oil hot water heating boiler thermostat control
Exhaust gas has been plagued by sewage paper industry, paper industry pollution problems of the country very seriously. Fujian Heng paper packaging company has been committed to the use of clean-type hot water heating boiler thermostat control paper processing. October 22, 2016, David Carse, the paper with my company, signed a 6 tons of steam an integral condensing steam boiler for the production of corrugated cardboard and other paper products. I provided the boiler greatly solve the problem of sewage wastewater Heng paper. After the boiler operation, both to meet local environmental requirements, but also reduce operating costs for the constant boiler paper products.
Accessories szs system and hot water heating boiler thermostat control water tube boilers which (1) the fuel system the fuel system of pumps pumping fuel from the fuel tank to the day tank, is then withdrawn from the daily tank fuel pump, through a pressurized, heated, and sprayed into the filter oil atomization. This system is usually divided into the border daily service tank and oil supply system and fuel system. (2) feedwater, condensate water, steam condensate system piping system comprising pipes and valves and piping and other equipment from the deaerator. Steam system comprises a steam pipe and various valves. (3) the ventilation system features a ventilation system external air into the furnace for combustion of fuel, and the products of combustion (flue gases) discharged from the boiler to the atmosphere. In the process of air and flue gas flow, there will be a variety of flow resistance, if the natural ventilation generated by a chimney to overcome the resistance to flow, called natural ventilation. Obviously, this ventilation air flow generated is small, can be improved by increasing the height of the chimney natural ventilation. Using a fan to overcome the flow resistance of various ventilation systems, called mechanical ventilation. Mechanical ventilation is divided into positive pressure ventilation, ventilation and negative balanced ventilation. The so-called positive pressure ventilation means for sending air to the boiler and the flue gas discharged from the boiler to the atmosphere. Primer furnace boiler flue gas exhaust blower suction chamber, known as negative pressure ventilation. (4) boiler auxiliaries and monitoring instrumentation and monitoring instrumentation, boiler accessories boiler safe and economic operation are necessary, including: (A) as an annex to ensure the safe operation of the boiler: water level gauge, safety valve, pressure gauge and thermometer indicating steam parameters ; B) combustion supervision parts: pressure gauge, carbon dioxide indicator, oxygen table, smoking view mirror.
2 tons of diesel hot water heating boiler thermostat control has a boiler which is a kind of model diesel fuel boiler, such as the title of the diesel boiler 2 tons can be divided into 2 tons of diesel steam boilers and hot water boilers 2 tons of diesel oil in accordance with its nature, generally 2 diesel steam boiler tons of little use, basically there are few places to use, because some of powered industrial steam boilers are for the most, so most buy two tons of diesel boilers for heating or for all customers hot, multi-fuel reserves sufficient for these areas of some refineries or oil exploration base, then the customer exactly how to choose the type 2 tons of diesel fuel boilers it? This chapter focuses on the next introduce to you: It is well-known oil-fired boiler factory in Henan square quick introduction, two tons of diesel boiler contains two main one is the WNS type one is SZS type, among which the best-selling type WNS, why, mainly because of the type of boiler small footprint, and high thermal efficiency, the waveform of the boiler furnace structure, increase the cycle so that the heat of the furnace off gas in value with a more abundant, and the boiler fuel savings, low price is now two tons of diesel boiler best-selling series. More questions about two tons of diesel boiler model and technical parameters please consult the online customer service!
Electric hot water heating boiler thermostat controls not only need to be strictly checked when buying, but also need to use the code of practice, so as to avoid the danger to the person. The electric boiler uses a long time will have the aging phenomenon, then how to carry on the maintenance to the electric boiler? The following electric heating zone you understand the maintenance of electric boilers: the general use of electric boilers within 1 to 2 years to carry out a certain maintenance of electric boilers, it is conducive to the normal operation of electric boilers, Regular maintenance is also the basic to ensure the normal operation of the electric boiler. 1, when maintaining the boiler, the power supply must be cut off and pressure relief must be made. 2. Burners should be removed from the boiler body every two months. It really cleans up foreign bodies such as charcoal and dust. The photo-electric tube is polished once a month. The fuel filter should always be cleaned and filtered. Carefully clean the inner filter screen of the oil pump and do not destroy the gasket. Burner must not run without oil, so as not to damage the oil pump. 3, the water level gauge should be kept clean at all times, open the cleaning valve once a day to ensure clear water level. 4, the safety valve is pulled once a day in case of rust failure. After the work, check if the tools, materials, accessories are complete, to prevent remaining in the furnace and other spaces. Special person delisting, acceptance and acceptance of qualified before leaving the work site, the final maintenance records, in order to prepare after Query.