pakistan saw dust fired boiler manufacturer
Causes high energy electric steam pakistan saw dust fired boiler manufacturers are what it? Through a lot of practice and testing, in terms of common understanding has been great progress in the actual design and the increasingly close. Current electric steam boiler heating operation and management, mainly built housing distribution sector professional management and self-management units into two categories, in general management level is relatively low. Some good situation under professional management, self-management units are few higher level, the most basic is in the "high energy consumption, low efficiency" of the situation. In addition, the prevalence of social importance heating, and energy-saving awareness is weak, new technology, new achievements rarely used, long stay in the extensive management experience, failed to improve the refinement of scientific management.
In the fierce competition in the market, fast pakistan saw dust fired boiler manufacturer adhere to "not forget the early heart, sustained ingenuity" of the faith, taking the long view, establish and improve a comprehensive overall solution, leading to control market trends, improve the environmental performance of the boiler, make unremitting efforts to build China clean boiler brand.
The method of starting the pakistan saw dust fired boiler manufacturer during boiler startup control drum wall temperature difference of the process to be controlled in a predetermined drum wall temperature difference may take the following measures within 40 ℃: (1) water temperature before ignition can not be too high, not too fast speed, according to rules of execution. (2) water is completed, the bottom may be put into steam heating conditions. (3) strictly control the raising rate, in particular 0 ~ 0.981MPa boosting speed stage should be less than 0.014MPa / min. Rate of temperature rise not greater than 1.5 ~ 2 ℃ / min. (4) should be regularly switching angle oil gun, until the next row when four full cast oil gun, each part as far as possible evenly heated. (5) via the above-described operation can not effectively control the drum, the lower wall temperature, then when the approach or reach 40 ℃ booster should be suspended, and the sewage regularly, in order to enhance the circulating water, and stabilized until the temperature difference is less than 40 ℃ line boost.
Boiler for heating 50,000 square meters
When the weather is cold, the heating boiler begins to perform its heating function. Because of the important role of heating boilers, many companies, planting, breeding, schools, hotels, hospitals and other industries will use them. For most enterprises, hot water boilers are generally selected when heating boilers are selected, and heat is transferred through the pipes through hot water.