mpo iq oil fired high efficiency water boiler
If the configuration boiler fuel gas or dual fuel burners, then the boiler is oil or gas boiler. Fuel gas-fired boiler is a more general concept, fuel gas-fired boiler is divided into mpo iq fired high efficiency water boilers, hot water boilers, steam boilers and thermal oil boiler, according to their own use to select a different fuel gas-fired boiler time of purchase.
A, WNS series automatic fuel (gas) steam boiler 1, an internal combustion boiler using a horizontal double quick return smoke wet back structure, the body-mounted using the waveform furnace, combustion chamber and back to the waveform furnace, connected to threaded pipe. After exotherm temperature flue gas flame in the furnace, carried to the threaded pipe via the folded back to the combustion chamber to the convection heat before entering the smoke chamber; high temperature flue gas enters the condenser back energy, the heat transfer by sufficiently by chimney into the atmosphere. 2, for a variety of boiler fuel oil, natural gas fuel, city gas or liquefied petroleum gas. 3, the boiler before the smoke box with movable lid cigarette, demolition, convenient rear access. Boiler with integrated burner, has started fast, high efficiency, high degree of automation features, the need to provide for a variety of local life, civil and industrial steam. 4, a boiler with full instrumentation system valve, the valve body has a boiler inlet valve, check valve, the main steam valve, safety valve, drain valve, air valve and the combustor brought solenoid valve. Water meter with a measuring point pressure display, display and control drum pressure, exhaust gas temperature display, the temperature and pressure of the burner is displayed. 5, combustion and boiler feed water using automatic control, automatic adjustment, easy operation, low labor intensity and safe and reliable protection devices, easy maintenance and repair.
Steam boiler is one of the indispensable devices in the pharmaceutical industry, decoction of Chinese medicine, medicine drying, sterilization, cooking gum, drying, tabletting and capsule production processes, a large amount of steam will be used. West Libang Pharmaceutical Co., Ltd. is a pharmaceutical research and development, production and sales of high-tech enterprises, the existing anesthesia, cardiovascular, child immunization, pharmaceutical raw materials, pharmaceutical excipients, nutrition series of six automated production lines. With the increasing strength of China's environmental protection, some high-pollution devices are making the transition to clean environmental protection. Libang Pharmaceutical respond positively to national coal to gas policy, decided to change the existing coal-fired boilers to clean better gas steam boiler. Fast boiler with strong comprehensive strength in the field of clean energy, Libang Pharmaceutical after conducting comprehensive consideration, determined to cooperate with the fast boiler. The two sides further understanding, party fast technical engineers according to production needs state power, and soon its development of specific solutions for its recommendation of a 6 tons of steam condensing gas steam boiler (WNS6-1.25-Y.Q).
What does the Fangkuai boiler tell you about instrument activity analysis? What is the effect of instrument activity analysis? The operation of the boiler is reflected by the instructions of various instruments. According to the indicator data of the instrument and its changing trend, it is the analysis of the instrument activity to analyze whether the boiler's working condition is normal or not. The normal operating parameters of the boiler are measured by various thermal monitoring instruments in various parts. The vehicle data include pressure, temperature, flow rate, water level, current, etc. In normal operation, by monitoring the operation of these parameters, we can analyze and judge the operation condition of the passageway, and when the accident occurs, we can also pass the Abnormal data changes to analyze and judge the location and nature of the accident, this timely handling of the accident to create conditions. The surge of induced fan is due to the excessive differential pressure in the inlet and outlet of its static blade. The differential pressure of the inlet and outlet of the stator blade is influenced by the resistance of the pipe, and the same induced fan is more prone to surge when the resistance of the static blade opening pipe is large. The static blade opening of the induced fan produces the corresponding wind pressure and flow rate. When the pressure and flow rate produced by the fan are greater than or equal to the resistance of the flue gas pipe, the fan can work stably without surging. When the resistance of the pipe increases, the pressure flow at the outlet of the fan can not overcome the resistance of the pipeline system. The force reverses the current. When the pipe resistance is reduced to the fan outlet pressure, the flue gas flows downstream. The smoke flows back and forth in such a way that it is surging. Therefore, when the resistance of wind-smoke pipe is large, it is more prone to surge when the output force is not enough. The influence of starting and stopping pulverized coal production system on boiler combustion condition is analyzed. As a result of the three-time air belt powder, the furnace fuel quantity increases / decreases, and the oxygen content increases / decreases relatively when the pulverized coal production system is started / stopped. When the pulverized coal making system starts for a long time, the boiler flame length is long, the furnace fire filling degree is good, and vice versa; under low load, the multiple pulverizing system operates or completely stops the pulverizing system, especially to prevent the flame from suddenly extinguishing. Once What is the cause of duct clogging? How to prevent it? Reasons: 1) the burner is blocked by coke or the inlet of the burner is partly blocked by small oil gun. 2) too many impurities in pulverized coal, too high speed of pulverized coal feeder, too heavy pulverized coal and too low primary wind speed. 3) the speed of powder feeder is too high. Too much powder to blow away in time. 4) the wind pressure is too low once (the wind door is not open or the opening degree is too small), do not take away powder. Preventive measures: 1) according to the speed of the powder feeder and the load of the unit, the corresponding primary air pressure should be adjusted in time, the speed of the powder feeder shall not be greater than 700 rpm, the primary wind speed of each unit shall be kept at 25 ~ 30 m / s, and the mixing temperature of the primary air and powder shall be controlled at 180. At ~ 250 ℃, the primary wind pressure depends on the load and coal quality, and the range of variation is in the range of 2.5~3.8kPa.2) it is found that the primary wind speed is too low. When the primary air temperature is lower than the normal value, the primary air velocity and the primary air temperature corresponding to the speed of the powder feeder should be reduced in time. 3) the boiler oil tank stop powder feeder should fully blow the tube. Blow away the powder from the powder tube. 4) scorch or clog the fire nozzle and try to get rid of it. Which causes the induced fan vibration? 1) motor bearing oil shortage, resulting in bearing wear and vibration; 2) coupling installation center is not good; 3) induced fan stall surge; 4) induced fan ground angle bolt Loose; 5) blade ash or wear, out of balance.