steam boiler capacity 1 to 16 in h
March 25, 2019, which is bound to be a special day. 0900, sunny, cloudless, in my company's plant research and development center Plains Plaza, held fast Boiler "academician workstation," the opening ceremony. With the celebration of the music movement, Group President Mr. Lu Haigang make a keynote speech on the successful completion of academician workstation.
Note condensing boiler: condensing boiler and the residual heat can be recovered portion of the latent heat of condensation of water vapor in the flue gas temperature in the boiler flue gas, in order to improve efficiency, but also reduce the harmful gases in the flue gas, so it It will soon become the future development direction of boiler technology. In this new form of drive, consumers have to buy condensing boiler, then the lifetime of condensing boilers, which consumers need to pay attention to what use it?
Steam boiler pressure gauge should use precautions steam boiler capacity 1 to 16 in h pressure gauge should note the following: 1, rated steam pressure less than 2.45MPa steam boiler and pressure gauge accuracy not only in 2.5; rated steam pressure 2.45MPa child or equal to the boiler pressure too spread made not less than 1.5. Dial gauge diameter of not less than 100mm, in order to ensure the operation of the operator to see the surface of the pressure value shown. 2, should draw the red line on the dial gauge steam boiler, he pointed out that the maximum allowable working pressure. 3, the steam boiler pressure gauge should be provided at a convenient place to observe and purging, and to prevent the high temperature affected, freezing and vibration. 4, steam boiler pressure gauge should check at least every six months once the check should seal. 5, the pressure gauge connection tube steam boiler should leaks steam leakage phenomenon, otherwise it will reduce the pressure instruction value 6, the boiler steam pressure gauge scale element should be compatible with the measured working pressure, working pressure is usually 1.5; 3 times, preferably 2 times. When no steam boiler gauges, pressure gauges or pressure damage did not meet the requirements of the apparatus, boiler steam pressure gauges of the following circumstances, should stop using: 1, the surface glass breaking or blurred dial scale; 2, no seals , damage or seal verification period exceeded; 3, no pressure gauge pointer finite bit staple staple can not be restored to the limit at infinite set of bits from zero gauge pressure exceeds the pressure data bits garment allowable difference?; 4, the jump table or a pointer leak; 5, other effects gauge accurate defect.
Daily Maintenance of environmental protection and efficient gas steam boiler capacity 1 to 16 in h steam boiler gas are the main features of recent years because the state put forward higher requirements for environmental protection, many companies have purchased after rectification gas steam boiler, which allows gas steam boiler It has been more widely used, usually purchased with the strength of the manufacturers of the products, can use more secure stability, but also the stability of gas steam boiler and routine maintenance have a great relationship, here to introduce the gas steam boiler routine maintenance methods. First, the number of regular precipitation material will appear in the combustion chamber after long-term use of clean gas steam boiler the most practical, long-term accumulation of these deposits, is likely to cause instability phenomenon appears to run gas steam boiler. Thus every consumer should be a fixed time necessary for its complete cleaning, the use of high contamination factor in some environments, for periodic cleaning time shortened. Second, prevent bump gas steam boiler should not move it after installation, to prevent the move will lead to the internal components of the boiler loosening phenomenon. And during the move, the phenomenon is likely to occur and other items bump, although the product design anti-bump when will production, but severe shock and vibration inevitably will not have a serious impact on the internal boiler, boiler failure cause overhaul and had to stop production. Third, to avoid corrosion gas steam boiler must avoid being exposed to, once the boiler corrosion, which severely shortens the life and aesthetic appearance of the gas steam boiler corrosive materials, and therefore do not always pay attention to the corrosive Item close gas steam boiler, chemical cleaning agents are also used in cleaning corrosive cleaning. These are gas steam boiler easy to use method of routine maintenance, gas steam boiler does not require particularly careful care under normal circumstances, but about every six months to do some thorough cleaning is very necessary, in addition, if not compelling, do not move them, to prevent inflicting damage to the bump, with the article followed by contacting corrosive and do not let the gas steam boiler.