sugar plant 25 ton cfb steam boiler sale
Premix module up and running off all power to the boiler 1. The premix boiler modules, opening the inlet valve of the gas pipe, drain valve. 2. Check the gas concentration in the gas pipeline, the check valve on the pipe flange connections without leakage phenomenon, if any should be handled immediately. 3. After the inspection is completed, the power sent to the controller module premix boiler, close the power switch of the burner. 4. Check that the controller parameters are normal, the system comprises a gas supply, water supply system, ignition system and flame protection, water protection system control, pressure control and protection system, electronic control box and the like. 5. Open premix boiler circulating pump module, observe thermometers, pressure gauges, and the corresponding water level gauge pipe fittings for water leakage. 6. The furnace boiler ignition should choose different methods of operation, after prolonged shutdown should be small fire. 7. After ignition must closely monitor the boiler water level. Ensure the water level is maintained at normal level. 8. When the premix module system pressure close to the operating pressure of the boiler, check the connections for leakage, disassembled flange connecting bolts, need to tighten again, should operate sideways, the force should not be excessive, to prevent the bolts off. 9. The premix normal operation of the boiler module (1) should be in the water level gauge in the visible range, the operation should be adjusted with changes in load level gauge must be washed once per shift. (2) boiler blowdown, should be carried out at high level, low load, the operation should make protective measures. . (3) periodic testing demineralized water, softened water boiler system to ensure that qualified.
What structure and principles of industrial boilers in particular? What structure and principles of industrial boilers in particular? Industrial boilers has become the hottest on the market boiler boiler. Whether it is gas or gas hot water boiler sugar plant 25 ton cfb steam boiler sales, gas boilers generally use natural gas, liquefied petroleum gas and city gas as a fuel gas fuel. First, the working principle of gas steam boiler: the furnace and the combustion heat of the fuel gas steam boiler, heating pot of water evaporated into steam. Water pan (drum) in the furnace gases are fuel combustion energy released continuously heated, increasing the temperature and pressure steam is generated. When the boiling point of water increases with increased pressure, is sealed pot, the pot water vapor expansion is limited, and therefore the thermodynamic pressure (strictly speaking, water steam boiler). It is widely used as an energy source in the drum, the water is heated and vaporized again to saturation. Second, gas steam boiler basic structure: gas steam boilers and boiler drum consists of two body parts protection, instrumentation equipment, automatic control and protection system of continuous safe operation of its composition. This boiler water wall boiler drum boiler drum in the zoning arrangement, the first two return pipe fireworks smog chamber back to the drum. Connected between the drum and the tank, with water-cooling pipe and the downcomer, which constitute the framework of the combustion chamber. The pot is provided at the top with a steam water separator, to reduce the amount of water extracted from the steam. The bottom of the pan heating surface of the drum, and fireworks waterwall tubes.
December 28, 2018, fast Boiler Co., Ltd. through a one-time inspection, duly named academician workstation. The Group was rated "academician workstation" station units, marking the overall level of scientific research and innovation our company has been at the forefront of the boiler industry has been affirmed and recognized experts in the community. Establish academician workstation, it is an important measure of business demand and technological innovation academician expert resources to achieve successful docking. This served as the "fast boiler academician workstation (ID: GZZ2018042)" in the station academician of Chinese Academy of Engineering, the National Academy of pressure vessels and Xuedong, director of Pipeline Safety Engineering Technology Research Center.
The measures to deal with sparking but non-ignition of ignition rod in gas-fired boiler are as follows: clearing; cleaning first, if no replacement; adjusting test; adjusting distance (3~4mm is good); removing cleaning (cleaning parts with diesel oil), cleaning parts with diesel oil, etc. More information on oil products, oil products information oil blending technology, please follow the official account oil circle. Check pipeline and oil filter, insulation equipment; remove oil pump outer screw, carefully remove outer cover and remove oil net from inside, wash with diesel oil; replace it with new oil.