thermal heater boiler industrial coal fired boiler
biomass/coal fired steam thermal heater boiler industrial coal fired boiler for tofu machine
Our biomass/coal chain grate boiler in structural design, relative to the larger space of the traditional boiler hearth, while the layout of a secondary air, a reasonable composition of the aerodynamic field, to ensure that flue gas in the furnace residence time to avoid the tiny carbon particles are taken out of the furnace, So that a large number of volatile components precipitated instantly burning biomass fuel combustion.
BOILERS deposited combustible material, such as carbon black, oils idle, coal, etc., it is mainly due to incomplete combustion of the tail into the thermal heater boiler industrial coal fired boiler. Especially when the ignition and shutdown, most likely to cause incomplete combustion, the rear of the boiler deposited a large amount of combustible material. These deposits reduce the heat transfer surface of the tail heating the exhaust gas temperature rises. When the exhaust gas temperature rises to a certain value, there is sufficient oxygen combustion condition occurs at the secondary combustion, secondary combustion is in the shutdown some minutes or hours after the occurrence, which is the ignition point of combustible material and heat conditions. Running faster flow of the flue boiler, heat of the combustible substances produced smoke away quickly, only a slow oxidative, ignition combustion can not be achieved. After the shutdown, the gas flue, the flow is stopped, the heat generated by the oxidation of combustible material not easily lost, the temperature will rise. If the door or flue damper closed tightly, leakage into the fresh air for combustion, causing secondary combustion after shutdown.
AMD Power were to buy 10 tons of steam and one 4 tons of steam condensing steam thermal heater boiler industrial coal fired boiler fuel gas from the company for cell processing company production and construction. From the analysis of the demand to the boiler factory, by the company solely responsible for AMD Power fully demonstrated the company's confidence in me, the smooth progress of bilateral cooperation.
Several factors underlie the vertical steam thermal heater boiler industrial coal fired boiler efficiency China has been working to catch on coal to natural gas, vertical steam boiler with greatly reduced contamination of dust, smoke and other effects of a nitric oxide gas has also been healthy curb. Efficiency is an important indicator of a measure of vertical steam boiler, a good number of factors under the topic to discuss the direct impact of vertical steam boiler efficiency began. After analysis of stakeholders, heat loss from vertical steam boiler contains two pieces: the proportion of full combustion air with flue gas emissions unreasonable heat loss. Heat loss can be reduced smoke emission can be installed at the end of the vertical steam boiler stack waste heat reuse install, or more leading system with condensing boiler. Combustion air ratio sufficient unreasonable faults into: general vertical ejector-type steam boiler burner selection, resulting in a motor fuel ratio can not be adjusted. Most of the selected vertical steam boiler is mechanically strong emission combustion engine, air-fuel ratio resulting irrational factors are the following: air-fuel ratio can be divided into two reasonable chance comprising: when the air in excess, the excess will have full cold It is heated, resulting in increased operating costs vertical steam boiler, steam boiler efficiency vertical drop; when the air is not enough, will produce insufficient burning phenomenon, caused by vertical steam boiler efficiency.