oil gas fired horizontal steam boilers seller
Small oil-fired boiler flameout protection device use: small oil-fired boiler furnace space Product Introduction small oil-fired boiler of large and adaptable load capacity. Rational design of steam separator apparatus built to meet user requirements need to use higher quality steam. Furnace open manhole, head holes, hand holes, to facilitate the internal furnace to clean up, make repairs, maintenance is very convenient. Boiler safety interlock with multi-level protection: protection pressure switch (higher than the set auto stop and pressure), the low water level protection (boiler water level is below the warning level in the body, and automatically cut off power alarm), the protection valve (boiler pressure exceeds the pressure of work, discouraged automatic blood pressure), ensure that the boiler in a variety of conditions foolproof, secure home. Mechatronics combined organic appearance, new sophisticated, compact, less space, easy to transport and install. Thermal insulation materials and the use of new high-quality white color plate package, lighter in weight, good insulation properties, beautiful, not rust. Use flameout protection device for small oil-fired boiler to prevent furnace explosion, the fuel (gas) boiler must be set flameout protection means functions combustion in the monitoring of the furnace (including an ignition when the ignition failure or combustion halfway off, typically 5 seconds the re-ignition, run 1 second, off into the oil (gas) solenoid valve, and turns on and audible alarm signal, when the blower continues to operate, the residual gas was purged of combustible furnace, after 20 to 30 seconds after purging, and various auxiliary blowers automatically cut off power, the boiler stop running.) by the flame monitoring and control device component. Role is to monitor the flame control device signals the presence of a flame or interrupted. The main use of the photomultiplier tube, a photovoltaic cell and photosensitive resistance, they have an infrared type or ultraviolet type, A photoelectric conversion element, the working principle of the light converted to the corresponding strength of the radiation intensity of current. And a linear output state, sometimes weak induction current, through amplification, in order to have an effect on the controller.
Wuhan Port District Social Welfare Institute (apartments for the elderly) is invested by the government pension services, with a total construction area of 38,000 square meters, 532 beds, mainly adopt destitute persons, social support on behalf of the elderly. Hope to provide welfare to the elderly year-round 24-hour hot water, the original boiler equipment can not meet this demand, therefore, require additional purchase orphanage hot water boiler. After much investigation, in cooperation with the welfare determined fast boiler, provides three integrally condensing gas hot water boiler (WNS1.4-1.0 / 95/70-Y.Q) by a fast boiler.
Fuel gas-fired boiler fuel gas-fired boiler product presentation is different from coal-fired boilers, which requires the use of a burner fuel is injected into the boiler furnace using a combustion chamber without the use of fire grate facilities. Because not produce fuel ash after burning fuel gas-fired boiler, fuel gas-fired boiler so without slagging facilities. Oil injected into the furnace, if the gas and air mixture within a certain range, or turned off, it is easy to explode. Therefore, fuel gas-fired boiler combustion required to adopt automation and control systems. Fuel gas boiler compact, small boiler and ventilation, water supply, control and auxiliary equipment are arranged on a distribution box, it may also be assembled and medium-sized factory. Fuel gas-fired boiler safety valve installation points introduce fuel gas-fired boiler safety valve needs to be installed in the correct installation steps, in order to avoid mistakes, resulting in what needs to pay attention to danger, fuel gas-fired boiler safety valve installed it? Here, I introduce: 1 fuel gas boiler safety valve should prevent the lever means and movement of the self-weight limit leverage deviant guide tube, a spring safety valve should lift and handle means for preventing movement of the adjustment screw is screwed lightly . 2. Rated to 0.5t h evaporation boiler fuel gas /, at least two safety valves installed; Rated evaporation 0.5t h or less fuel gas boiler /, mounted on at least a safety valve. The separable exit of the economizer, steam superheater outlet of the safety valve must be installed. 3. Fuel gas-fired boiler safety valve to the boiler tubes, cross-sectional area should not be less than the import safety valve cross-sectional area. If several valves installed together with a short tube directly connected to the drum, short tube passage area not less than 1.25 times the area of all the exhaust valve. 4. Fuel gas boiler safety valve should be installed vertically in the boiler drum, header high position. Between the valve and the drum or header, not equipped with access to the steam outlet pipe and the valve. 5. For rated steam pressure less than or equal to 3.82MPa boiler safety valve throat diameter of not less than 25mm; the rated steam pressure is greater than 3.82MPa boiler safety valve throat diameter of not less than 20mm. 6. Fuel gas-fired boiler safety valve should normally be installed exhaust pipe, exhaust pipe should be through a safe place, and there is sufficient cross-sectional area to ensure the smooth flow of exhaust. Safety valve exhaust pipe at the bottom should be fitted to the safe location of drainage pipe, the exhaust pipe and drainage pipe not allow the installation of the valve.
Steam boiler in textile industry mainly supply steam to dry the textile products and as the textile oil fired horizontal steam boilers seller manufacturer, ZG Boiler can designs and manufactures biomass fired steam boiler, gas fired steam boiler, oil fired steam boiler, coal fired steam boiler, CFB boiler and so on and it can supply specific industrial textile steam boiler according to customers’ requirement. However, textile industry is suffering from energy crisis especially gas, low pressure and high demand among residence in winter causes completely breakdown, therefore, coal fired steam boiler become more popular than other kinds of steam boilers.