where is the 4 ton natural gas boiler
Fast one side condensing steam where is the 4 ton boiler complete protection, safe and reliable, more than 10 kinds detector guard, round protection boiler safety; proprietary condenser can maximize thermal efficiency, low environmental discharge; Chinese full touch control interface, let operational status at a glance; the use of ND steel and steel and aluminum hybrid materials greatly extend the life of the boiler.
Teach you how to properly operate a steam where is the 4 ton boiler: steam boiler before use to conduct the inspection of the damaged insulation, burner check to see whether the normal operation, also check to ensure that the open position of the valve is correct, check the device controlled device instrumentation and safety equipment accessories, equipment must meet the requirements. Steam boiler furnace entry point confirmation are: Open the valve before and after the oil circulation pump, oil heating flow valve opens, the liquid level in the sump reasonable mediate high position, confirmed that the gas pressure before ignition of the gas burner to the range, the power supply is normal .
Method for safe operation of steam where is the 4 ton boilers steam boiler before use, must be checked for damage of the insulating layer, to check the burner is operating correctly, and to check the position of the opening degree of the valve to ensure it is correct. Must be checked for automatic control instruments and equipment safety equipment accessories, equipment, in order to comply with the requirements. Check item prior to ignition of the steam boiler: open valve before oil circulation pump, oil heating valve is opened, adjusted reasonably high level of the tank, the gas pressure is determined before the natural gas burner ignition must be within the range, the power good . Refers to the operation of the steam boiler is refluxed pressure activated device circulating pump, the circulating pump outlet, inlet, outlet, and the system, it is in the normal range. Circulation pump run for 30 minutes. After the stability of the system, the next step. Open the gas tube steam boiler manual valve, button start-up burner, natural gas burner into the furnace, and then the ignition, the flame remains stable, i.e. is in a safe operating condition. In the firing process steam boiler, if you accidentally quenching phenomenon occurs, the device will automatically interlock burner saver appear. It must be promptly cut off the natural gas pipeline to start the furnace purification. Replacement of the residual gas in the furnace and closed. The system load requirements, temperature requirements and thermal oil outlet, the burner can automatically adjust the size of the fire source.
Burner fuel gas selected selection principles which fuel gas where is the 4 ton boiler burners should be based on structural features and performance requirements of the boiler body, in conjunction with user conditions, making correct comparison, several general principles according to the following options: 1) according to user selection of used fuel type, liquid fuel kerosene, diesel oil, heavy oil, residual oil and waste oil, fuel gas city gas, natural gas, liquefied petroleum gas and biogas, fuel should have the necessary analysis of data used: ① kerosene, diesel should have heat and density. ② heavy oil, residual oil and the viscosity should, heat, moisture, flash point, mechanical impurities, ash, freezing point, density and the oil temperature. ③ should calorific gas, gas pressure and density. 2) to select the type burner nozzle atomization method or the gas burner and the furnace structure according to the performance of the boiler. 3) the burner output should match the rated output of the boiler, choose a good shape of the flame, such as length and diameter so as to adapt the furnace structure. The required combustion air is supplied from the root flare fuel gas and air or oil mist uniformly mixed rapidly, to ensure complete combustion. The rated output of the boiler and boiler efficiency is determined, the fuel consumption is calculated, and then selected according to power a single burner arranged to determine the number of burners. Increase the number of burners, in favor of the atomization quality assurance wind oil mix, but too many, and not easy to operation and maintenance, will give burner arrangement difficult. 4) adjusting the burner to a large extent, be able to adapt to changes in boiler load, to ensure complete stable combustion under different conditions. 5) fuel atomization less energy consumption, adjusting the wind resistance of the device to be small. 6) Effects of noise and smoke emission must comply with environmental standards, mainly emissions S02, CO and NOx must be lower than the predetermined country, should use low NOx burners and low noise. There are integral and split two 7) a burner assembly embodiment. I.e. monolithic burner body, the burner and a combustion air blower system (including an oil pump, a solenoid valve, a servo motor or the like) into one; split i.e. burner body (comprising a combustion head, oil or gas systems), fans and combustion burner control system (including the control box, fan thermal relay, AC contactor, etc.) are each independent three-part system, according to the specific requirements of the boiler and user choice. Simple 8) should be used in construction, reliable operation, easy to adjust and control the repair, easy to implement automatic control of the combustion process in the burner. 9) to deal with the burner brand, performance, price, and service life of comprehensive comparison. 10) In addition to the burner air pressure to overcome the resistance of the boiler body considered, but also to overcome the resistance and flue gas economizer system.