof, but the conditions required setting time, shall meet the requirements of paragraph 3, the first gist of the present, should meet the following conditions, and former boiler room should be set prior consent districts of the city and over special equipment safety supervision agency: (1) steam boilers rated evaporation each no more than 4t / h, rated steam pressure does not exceed 1.6MPa; each heat rated water boiler (including direct fired absorption chiller-room unit) does not exceed the output of 2.8MW, the rated water temperature ≤95 ℃. (2) must be light oil, city gas, natural gas as fuel or electric heating boiler. Underground boiler room non LPG gaseous fuel or a density greater than 0.75. Connection (3) using a fuel supply pipe welding backing. In addition, when set in the basement boiler room, blowdown or appropriate measures should be set up sewage. When using gas as fuel, the exhaust system is also provided accident. 5, not connected to the boiler room A, (B) and (C) a liquid combustible fire risk room. If connected to other production plants, application firewall separated. Waste heat boiler is not so limited. Boiler production plant belongs to class D, between the fuel tank, between the pump delivery room Class C production, between the gas regulator belonging to the delivery room A of production. 6, between the outer wall or roof of the boiler should be at least equivalent to 10% of the area between the boiler pressure relief area (such as windows, skylights, shutters, etc.), and the relief port should avoid crowded places. 7, boiler room should be equipped with emergency lighting and evacuation signs, emergency lighting voltage shall not exceed 36V.
Gas-fired latest horizontal 2 ton oil fired steam boilers can be cleaned during cleaning using efficient and environmentally friendly non-corrosive detergents. This will cause the tube to expose the primary color of the metal and reduce the impact of dirt and bio-algal sludge. After ignition of gas-fired steam boiler, attention should be paid to observing the furnace temperature and the temperature of the main steam. With the increase of main steam pressure, the flue gas temperature of boiler is obviously increased after ignition. If the temperature does not rise, you should go to the scene immediately to inspect the oil gun fire. The scale thermal conductivity of a gas-fired steam boiler is only 1/10 of that of steel. This hinders heat transfer when it scales on a heated surface. In order to keep the boiler in use The output shall increase the temperature on the combustion side. The increase of outlet temperature of gas-fired steam boiler increases the loss of gas-fired steam boiler, and the scale on the water wall of equipment will effectively reduce the heat transfer effect, which may lead to the increase of the temperature of water wall and the burst of water wall. When a gas-fired steam boiler is in operation, a series of chemical and physical reactions will occur in the furnace. In use, it will effectively form a hard and dense scale on the heated surface, which will directly lead to its heat exchange. The reduced efficiency and corrosion due to scale will reduce the heat absorption of gas-fired boilers.
The scaling of gas-fired latest horizontal 2 ton oil fired steam boiler not only reduces the thermal efficiency of the boiler, but also increases the temperature of the heating surface of the boiler, causes damage to the heating surface, and even causes the explosion accident of the boiler. Therefore, the use of soft water treatment equipment, strictly according to the process operation of boiler feed water softening treatment equipment, control boiler feed water quality, can delay the formation of the scale. At the same time, it is very important to control the boiler scale in real time, master the boiler scale and clean the scale if necessary. Because the temperature of the gas-steam boiler body and the steam-water heat pipe system is higher than the air temperature in the boiler room, some of the heat is emitted through radiation and convection into the surrounding air. This becomes a loss of heat. Boiler Therefore, the heat loss should be reduced when the heat insulation and heat pipe system of the boiler are damaged or leakage is discovered. The increase in noise from gas-fired steam boiler burners is mainly due to the closure of the valve or insufficient oil intake in the oil path, blockage of the oil filter, or because of low inlet temperature, high viscosity or oil on the pump. Too high temperature; oil pump failure; fan motor bearing damage; due to dirty turbine impeller, the equipment is too loud. This failure occurs when a gas-fired boiler is in use and is not easy to atomize (heavy oil) because of the high viscosity of the oil; it is also due to cyclone and jet The distance between the nozzles is inappropriate; in addition, because the burner is worn or dirty; it is also due to the excessive heating temperature of the spare fuel tank, resulting in steam pumping the oil pump out of the oil pump; or because the oil in the oil boiler is hydrated. Gas steam boiler feed water contains a variety of impurities and calcium, magnesium and other scaling substances, the boiler will inevitably expand. The thermal conductivity of the scale is very low, so once the surface is polluted by the hot surface, the exhaust temperature of the boiler will increase, and the heat loss of the exhaust gas will increase due to the increase of the thermal resistance. The experimental data show that the heat loss of waste gas will be increased by about 2%-4% when 1mm oxide is formed on the heating surface of boiler. The thicker the scale on the heating surface of the boiler, the greater the thermal resistance, and the lower the thermal efficiency of the boiler.