natural gas consumption of 11ton boiler
The main data processing means is automatically shutdown when the consumption of 11ton boiler pressure is too high, the combustion system will stop working; operating power may also be changed, single-stage or two-stage combustor; can adjust the amount of oil (or gas) to achieve proportional control, whereby depending on the steam pressure adjusting load operation of the burner, to ensure safe operation of the boiler.
2. Environmental policy is required for consumption of 11ton boiler emissions. Coal-fired boilers for waste pollution and energy of the atmosphere is amazing. Many cities have been expressly prohibited by the new economic development zone on the coal-fired boiler, while the use of gas, oil, electric central heating boiler or cogeneration.
3. The boiler is the initial investment, including the boiler unit, ancillary equipment, construction investment and other related costs.
2018ISH heating HVAC industry event, fast Boiler "Thalia T7" was set aside to hold the event May 23, ISHChina & CIHE China (Beijing) International heating ventilation air conditioning, heat pumps fresh air and home comfort systems and technology exhibition in Beijing International Exhibition hot center opening.
With the increase of air supply volume, the mixture of oil mist and air is improved, which is beneficial to combustion. However, if the air volume is too large, the furnace temperature will be decreased and the incomplete combustion loss will be increased. At the same time, the heat loss of exhaust gas will be increased and the power consumption of the fan will be increased because of the increase of flue gas. If the air volume is insufficient, the combustion will be incomplete, resulting in carbon deposition at the tail, which is prone to secondary combustion accidents. Therefore, each consumption of 11ton boiler should pass the thermal efficiency test to determine its economic air volume at different loads. In practice, the stoves usually take into account the ignition of the nozzle and the carbon dioxide or oxygen content in the flue gas. Content to adjust the supply air volume. If it is found that the combustion condition of a nozzle is not good, or if the atomization plate with different aperture is replaced, the air pressure of the supply duct should be kept unchanged, and the opening degree of the duct baffle of the nozzle should be adjusted to normal combustion. If the fuel quantity changes due to the change of the oil pressure in front of the furnace, the opening of the fan baffle should be adjusted to achieve normal combustion by changing the air pressure and air volume of the air supply duct when it is necessary to adjust the supply air volume.
3) the observation and analysis of all kinds of flame when adjusting the fuel oil. Generally through the fire point adjustment and flame center adjustment to complete the flame adjustment. The ignition point of the oil mist should be close to the nozzle, but there should be no tempering. Early ignition is beneficial to complete combustion and stability of oil mist. However, the fire is too early, too close to the nozzle, easy to burn the nozzle and furnace wall to determine the mouth. Furnace temperature flying oil varieties and atomization quality, as well as air volume, wind speed and oil temperature, will affect the distance and proximity of the ignition point. So if you want to adjust the ignition point, you should find out the cause in advance, and then take targeted measures. When the boiler load is constant and the oil pressure and oil temperature are stable, Should be based on the ignition point wind speed and wind distribution situation.