straw pusher for boiler coal fired steam boiler
2018, the Group's focus on employee unions difficult. Before and after the traditional festivals, union members of the Group figure active in the employee's family difficulties; a sudden and serious illness died of the scene, the group will always be union members on behalf of the company employees a timely manner; in the process of foreign aid in the public interest, Labor union also took up the banner of love passed.
Shutdown four tons of gas boiler straw pusher for boiler coal fired steam boiler shutdown and maintenance of fire into pressure shutdown, normal shutdown, emergency shutdown. A pressure fire fire shutdown shutdown pressure applied to temporarily stop the supply of steam, the boiler is shutdown pressure hot standby state. 1, before the pressure reduction appropriately to fire the boiler load, and according to the length of the seam thicker shutdown time, (up to 200mm) to accelerate the speed of the grate, the grate is stopped when rotated about 1.5 meters from the coal seam to the shutter. 2, stop blowers, blower suitably adjusted flap subsections, relying on a lean-burn natural ventilation is maintained. 3, the sewage, to allow the water level in the boiler water level. 4, Yang fire regularly, to prevent rotation of the furnace grate extinguish the fire bed. Young fire first before sewage water, then rinse water level gauge. II. Normal shutdown Normal shutdown for heating period ends, boiler pour fire into the buck repair or maintenance. 1, make a record before shutdown problems in operation, so that after the shutdown process. 2, the coal bucket coal memory runs out, the amount of toner to reduce the wind. 3. Stop the blower, draft fan stop and then the opened door grate ash. 4, after the steam supply is stopped out, the boiler to the boiler water to maintain a high level. 5, close the main steam valve, if the pressure rises to open the air exhaust valve suitable pressure relief. 6, stop the water supply to the boiler and economizer attention to monitoring changes in water temperature, open return pipe if necessary. 7, 4 to 6 hours after the furnace fire bed down exhausted, continued rotation of the cooling grate. Throughout the boiler throttle, the door should be kept closed. Allowed to naturally cool. 8, appropriate to open the pump, the boiler water and sewage. When the pressure drops to zero, open the air valve. 9, when the boiler water temperature is below 70 ℃, boiler water can be exhausted. Shutdown is complete. 10, less than 24 hours during shutdown. Avoid Shutdown cooling process, step-down too fast. Third, emergency shutdown emergency shutdown applies to the boiler accident, g combustion equipment damage, furnace or boiler structure collapsed wall is red-hot, a serious threat to the safe operation of the boiler when; h boiler pressure parts found serious distortion, leakage. when i found flue gas explosion or secondary combustion, boiler and seriously endanger the safety of operating personnel;; when endanger the safety of operation.. the safe operation of the boiler j endanger other unusual circumstances when. 2, the emergency shutdown procedures to immediately stop a blowing coal and reduce the wind; B rotates quickly grate, the pour slag pit coal or sand, wet ash coal burning fire to extinguish. , but not to the firebox water;. c boiler air valve, the relief valve opens quickly exhaust the steam pressure is reduced;. d after the fire goes out, stopping fan, opening the ash door and door, promote air circulation accelerated cooling; 3, emergency shutdown Notes a. when an accident and emergency shutdown due to lack of water, boiler feed water is strictly prohibited to, and shall not be such as to open the air valve or exhaust valve work on preventing boiler from sudden changes in temperature or pressure to expand accidents;. b when filled with water due to an accident and emergency shutdown, should immediately stop the water supply, reduce combustion, open the drain valve and drain, due to lower the water level, while opening the main steam pipe, the sub-cylinder and steam traps mother tube, water and prevent steam pipe with a large number of water hammer occurs. c. emergency shutdown operation to ensure the safety of the main event of an accident to calmly deal with, timely reporting, and make relevant records in the "log table boiler." d. Whether shutdown any case, we must maintain timely contact with steam departments.
Washing plant choose what fuel straw pusher for boiler coal fired steam boiler more cost effective? Washing plant with a steam boiler fuel is more cost effective to what has been plagued by the problem that a lot of users, and today we analyze this problem. According to cost savings for the selection of coal-fired or biomass steam boiler more cost effective, gas steam boiler is relatively easy but the cost is relatively high, in some places not to use coal and no natural gas pipeline, then select the burn methanol, more than liquefied petroleum gas and fuel oil province, Taikang County Hengyu thermal equipment Co., Ltd. is specialized in producing supervisory inspection-free steam boiler, a more comprehensive model specifications from 0.3 tons to 0.5 tons of large tonnage steam boilers, coal-fired fuel, raw materials, fuel gas and combustion of methanol, fully automatic operation out of steam quickly and does not require supervisory inspection, I have a lot of cases washing plant, the company Sina, Netease, Tencent and other major news HC have reported. What you do not understand can inquire our company.
6 tons adjusting a combustion gas straw pusher for boiler coal fired steam boiler, normal combustion boiler three basic aspects of indicators include a uniform supply of the fuel, reasonable ventilation, adjustment the combustion. 1, to maintain the high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100 ~ 1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. 2, fuel ash to reduce ash content in the combustibles to be below 10%. 3, reducing the temperature of the boiler flue gas exhaust gas temperature should be controlled below 200 ℃. 4, holding furnace negative excess air boiler is 1.2 to 1.4, by adjusting the balance of the blowers to maintain the furnace pressure is -20 ~ -30Pa. 5, the thermal efficiency of the boiler to improve the thermal efficiency of the boiler should be kept above 60%. II. Combustion Adjustment 1, the amount of fuel to air required for combustion and the amount of a reasonable distribution. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. 2, the thickness of the seam and seam thickness configuration grate speed is 80 ~ 120mm grate speed at high, middle and low profile configuration of several commonly used methods:. 9a rapid combustion of thin seam b c thick seam in low combustion. 3 thick seam combustion speed, the segment with the wind blowing principle: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. Normal combustion conditions are: fuel from the coal at the beginning of the fire shutter 300mm, uniform flames, the fire bed formation, at the end of combustion from the end of the grate 300 ~ 500mm. 4. maintain proper furnace temperature to avoid coking. The fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. 6. The residence time of the fuel on the grate in less than 30 minutes.