water tube diesel oil fired industrial boiler price
Basic requirements for thermal control of fuel gas water tube diesel fired industrial boiler price rooms 1. Main characteristics of fuel-fired Gas-fired Boiler the main difference between oil-fired gas-fired boiler and laminar combustion coal-fired boiler is that the combustion system is different, mainly in the fuel property and combustion mode. The combustion system of the fuel-fired gas-fired boiler has the following two characteristics: 1) if the combustion process is not controlled properly, a large number of combustible mixture can be formed in the furnace, and when the mixture is deflagration, it may cause the furnace explosion. Causing serious property losses and casualties. 2) the combustion mode of fuel-fired gas-fired boiler is space combustion, the combustion speed is faster and the load response is quick. 2. Self-control of oil-fired gas-fired boiler The control requirements are in accordance with the combustion system of the fuel-fired gas-fired boiler, and the basic requirements for the automatic control system of the oil-fired gas-fired boiler are as follows: (1) the reliable system is configured to prevent the explosion of the oil-fired gas-fired boiler. When designing the automatic control system of oil-fired gas-fired boiler, the reliability of the system must be given priority consideration, and if necessary, the design mode of setting the protection system and the detection control system separately can be adopted. In order to improve the reliability of the control and protection system, it is necessary to configure the necessary backup manual control and double indication of important parameters in the selection of the microcomputer control system. (2) strict procedures should be taken to control the start-up of oil-fired gas-fired boilers. Program control is adopted to strictly detect fuel system, air supply system and flame monitoring system in the process of starting and stopping, so as to avoid failure in the process of starting and stopping furnace. (3) timely alarm protection should be based on specific conditions. Select the following alarm and interlocking protection items related to combustion system: 1) alarm and interlocking protection of drum water level. 2) Boiler pressure overpressure (hot water boiler outlet temperature overheating) alarm and interlock protection. 3) flameout interlock protection. 4) low oil pressure interlock protection (oil fired boiler). 5) High oil temperature interlock protection (oil fired boiler). 6) low oil temperature interlock protection (oil fired boiler). 7) low Gas pressure interlock protection (gas boiler). 8) High gas pressure interlocking protection (gas boiler). 9) low wind pressure interlock protection. 10) burner flange limit to open correlation lock. 11) combustible gas leakage alarm. 12) earthquake interlocking protection. (4) when the rapid system responds to the abnormal flame extinguishment in the operation of the fuel-fired gas-fired boiler, the automatic control system is required to cut off the fuel supply rapidly and prevent the fuel from entering the furnace, so the automatic control system is required to respond quickly enough. (5) when the load of the fuel-fired gas boiler changes, the response speed of the fuel regulation is higher than that of the air supply system. Hurry up. When the load increases suddenly, the increase speed of fuel is greater than that of the corresponding air quantity, which results in insufficient combustion and black smoke, and when the load decreases suddenly, the reduction speed of fuel is fast, and the oxygen content of exhaust smoke is too high. For the small boiler controlled by bit, the increase or decrease of combustion should match the increase or decrease of air volume, otherwise, the ignition may be extinguished. Therefore, combustion and air control should be considered in the design of automatic control system. (6) for the automatic control system of gas-fired boiler, the explosion-proof instrument should be used in the field instrument.
Boiler and burner What is the difference? Simply put by the water tube diesel fired industrial boiler price and boiler furnace consisting Pot is the place to absorb heat, increasing the temperature is generally endothermic water, or water absorbs heat of vaporization of components, mainly heating water wall, etc. surface composition, and the fuel is coal furnace, where the heat released by burning oil, material, and other components mainly furnace while the burner is to provide a combustion apparatus of the release of energy, the material is spray combustion, combustion air.
Hot water water tube diesel fired industrial boiler price is the essential equipment of our hotel, one of the parties to provide fast condensing pressure hot water boiler immediate operational effect. Our demand for environmentally friendly and out of the hotel itself, very high environmental performance requirements for boilers, party fast products fully meet our needs, the index after testing are in line with the relevant provisions of the State; with the outside atmospheric pressure remains stable sufficiently improved security index boiler, eliminating our worries. --customer feedback
Overview of 10 Ton Gas Fired Steam Boiler
10 ton gas fired steam boiler for sale in ZG Boiler is a “D” type double drums water tube boiler, and its furnace hearth is adopted with membrane water wall structure. The 10 ton gas fired steam boiler has a good fuel application, such as light oil, heavy oil, natural gas, liquefied gas, city coal gas and so on. And it has the following advantages: compact structure, small occupation area, good degree of flame; Good thermal insulation performance; With automatic burner, high combustion efficiency; Multiple protection function, safe and reliable operation; ISO9001-2008, IBR and ASME certifications.