steam boiler for feed mill gas fired boiler for
2. Oxygen corrosion
For the biomass fuel boiler pressure parts,the water side is mainly electro chemical corrosion,the fire side (or flue gas side) is mainly chemical corrosion.The oxygen corrosion belongs to electrochemical corrosion, it is mainly caused by the dissolved oxygen in water.At room temperature,the dissolved oxygen concentration is about 9.1mg / L,according to the GB1576-2001 “industrial boiler water quality” requirement ,the rated steam pressure should not be more than 1.0MPa,the dissolved oxygen concentration should not be more than 0.1mg / L,otherwise,it is likely to lead to metal corrosion.
The difference of fuel between Oil-fired Boiler and Gas-fired BoilerOil-fired boiler refers to the fuel-fired boiler, including diesel oil, waste oil and other oil boilers. The overall arrangement of the oil-fired boiler is similar to that of the coal-fired boiler, except that the bottom of the furnace of the oil-fired boiler is mostly made into the bottom of the insulation furnace with a tilt to the back wall of 10 °~ 30 °, in order to obtain good combustion characteristics. In order to atomize fuel oil, there are two types of fuel burner nozzle: mechanical centrifugal injector and steam atomized Y type injector. The fuel of the oil-fired boiler is the fuel (such as diesel oil, kerosene, etc.). The fuel of the gas-fired boiler is gas (such as natural gas, city gas, biogas, etc.), depending on what fuel the boiler burns. The difference between a fuel-fired boiler and a gas-fired boiler is what kind of fuel burners are used to burn the gas-fired boilers, which are called gas-fired boilers, oil-fired boilers with fuel-fired burners, and oil-fired boilers called oil-fired boilers.
Matters needing attention in installation of Gas-fired BoilerGas-fired boiler also says that gas-fired heating boiler is a kind of boiler which uses gas combustion to heat water to satisfy people's heating. It belongs to the category of domestic boiler. By gas-fired heating boiler we usually refer to gas-fired atmospheric hot water boiler, gas including natural gas, liquefied gas, city gas, coke oven gas, biogas and so on. There are explosion-proof doors on the rear of the fuel-fired boiler or on the smoke pipe, and the position of the explosion-proof doors should be conducive to the discharge of the explosion. In cases where explosive gas may endanger the safety of operators, a pressure relief guide tube shall be installed on the explosion-proof door. The installation of boilers, auxiliary machines and water treatment equipment shall be in accordance with the technical requirements of the equipment manufacturing plant. . The equipment foundation must wait until the equipment arrives and checks correctly with the design drawing before construction. 3. When installing the equipment, avoid the equipment, and the installation material should be stacked on the floor. When using building column, beam lifting equipment, the bearing capacity of beam and column must be verified in advance. 4. After installation of oil, gas, hot water and steam pipes, the pressure test acceptance shall be carried out according to the Code for Construction and acceptance of Industrial Metal Piping Engineering GB 50235 / 1997.
Anyang City Minshan Nonferrous Metal Co., Ltd. is a collection of urban mining, renewable resources, energy as one of the economic wisdom of cleaning companies, mainly non-ferrous metal extraction and processing work. Company to conserve energy, cleaner production for the purpose of this concept coincides with the fast boiler. Thus, when the company in the purchase of the product boiler, and fast boiler almost hit it off, by the party to provide a fast 6 tons of steam integrally condensing gas steam boiler for feed mill fired boiler for (WNS6-1.25.Y.Q).