professional 21 t h coal fired steam boiler
About six tons of professional 21 t h coal fired steam boiler shutdown of a temporary shutdown: It is planned, therefore slow cooling during shutdown protection device, it should also pay attention to safety, pause furnace according to the rules in Chapter IV Fenghuo (pressure fire) get on. 2, safety shutdown: care should be completely stopped even on normal operation plan for 1 to 3 months to be a shutdown, shutdown should maintain more safety injection apparatus, after the shutdown, and other water-cooled furnace to below 70 ℃ when they let go of the gas, open manholes, hand holes, rinse the pot with water scale. 3, emergency shutdown: the boiler operation, when the case of the following circumstances, should an emergency shutdown, and notify the relevant authorities. (1) expanding the cease-fire should first see if the water table level is called to take water law. If Inception water table, water cock side, and then close the steam cock, and then turn on the water faucet open and close repeatedly called after water, still can not see the water. (2) All water supply equipment failure. (3) All water gauge, pressure gauge, safety one of all the failures. (4) a boiler or furnace wall element damage, serious threat to the safe operation of the boiler, emergency shutdown, should focus on preventing the stop of the accident and the specific steps as follows: ① first blowing off; ② the coal on the grate red raking; ③ Close induced draft fan.
Anyang City Minshan Nonferrous Metal Co., Ltd. is a collection of urban mining, renewable resources, energy as one of the economic wisdom of cleaning companies, mainly non-ferrous metal extraction and processing work. Company to conserve energy, cleaner production for the purpose of this concept coincides with the fast boiler. Thus, when the company in the purchase of the product boiler, and fast boiler almost hit it off, by the party to provide a fast 6 tons of steam integrally condensing gas professional 21 t h coal fired steam boiler (WNS6-1.25.Y.Q).
Boiler for Rubber industry
Rubber Vulcanizing need high temperature steam, while steam generation is produced by steam boiler. In rubber industry, steam boiler play an important role which supply high temperature steam. Steam boiler fuel can be: Rice Husk, Coal, Lignite, Washery Rejects, Char, Indian/Imported Coal, Petcoke, Pith, Wood etc. Boiler prices for steam generation in rubber industry, please contact our online service, and we need to comfirm the capacity, pressure, temperature.
Horizontal hot water boiler a few precautions, overpressure accident 1 boiler, professional 21 t h coal fired steam boiler overpressure phenomenon of (1) a sharp rise in steam pressure, the pressure exceeds the allowable working pressure gauge pointer over the "red line" is still working pressure safety valve l high. (2) the operation of the device is the interlock overpressure protection, should send overpressure alarm signal, stops the air blowing, the wind, coal. (3) steam temperature and steam flow rate reduction increases. 2, to treat boiler overpressure (1) weakened rapidly burning, manually open the valve or bleed valve. (2) increase the water supply, while the lower reinforcing blowdown drum (It should be noted at this time to maintain the normal water level of the boiler), in order to reduce the temperature of the boiler water, thereby reducing the pressure in the boiler drum. (3) as a safety valve malfunction or all of the pressure gauge damage, emergency shutdown, safety valves and pressure gauges are to be repaired after the boost operation. When endanger the safe operation of (4) Boiler excessive pressure, blood pressure should take measures, but too fast buck is strictly prohibited. (5) boiler overpressure eliminate serious, to the shutdown of the boiler internal and external inspection, to eliminate the overpressure caused by deformation, leakage and other safety accessories and maintenance unqualified. Second, an accident boiler water, boiler water shortage (1) below the minimum safe water level line, or can not see the water level, the water level gauge glass (plate) as a white. (2) as a full-color water level gauge vapor instruction color. Low water level alarm signal (3) water level alarm occurs. (4) low water interlocking means, the water level should be below a prescribed value blower, Fan, grate reduction motor stops running. (5) a sharp rise in the superheater steam temperature, higher than the outlet steam temperature. (6) boiler exhaust gas temperature rises. (7) the water flow is less than the steam flow, causing Should the water tube due to tube cracking or economizer, an opposite phenomenon occurs. (8) When a serious water shortage, can smell the burnt smell. (9) When a serious shortage, the door can be seen from the red-hot waterwall tubes. (10) a serious water shortage, the furnace tube may rupture, then can hear the explosions, smoke and steam from the door, watching spray the fire door. 2, boiler water treatment (1) through the "waters", sentenced to severe water shortages, emergency shutdown must be prohibited blind to the boiler feed water. (2) through the "waters" sentenced to a slight lack of water, it should reduce fuel blast, the wind, and slowly feed water. Third, full water boiler 1 accident phenomenon (1) above the maximum allowable water level line, or can not see the water level, the water level gauge glass (plate) dark color boiler filled with water. (2) all of the water phase as a color level gauge indication color. High-water alarm signal (3) water level alarm occurs. (4) decreased superheated steam temperature. (5) water flow is not normally greater than the steam flow. (6) water in a large number of sub-cylinder, severe trap operation. (7) with a large amount of water steam severe, increased salinity, water hammer occurs in the sound of the steam pipe, the steam connection flange outwardly dripping take place. 2, steam boiler full of water treatment rinse water table, determined to be minor or serious full of water full of water. Method: Close water table, the water pipe connected cock, then open drain cocks As can be seen from the decreased water level, indicating a slight full of water, the water supply is stopped, the drain valve open, put to the normal water level. Such as severe filled with water due to take emergency shutdown measures.