national inspection free oil gas steam generator
As the cost of powering this equipment by burning fossil fuels has steadily risen, the use of biofuel cogeneration as a source of power production has become more prevalent. Many sugar mills have updated their bagasse-fired boilers and linked them to generators that produce electricity used to power the mill’s operations and to be sold to the local power grid.
For large and medium-sized enterprises which do not have heat supply from the central thermal power plant, when the continuous and stable steam consumption is above 20t/h, there are generally conditions for the establishment of self-provided thermal power plants. This kind of enterprise can choose 20t/h medium pressure boiler type or 35t/h medium pressure and sub-high pressure boiler, 1.5MW or 3MW back pressure type steam turbine-generator set, and build self-provided thermal power plant, which is mainly heating and auxiliary to generate electricity, and can obtain great economic benefits. Compared with the dispersed small-scale industrial boiler, the fuel consumption of the cogeneration is equal to that of the small-scale boiler due to the higher thermal efficiency of the boiler. Under the same heating conditions, it can be obtained by using co-generation of heat and power. Extra power.
It provides fast side of boiler equipment, installation and commissioning after all normal, we immediately put into use, the hotel did not delay the normal heating. Meanwhile boiler capacity, energy efficient, fully able to meet the needs of heating and bathing water in our hotel rooms. --customer feedback
Small gas steam boiler in the hotel building applications in daily production, how to save energy and reduce the emission of pollutants, reduce costs, increase economic benefits to the business, the real problem is getting attention, and gradually resolved. Shenyang is a hotel accommodation, offices, restaurants, stores in one large commercial buildings, construction area of 6 × 104m2. During the heating period, heating systems, domestic hot water steam system, laundry room used by the municipal heat supply network. After the heating period, domestic hot water systems, steam laundry prepared from 2 model white WNS8-1.25-YQ fuel steam boiler (heating of serving as backup boilers) for the steam, steam production of single 8t / h. Steam boiler room to the sub-cylinder (in the basement podium) linear distance is 200m, and specifications for the steam supply pipe DN250mm, Buried employed, the compensator 4 disposed manhole. Based on the actual measured amount of steam on the hotel, and the application of energy-saving small gas steam boiler in the hotel building were discussed. Selection 2 gas steam boiler us 2009 June 7 to July 1 for steam consumption for domestic hot water systems, laundry room were measured. Average pressure of 0.08MPa steam, hot water systems, laundry average daily amount of steam were 7.43,2.43t / d. Two systems together, the maximum amount of steam per unit time and the average amounts were 0.77,0.41t / h. From the measured data, daily 9: 30-11: 30, 15: 30-17: 00 cooking gas peak, the highest air consumption is 19.65m3 / h, the hotel into the household gas pipeline gas supply capacity of 95m3 / h. According to domestic hot water, laundry room two systems unit time summer highest steam consumption is 0.77t / h, should be used in a 1t / h gas steam boiler, its gas consumption is 76m3 / h. In actual use, reasonable arrangements for gas time, can fully meet the demand for gas gas steam boiler. From the above analysis, the steam production of the hotel is much larger than the existing fuel steam boiler steam summer practical usage. According to the measured summer daily expenditure of more than just fuel costs more than 3000 yuan / d. Underground layer may be mounted on a podium 1t / h gas steam boiler, steam lines since all indoors, and therefore low cost pipeline system, and reduce the emission of pollutants, environmental protection efficiency significantly. 3 gas steam boiler room design of the hotel podium underground over 3 floors, including the basement of the original generator set oil storage has been discontinued, construction area of about 60m2, close to the basement exit ramps from the gas pipeline into the family 8m, after transformation, can be used as gas heating boiler room. Gas heating boiler heating system flow shown in Figure 1. Gas heating boiler to be mounted ventilation system, the ventilation normally not less than 6 times / h, accident ventilation of not less than 12 times / h, the amount of exhaust air volume should be slightly larger, so that the boiler room space maintain positive pressure, and the ventilation should be selected proof products. Gas heating boiler to be mounted combustible gas detection and alarm devices, combustible gas detection and alarm device to automatically signal when gas leakage occurs, the emergency shut-off valve closed and to ensure that no further leakage of the combustible gas. Water spray system shall be installed, and the sprinkler system in conjunction with the original. Gas heating boiler in order to prevent water from leaking into the premises are ground floor, the ground should boiler room waterproofing and drainage ditch, the concentrated water discharged to the ground floor drainage system pressure, into the room promptly [1,2 ].