pharmaceutical industry atmospheric fire tube boiler supplier
Method Three: Learn from Video. ZG Boiler will send you some pharmaceutical industry atmospheric fire tube boiler supplier installation, operation, maintenance related books or videos. You can learn it on your own.
Use steam pharmaceutical industry atmospheric fire tube boiler supplier pressure gauge should pay attention to the following items: 1, rated steam pressure is less than 2.45MPa steam boiler, pressure gauge accuracy must not be both 2. 5; Rated steam pressure large or equal to 2.45MPa boiler, pressure must not be less than 1. 5 class. The dial diameter of the pressure gauge shall not be less than 100 mm to ensure that the operator can see the surface pressure indication clearly. 2. A red line should be drawn on the pressure dial of the steam boiler pressure gauge, indicating the maximum allowable working pressure. 3. Steam boiler pressure gauges should be installed in places that are easy to observe and rinse, and should be protected from the shadows of high temperatures, freezes and vibrations Ring. 4, steam boiler pressure gauge should be checked at least once every six months, after calibration should be sealed. 5, steam boiler pressure gauge connection pipe should not leak, steam leakage phenomenon, otherwise will reduce the pressure indicator value. 6. The range of the steam boiler pressure gauge shall be adapted to the working pressure of the measured components, usually 1.5 times of the working pressure, preferably 2 times of the working pressure. Steam boiler does not have a pressure gauge, the pressure gauge is damaged or the installation of the pressure gauge does not meet the requirements, steam boiler pressure gauge should be stopped when one of the following: 1, broken surface glass or dial calibration unclear; 2, no lead seal, lead seal damage or Beyond the calibration period; 3, when there is no pressure, the pressure gauge pointer of the finite pin cannot be restored to the limit pin, and the data of the infinite position gauge pointer deviating from the zero position exceeds the pressure coat allowed? Poor; 4, gas leak or pointer jump in the meter; 5, other defects that affect the accuracy of the gauge.
Our hospital requirements for environmental protection, health and safety in these areas is very high, for a wide variety of market pharmaceutical industry atmospheric fire tube boiler supplier is also very headache and confusion, there fast boiler solve the above problem, the boiler set clean environment to provide for our hospitals and efficient operation in one, coincides with the philosophy of our hospital. --customer feedback
How to save energy for gas-fired pharmaceutical industry atmospheric fire tube boiler supplier
Energy conservation is a problem that needs to be considered in industrial production, especially for industrial boilers that support thermal power support for industrial production. Energy conservation is a reflection of the technical level of the boiler industry. With the implementation of the national energy conservation and environmental protection policies, the traditional coal-fired industrial boilers have gradually been replaced by natural gas steam boilers, and a revolution in energy-saving and environmental protection has taken place in the field of industrial thermal power.